Knowledgeable, fast fix. Eli was GREAT!!
So glad that Michael was able to come to my home and repair my water heater issue. He also spent time reviewing what my future water heater options will be, so that when my current old electric 80 gal kicks the bucket, all I will have to do is make a phone call for a Hybrid upgrade. Great Job & EXCELLENT customer service!
All is well, except I thought that the teck was going to replace the filter in the furnace. I had a new one by the furnace. This morning I noticed he didn’t, so I replaced it myself. Maybe he thought a new one wasn’ t needed.
Angelena was very informed on my problem with my electric water heater. Showed me several options for a fix.
The techs were very nice and took care of what needed to be done.
Appreciated the service. Nick showed me how to unclog the humidifier if it clogged up again. They kept in touch about estimated time of arrival and came when they said they would. Thanks.
I replaced the blower motor, blower wheel, and blower motor capacitor. Tested the unit and it is now operating properly at this time.
Competed inspection on Dikian package unit, replaced customer supplied air filters, check and greased motor bearings. Tested electrical components, check wiring connection and verify heating operations.
Conducted CPMA on all heating equipment. Inspected all electrical and mechanical heating operations. Inspected all motors and capacitors electrical tolerance. Inspected condition of the blower wheel, belts, and heat exchanger. Checked for correct heat temperatures within tolerance. All filters have been changed. All deficiencies have been noted for repairs.
All quotes given include parts, tax and labor, parts no longer available for Roberts Gordon unit heater
One of the filter doors fell off there was a screw holding it but it broke. Covered under warranty because we were out here a 30 days ago. Drilled new screws into new metal.
Upon arrival customer took me to the basement where they want us to run branch brain from floor brain to sump pit. I ran drain with machine and checked operation.30 day warranty. Bandaid repair
Checked both systems in cooling mode and changed filters.
Checked the East side conference room and three offices for comfort issues. Checked the Rtu in cooling and found no problems with the unit cooling normal. Checked the ductwork for manual balance dampers. Ajusted the four supplies at the take offs to the customers load in the complaint rooms. Advised the customer that they made need to make more ajustments if needed.
I preformed a scheduled maintenance inspection on the air conditioning system, everything is operating within factory specifications.
Replaced voltage enhancement system
I arrived to find that bothsystems were low on refrigerant. I performed an electronic refrigerant leak search and found both coils have non-repairable refrigerant leaks. I added refrigerant to both systems per customers request. Given the age and condition of the systems, the customer would like the office to call Monday morning to schedule a design specialist to come out and quote new equipment pricing.
I checked the Rtu 1 which serves the east offices for no cooling. I found the unit not receiving a call for cooling from the thermostat. I manually jumped the unit on and it started and appeared to run normally. I went down to the space and checked the thermostat in the Wyandotte Room. I found on pin on the printed circuit of the thermostat loose causing a bad connection. I got approval from Elijah to replace the thermostat. I replaced the thermostat and the unit is now cycling on properly from the thermostat. Please note that extra labor was involved in this call due to having to wait for a meeting to end to access the thermostat in the Wyandotte Room. Rtu 1- Lennox model # 5618C02273 PO # - 20534
Estimate for water heater
I performed the full cooling pma. I replaced the filters and checked amp draws, capacitors, contactors, bearings, belts, temp splits. Both units are operating properly at this time. There is no water access outside on this building, we will return with a portable sprayer to wash the condensors. 5/23/19 i turned to wash the condensor.
Estimate for a sump pump installed The sump pump may help but will not solve the water problem. The water is coming in from the walls because of clogged gutters and poor landscaping. Walk out basements with proper landscaping very rarely needs a sump pump