Knowledgeable, fast fix. Eli was GREAT!!
So glad that Michael was able to come to my home and repair my water heater issue. He also spent time reviewing what my future water heater options will be, so that when my current old electric 80 gal kicks the bucket, all I will have to do is make a phone call for a Hybrid upgrade. Great Job & EXCELLENT customer service!
All is well, except I thought that the teck was going to replace the filter in the furnace. I had a new one by the furnace. This morning I noticed he didn’t, so I replaced it myself. Maybe he thought a new one wasn’ t needed.
Angelena was very informed on my problem with my electric water heater. Showed me several options for a fix.
The techs were very nice and took care of what needed to be done.
Performed equipment site survey.
rebuilt hall bath three handle Gerber tub/shower faucet, tested for operation. Replaced hot and cold, diverter stems also with new chrome handles. Installed customer supplied shower head, customer is to place that where she would like. Customer would like paper copy of invoice since she has no e-mail.
Homeowner will call when she gets the shower head
I arrive to find the thermostat set to 70Â° with a room temperature of 64Â°. When I got to the rooftop unit there were no error codes or call for heat from the thermostat. Iâ€™ll check the thermostat and found one of three common wires not connected. After I connected all three, wires and put it back into the thermostat system came on and cycled off with no problems. I arrive to find the thermostat set to 70Â° with a room temperature of 64Â°. When I got to the rooftop unit there were no error codes or call for heat from the thermostat. Iâ€™ll check the thermostat and found one of three common wires not connected. After I connected all three, wires and put it put it back into the thermostat system came on and cycled off with no problems. However when changing modes on the thermostat I did notice a little bit of glitching, they said that theyâ€™ve had issues for a while. If issues continue we will need to change the Samod II ZONEX thermostat.
RTU#2 the blower belt ax57 was replaced today.
Perform preventive maintenance agreement. Replace air filters, check all electrical and mechanical components. Created an estimate for the one recommended repair. For further information please see check out sheets or estimate.
Found the inducer fan motor on RTU#1 serial #5612G08655 to have a short in the windings. Inducer Part# 69M33 was replaced and the unit is now heating as designed.
Arrived to find humidifier working properly at this time. Adjusted water flow and humidity setting on thermostat. Humidifier is operating properly at this time and creating humidity at this time.
Upon arrival the customer informed me that the humidifier wasnâ€™t working and they believed it hasnâ€™t worked since being installed. After further investigations I discovered that on the ifc board, there is a required jumper from R to hum stat for humidification purposes and that jumper was not present. I installed the required jumper from R to hum stat and the humidifier operated as it should. This is a no charge trip due to the equipment was purchased and installed through LBA in March 2019 and is covered under our workmanship warranty. Thank you
Completed annual furnace tuneup, tested all safety operations, cleaned all necessary sensors, replaced air filter. Everything tested as it should at this time. Gave customer a quote to change smoke detector quoted $120 to use customer provided smoke detector, and $150 if theyâ€™ll be a provided
System wasnâ€™t responding well to pressure switch. Customer choice band aid repair. Changed the pressure switch to the furnace. Furnace had no pr furnace had no Problem starting up, system is running Accordingly.
Performed quoted work, replaced the inducer motor and capacitor. Tested the unit in heating mode, and it is operating properly at this time.
I replaced the inducer motor, and capacitor. I did not the replace the belt at this time, because the part store sold out. I will return to install a new belt. Tested both units are they are operating properly at this time. 10/25/19 returned to replace a48 belt.
I replaced the blower motor, blower wheel, and blower motor capacitor. Tested the unit and it is now operating properly at this time.
Competed inspection on Dikian package unit, replaced customer supplied air filters, check and greased motor bearings. Tested electrical components, check wiring connection and verify heating operations.