LBA identified that the rusted, roof exhaust pipe did not need to be replaced because it was no longer active, preventing an unnecessary expense.
Came first thing and explained everything well.
Aaron was timely, thorough, diligent and informative. Very professional'
Andrew was very diligent with a repair service. He called the manufacturer to make sure everything was working properly since dehumidifier was making a noise. I really appreciated him doing that, and now we know the unit is running perfectly.
Please don't misinterpret. Your company has worked on our home for years. Many times neither my wife or I could be there for the work done. From out of town to conference calls, we had set up an arrangement to be billed. This was never to be an inconvenience, but an accommodation for us and we have excellent credit. We use your company exclusively and recommend you to many others. Thank you for being the company you are....A. Kent Best
Josh was friendly and fast while servicing our unit.
Explained things well & fixed problem quickly
Upon arrival customer took me to the garage where the clean out is and had standing fluid. Ran sewer machine 30â€™ and blockage cleared. Ran all 100â€™ of cable came back clean. Ran water at floor drains to check flow. Draining as it should now. Bandaid
***failed exhaust removal motor main level condenser serial#1315E13287*** ***$151.75 warranty parts credit towards repair*** ***only 5 year manufacturer limited parts warranty runs out April 2020*** Upon arrival the customer informed me that one of the outdoor units was making a horrible squealing sound while operating. After further investigations I discovered that the exhaust removal system had a fault. The motor bearings are failing and the squealing noise is produced by that. I presented repair options to the customer and the customer chose the silver level HC7C main exhaust removal system renovation. Work completed: removal and replacement of outdoor fan motor with OE motor, removal and replacement of the voltage enhancement component, removal and replacement of the voltage distribution component, electrical termination service and performance and safety testing. I replaced the starting components versus the fan blade due to the fan blade being in good shape and the customer woul
Upon arrival the customer informed me that there was water leaking from the furnace. After further investigation I discovered there to be a fault within the water removal system. I presented repair options to the customer and the customer chose the band aid level repair that is covered by LBA under the warranty pertaining to new equipment installation. Furthermore, during my inspection I discovered a significant amount of what appeared to be microbial growth inside the evaporator case. I expressed my concerns to the customer and the customer wasnâ€™t interested in the options of adding UV light technology at this time. Thank you
Checked on replacing flue pipe that went through roof. That flue is no longer being used for venting any appliances. Customers house has been switched over too using 90 percent venting or electrical appliances. Customer is liable for trip charge.
The prv that goes into the add a line has a compression nut the wasnâ€™t fully tighten down and had a really slow drip. I tighten the compression nut down and watched to see if there was a drip. No drip and everything tested good.
Upon arrival talked to Mr Stoneburner . He thought we needed to change pressure reducing valve upon inspection I agreed.After showing options Mr stoneburner chose the bandaid .60 day warranty.Installed valve and checked operation no leaks and pressure back to normal.
Arrived to find unit not operating due to a fault in the voltage and Hance meant system. Showed customer options customer chose a Band-Aid option which has a 30 day warranty. Performed all work under the Band-Aid option. Also performed a and electrical termination service. Perform safety tech center unit was operating properly. Unit is operating within factory specifications at this time.
I preformed two air conditioner maintenance and safety inspections. The system that Nick serviced a few weeks ago is still holding the refrigerant he added. However the newer system has started leaking 410A. I have discussed with Connie the repair options and her 10 year limited manufacturers warranty. We have decided to monitor the refrigerant levels and decided on a repair next year.
Performed a full cooling inspection. Tested all safety switches and wiring. Cleaned and washed out outdoor unit. Changed indoor filter. Flushed condensate line. Unit is operating at factory specifications at this time.
Installed customer supplied laundry sink basin and installed new shut off valve for house
Air conditioning maintenance
No hot water
Lennox xc 14 preventative measures
Tankless water heater flush also estimate for new water heater.