Noah was quick to review our issues, efficient in explaining what could be done vs. what needed to be done, and helpful in fixing our issues in a concise and proper way.
Great service very fast response
I called LBA because we have an older unit and I knew I could trust them. The fix was simple and performed quickly. Glad I didn't have to replace the entire unit yet, but when it comes time to replace, will definitely call LBA back out.
The service people were very nice, proficient and courteous.
Service was performed in a timely fashion and I was made aware of what steps of the process was being done. Any questions I had about HVAC not even related to the current service was answered.
Perform a heating maintenance check all operations check temperature split check drain lines checked filter checked all electrical components check blower motor checked inducer motor clear inducer port checked heat exchanger checked blower wheel check igniter cleaned flame sensor found that the humidifier was not operating found that the connections to the humidifier were not connected after connecting the wires The humidifier came on but the humidifier pad was dirty causing it to overflow I informed the customer customer wanted me to do a humidifier tuneup replace humidifier pad and port Port make sure humidifier is not overflowing check CO levels check for gas leaks everything is running fine at this moment system was running when I left thank you for having me out today Alex View visual findings from this job here - https://visionshare.xoi.io/?id=XA-178F-1E96EEF55512439985062ED7ECC60962
Checked all operations in the cooling mode and inspected furnace filter. Found furnace filter was dirty and replaced with customer supplied. Checked all electrical and refrigerant components at the outdoor unit. Found out the remote to be extensively dirty. Upon customer approval I perform an extensive cleaning today. System is operating properly at this time. View visual findings from this job here - https://visionshare.xoi.io/?id=XA-6F30-8BE56DA927B9405F80BDFE5EA614E843
I re leveled the outdoor unit by uninstalling and reinstalling air conditioning system outdoors. Checked all operations after completing repairs pulled below 500 µm and checked refrigerant charge and was within factory specifications. Air conditioners operating within factory specifications at this time. View visual findings from this job here - https://visionshare.xoi.io/?id=XA-D392-3D9F1D0466AF4FAFA2C0B8737F1609A6
Scope of work. Company will install two new frost free hose hydrants. Company will remove old hydrants from home. Company will honor two year warranty on all parts and labor. Arrived at customers home August 8, 2022. Customer concerned about hose hydrants on outside of home. Gave customer estimate to replace both hose hydrants with frost free a inch hose hydrants. Customer accepted estimate. Shot water to home and installed new hose hydrants. Customer also signed up for Service membership. Company will honor two year warranty on both new frost free hose hydrant installations. Thank you for choosing LBA have a wonderful day
Performed cooling maintenance checked all operations check filter checked temperature split checked drain lines checked all electrical components check refrigerant wash outdoor unit system is running fine at this moment customer was interested in system releveling I quoted customer 1200 customer wants to take the unit out relevel the pad customer will let us know when he’s ready to do the repairs thank you for having me out today Alex
Performed furnace maintenance. Filter does not need replaced. Completed all checks and cleanings. Complete a combustion analysis check for proper/safe operation of a furnace. System is heating and operational at this time.
Upon arrival customer informed me the furnace was not coming on to heat the house. Upon inspection I came across that the gas valve was bad. Furnace is 44 years old, recommended replacing the unit because of the age and also safety of the old unit. Having a comfort specialist out to give options on replacement. Thanks for having me out it was great to meet you!
Performed full heating preventative maintenance on one rooftop unit. Checked all electrical and mechanical components, changed all filters. The unit is operational at this time.
I found a few issues with the Lennox package unit (model ZGB060S4BS1Y, serial 5617F03808). The economizer control module is broken causing the fresh air damper to stay open. I disconnected the economizer with the damper shut. The system is a little low on refrigerant, I was unable to find the leak with a quick leak search using an electric detector. The other issue was the fan was set to run, this will cause the humidity to rise. I set the fan to auto so it will only run with a call for cool or heat. Rich and I will discuss a strategy and billing.
9-8-21 Return visit Yesterday found evaporator frozen, needed to sit overnight to thaw out. This morning found unit running evaporator was thawed out. I installed new blower belt check tension. Start the AC system, check my evaporator split. Evaporator split was at 10Â°=64Â°- 54Â° Checked The Refrigerant Charge, System was low on Refrigerant. Added 2 pounds of 410 a refrigerant per the manufacturers charging chart. Rechecked the evaporator split currently I am at 20Â°= 64Â°- 44Â°. Did a quick refrigerant leak search not find any leaks today. Unit is working at this time.
9-7-21 2.25 hrs AC not working Found evaporator iced over lower belt loose. Thermostat set at 50Â° Starting to thaw out the evaporator coil is too much ice on it Iâ€™m gonna let it sit overnight and return the morning.
22 year old carrier system operating, furnace motor rattling in bad shape. AC leaking r22. Recommended upgrading to new higher eff ac and furnace system. Presented 3 Ruud options, said he will decide later today.
Customer had company out due to leaking 40 gallon natural gas Bradford white water heater. Leak was coming from rusted out nipple on top of heater. Customer just requested estimates on 40 and 50 gallon water heater with minimum code upgrades. Company is writing up two different estimates for replacement. 40 gallon water heater natural gas, 2 gallon thermal expansion tank, new isolation shut off, and new gas flex. Company will install PRV if needed. Installation crew is coming same day for installation and will notate installation itself thank you for choosing LBA and have a wonderful day.
Met with Father Dave. His daughter and son in law live there. 15 year old ac and furnace, ac dismantled and non op. Presented 3 Ruud options to install ac and gas furnace system. Recommend duct cleaning and IAQ. Reviewing with decision makers, follow up Monday.
Order parts, pick up parts, pull parts into roof, remove old blower motor, install new blower motor and pulley, reattach belt, verify operation, remove old parts from roof and haul away. Lennox Model LGH036SUTS4Y Serial 5619F08453 The blower motor is not covered under warranty, I have already checked and the blower motor will take about 5-7 days from date of being ordered. 5-28-21 picked up motor from shop, arrived at site, got motor on roof, removed old motor, wired new motor to match old motor, installed new motor, verified operation. Unit is working correctly in all stages. Dehumidification set at 48 percent and running properly. Heating had a temp rise of 35 degrees rated at 15-45. Cooling had a delta T of 19 degrees out of 20. Blower is pulling 2.4 amps out of 2.6. Unit is back and running correctly at this time.