Technician very pleasant and knowledgeable
Very professional and courteous
She did a great job, explained what she was doing and why. Very pleasant and helpful. Great attitude!
Nick was very professional and courteous.
1-20-21 wed Picked up filters Performed heating check on 1 office split system furnace and 2 garage unit heaters. See attached check out sheets, all 3 systems working working properly at this time
Upon arrival I preformed quoted work to replace the hallway bathroom toilet with a comfort high elongated toilet. I also signed the customer up on the P3 agreement. I tested for leaks and everything tested good.
Customer complaint of a burning smell in there data room, upon my arrival customer had unit turn off, I turn unit back on to try locate the smell, we inspected unit wiring didnâ€™t see any problems ,checked operation of supply it too is working ok , talk with the customer about not able to finish any problems at this time, all work was done on unit model# PKA-A36KA7 serial# 8YM0384
Estimate for toilet replacement
RTU Model#ZF048N10A2AAA4A Serial#N1D6479791 Currently complaint of no heat, troubleshoot and found unit off on high limit switch, reset switch than checked operation of fan motor name plate is 2.3 amps actual amps is 1.9 , the motor is running with in range ,checked temperature rise and that also is ok , I did change out two dirty filters that customer provided, everything seem to be working ok at this time , I explained everything to customer , if problem returns ie us a call
Performed maintenance and safety inspection on two air handlers. Both air handlers are wired for cooling only and have no heating elements. The filters have been changed, Betsy been checked and the blower motors are operating properly. I also gather plumbing and HVAC information for a maintenance contract. There are three bathrooms. The downstairs menâ€™s restroom has one toilet one urinal and one sink. The downstairs womenâ€™s bathroom has two sinks two toilets and two showers. The upstairs bathroom has two sinks one urinal one toilet and two showers. There are two hot water heaters one for the sinks and one for the showers. A quote will be sent for maintenance. Both water heaters or electric water heaters the smaller one is only a 6 gallon unit. The larger one is a 40 gallon. The plumbing maintenance site survey was not attached my job and I have no way to open it to fill it out.
Furnace Maintenance Tuneup- Inspected thermostat, Inspected air filter, checked for Co-(0ppm) Checked for Gas leaks-(None). Inspected and tested all motors, all motors are operating within the factory specifications. Tested the voltage enhancement system, tested all safety sensors, all sensors are operating correctly at this time. Inspected heat exchanger- heat exchanger shows some rust, no cracks or holes are visible, heat exchanger appears to be safe at this time. Cleaned inside and outside of the furnace cabinet. Performed combustion analysis, readings came back normal. All heating ops are normal at this time.
I arrived on site to work on Rtu # 1 model# 48TJE004-511 serial# 0899G20467 I replaced the gas valve on the unit and verified operations. Unit # 6 model # 48TJE004-511 serial# 0899G20471 I replaced the ignition board on the unit and verified operations.
Today I completed your annual heating tune up, I checked all safety and electrical devices to ensure your system is running safely and efficiently, I cleaned system and performed combustion analysis, checked for proper heating transfer, everything tested as it should at this time, thanks for choosing Lba, Eli
Upon arrival I preformed a whole home plumbing inspection for the customer. The water heater is 4 years and in working condition. The customers water pressure is at 60 psi. Code requires it to be between 60 and 80 psi.
Performed full heating maintenance on 6 RTUs and 4 unit heaters. Checked mechanical and electrical components. Checked temp rise. Estimates have been sent for repairs.
Performed full heating preventative maintenance on six RTUâ€™s and 4 unit heaters, checked all electrical and mechanical components
Upon arrival I tested backflow preventerâ€˜s. I tested three backflow preventerâ€˜s in all. Number one Ames 3/4 double check valve serial number 05774 check valve one closing held at 1.75 check valve number two closed and held at 1.5 this backflow passes Number 2 Watts reduce pressure assembly serial number 298028 size three-quarter check valve number one held at 8.5 check valve number two held at two relief valve opened at three this backflow passes Number three Ames double check detector assembly size 6 inch serial number GC0877 check valve number one held at 1.75 check valve number two held at two psi this backflow passes.
Performed maintenance inspection on a Lennox furnace. Checked all the electrical components and safeties for proper operation. Checked Combustion on the exhaust. Filter is still clean at this time. Customer service their own humidifier. Furnace is currently operating under manufacture specifications.
Water heater inspection special with flush Company flushed and inspected all amenities on state select water heater 75 gallon 1. Shut off for cold side of water heater is gate valve which is operational. 2. Company also vacuumed out dust around burner assembly. 3. Ran water to ignite burner for testing. 4. Tested pressure for pressure regulating valve which is operating at 60 psi 5.Tested thermal expansion tank which is operational but is undersized. 6.Inspected gas line With leak detection Final report and conclusion is that Everything on water heater is testing ok at this time. Recommended repairs 1. Expansion tank replacement for code requirements. Customer does not want any estimates at this.