Great as usual!
Knowledgeable, fast fix. Eli was GREAT!!
So glad that Michael was able to come to my home and repair my water heater issue. He also spent time reviewing what my future water heater options will be, so that when my current old electric 80 gal kicks the bucket, all I will have to do is make a phone call for a Hybrid upgrade. Great Job & EXCELLENT customer service!
All is well, except I thought that the teck was going to replace the filter in the furnace. I had a new one by the furnace. This morning I noticed he didn’t, so I replaced it myself. Maybe he thought a new one wasn’ t needed.
Angelena was very informed on my problem with my electric water heater. Showed me several options for a fix.
Upon arrival manager took me to the water heater in the back. I did a diagnostic. And called customer support. I checked Continuity on igniter. Igniter Has failed.I tried to source a new igniter to get the water heater up and going today. I called all plumbing supply houses in the area none stock igniter.After talking to a manager about state of water heater. Theyâ€™ve decided to replace water heater and are going to call the office and set an appointment for us to install owner supplied water heater.
Meeting canceled customer a no show
Performed maintenance inspection on a Ruud air conditioner. Checked all the electrical components and refrigerant for proper pressures and temperatures. Checked temperature drop and washed outdoor condenser coil. Air conditioner is operating under manufacture specifications.
Arrived on site for no cooling. Checked 7.5 and 8.5 Lennox RTU'S for no cooling. Found both units low on refrigerant. Added 6lbs of refrigerant to 7.5 ton unit and 3lbs of refrigerant to 8.5 ton unit. The units are cooling now with a 20* temperature split. Inspect both systems for obvious refrigerant leaks. Did not notice any obvious leaks. Both systems will need a electronic leaks search performed to point source of refrigerant leak.
Today I added half a pound of refrigerant today split system that supplies the office spaces in the front of the warehouse. I also removed ductwork from the air handler so I could clean the evaporator coil it was very dirty. I used a chemical cleaner after brushing it. Note that we need to make sure when replacing the air filter that we secure the door to the air filter because it is a very dusty warehouse. The unit is cooling has designed up this time with a 21Â° temperature split.
Found the split system in the back of the building for the lower level not be Cooling this was labeled AC unit number one. I did not have any power at the outdoor condenser unit so I checked the breaker and the breaker was not tripped so I reset it. When I went back to the roof and turn the condenser on it only ran for a few moments sounded very loud and smells like a burnt compressor. I was going to confirm the compressor was bad by ohming the windings but when I went to remove the wire plug from the compressor it exploded blowing all the refrigerant out of it, all the refrigerant was blackjack burnt. I sent the replacement quote information to are estimator. A split system in the front of the building has a low charge and needs to be charged accurately. Due to the time of day Elijah would like us to come back Monday and charge it in the morning. I spoke with dispatch and told them that's what we need to do so we will be back Monday.
Checked the paint booth for over pressurization after the customer replaced the VFD on the exhaust fan. Found the VFD operation normal. Found the profile damper in the unit out of ajustment. Ajusted the damper to the customers requirements for proper air flow. Also checked the East Lennox RTU for the East offices for no cool. Found the blower motor off on internal overload do to single phasing and the evaporator froze up. Found one of three wires to the motor pulled loose from the blower motor contactor causing the single phasing. Repaired the wire. Started the unit and deiced the evaporator. Placed the unit back into service after deicing. Explained the repairs to Elijah.
Cause of problem was that the A/C was low on charge. recharged A/C to proper pressures and temperatures. Also injected leak sealant to seal any micro leaks in the lines. Ac is operating under manufacture specs.
Upon arrival found thermostat not operating Properly, customer had a thermostat and we performance changed out of the thermostat thermostat performed correctly and satisfied.
Upon arrival found that the second floor air conditioner was not operating due to electronic enhancer not operating anymore. Gave customer several options for repair customer chose the Platinum option. Completely restored an rejuvenated the electronic components to manufacture specification. After performing at platinum repair I completely washed outdoor condenser coilâ€˜s with ECC. After performing clean out tested both air conditioners, both air Are running and performing to manufacture specification
Upon arrival found that air cleaner system was not operating properly at this time. Was unable to find a replacement bulbs system for the current air cleaner. After speaking with customer we decided to replace the air cleaner system with the air scrubber system. Installed air scrubber system and tested all operations after. The furnace is heating properly and the air cleaner is operating properly at this time as well. Customer finance this repair.
Upon arrival found that the ignition system had failed on the furnace at this time as well as several code violations at this time. Repaired ignition system cleaned out heat media transfer coil indoors and will return Monday to replace gas line bring electrical up to code and reseal return duct all at the furnace. The Furnace is now heating at this time. Disinfected tablet before and after signature due to email not working properly for the customer.
Performed an air conditioner inspection, after analyzing superheat and sub cooling and airflow measurements the system is slightly low on refrigerant recommended refilling with refrigerant 410 a customer wants to wait and see how it feels in the summer time. Compressor is operating to manufacture specs. Fan motor is also operating in manufacture specs.
Conducted CPMA on the 2 remaining split systems. Inspected all electrical and mechanical cooling operations. Inspected all motors and capacitors electrical tolerances. Inspected condition of the blower wheel, and belts. Cleaned all outdoor coils, and replaced all filters. Checked for correct cooling temperatures. The package unit for the paint booth filters and coils have been cleaned. A full check out sheet will need to be completed by a senior technician.
I preformed a whole home plumbing inspection for a P3