So glad that Michael was able to come to my home and repair my water heater issue. He also spent time reviewing what my future water heater options will be, so that when my current old electric 80 gal kicks the bucket, all I will have to do is make a phone call for a Hybrid upgrade. Great Job & EXCELLENT customer service!
All is well, except I thought that the teck was going to replace the filter in the furnace. I had a new one by the furnace. This morning I noticed he didn’t, so I replaced it myself. Maybe he thought a new one wasn’ t needed.
Angelena was very informed on my problem with my electric water heater. Showed me several options for a fix.
The techs were very nice and took care of what needed to be done.
Appreciated the service. Nick showed me how to unclog the humidifier if it clogged up again. They kept in touch about estimated time of arrival and came when they said they would. Thanks.
WE'VE BEEN USING LBA FOR OVER 12 YEARS AND RECOMMEND THEM TO EVERYONE! THEY ARE AWESOME!
I checked the Rtu 1 which serves the east offices for no cooling. I found the unit not receiving a call for cooling from the thermostat. I manually jumped the unit on and it started and appeared to run normally. I went down to the space and checked the thermostat in the Wyandotte Room. I found on pin on the printed circuit of the thermostat loose causing a bad connection. I got approval from Elijah to replace the thermostat. I replaced the thermostat and the unit is now cycling on properly from the thermostat. Please note that extra labor was involved in this call due to having to wait for a meeting to end to access the thermostat in the Wyandotte Room. Rtu 1- Lennox model # 5618C02273 PO # - 20534
Estimate for water heater
I performed the full cooling pma. I replaced the filters and checked amp draws, capacitors, contactors, bearings, belts, temp splits. Both units are operating properly at this time. There is no water access outside on this building, we will return with a portable sprayer to wash the condensors. 5/23/19 i turned to wash the condensor.
Estimate for a sump pump installed The sump pump may help but will not solve the water problem. The water is coming in from the walls because of clogged gutters and poor landscaping. Walk out basements with proper landscaping very rarely needs a sump pump
Arrived onsite to look at a unit that was freezing up. Upon investigation of this unit I found that it was a split system that serves the offices in the warehouse. I then began to check the air handler over the offices to ensure we had proper airflow I found the blower motor running and the capacitor within range. I then checked the filter and found that it was clogged full of dust and was allowing very little airflow through. Upon finding this I find one non used 20x20x1 non pleated filter that had not been used bye the unit to replace the dirty one with. Upon replaceing this I got back on the roof and turned the disconnect back on to the unit and checked the pressures on it. I found that the pressures were in a good range and that the unit appeared to be good on charge. I then checked the temperature split and found it within range at 21Â°. The unit is now operating properly I have also suggested to elijiah that the filter be changed atleast on a bi monthly basis on this unit do to t
Refunded customer per request
Took out old sump pump and put in a Zoeller sump pump. Everything tested good
Did a water heater flush. Everything tested good.
Replaced thermal expansion tank and supported.
Electric water heater hot limit switch ended up opening had to reset the switch, change the temperature setting for the water heater
I performed a furnace tune up on a trane system
Install customer supplied kitchen faucet.
Clear main drain in house and from yard clean out removing Roots from drain.
Goodman equipment tune up for a home in Country View.