I called LBA because we have an older unit and I knew I could trust them. The fix was simple and performed quickly. Glad I didn't have to replace the entire unit yet, but when it comes time to replace, will definitely call LBA back out.
The service people were very nice, proficient and courteous.
Service was performed in a timely fashion and I was made aware of what steps of the process was being done. Any questions I had about HVAC not even related to the current service was answered.
Arrived to find that the condensate trap was plugged in causing water to overflow from the condensate pan. The condensate trap was plugged. This was caused by excess oil on the evaporator coil from the manufacture when they make the coil. I flushed the drain line and the drain is now flowing properly. I also checked refrigerant level and it is within factory specifications. The system is operating properly at this time.
Found water for irrigation Will be tested tomorrow Tested backflow device all passed
We were called about a backflow test. I opened pit to access backflow and preform test. No water to backflow has been disconnected. They do not have a functioning irrigation system
Checked all operation in the cooling mode. Checked all electrical components on the outdoor unit. Spoke with customer about extensive coil cleaning which customer wanted to do so at this time. Replaced furnace filter. System is operating within factory specifications at this time.
I have replaced the blower belt and tensioned it properlu on rtu-1 at this time. Also while performing this I checked what was believed to be a low temperature split and that the unit was low on charge out per Zach's request on this quote. Upon investigation I found that the location of my temperature probe was not picking up accurate information and I also found that the economizer was open slightly to far causing a high return. I have adjusted this at this time and found the unit running properly with a 20Â° cooling split.
Performed preventative maintenance per agreement. Washed coils, changed filters, and checked operation and components on 1 Lennox 5 ton rtu. I found that the blower belt for rtu-1 was in poor shape at this time.
Customer is waiting till October to buy and thatâ€™s if his credit score jumps he says . He is in no hurry because there is nothing he can do anyway. He was already denied by Anthony. Heâ€™s having multiple companies come out anyway just to see prices. I told him pricing changes from now to then.
Installed new 40 gallon water heater
Tried to relight pilot light on water heater, unsuccessful have to do repairs or replacement
Floor drain clogged because of AC condensation. Auger branch line for a home in Genesis Creek Estates.
I added freon to a Trane system.
Kitchen drain line clogged. Auger drain line.
I replace a condenser fan motor on a Lennox system.