Very professional and courteous
She did a great job, explained what she was doing and why. Very pleasant and helpful. Great attitude!
Nick was very professional and courteous.
The service tech Mike was great. He did a great job a few weeks ago when he came and priced the system and a very clean and efficient job for the install.
The unit on the ground was not cooling. I found the condenser was dirty, the belt was very worn out and had serveral tears, and the filters were extremely dirty. After washing the coil and putting on the spare belt. The uni is operating properly at this time. I replaced 2 filters and the customer replaced the 2 other filters
Upon arrival found unit number 5 not running as disconnect was not making proper connection manually pushed in operating well now also gave customer price to replace disconnect.
Performed maintenance on split system see quote for repairs.
Customer has water heater that is five months past the warranty. I am replacing the main burner control system, due to the failure. Also replaced the gas valve. After installation I relit the water heater and make sure the system was heating working. I also replaced the flapper in the hallway bathroom beside the laundry room.
Installed new shut off valve for refrigerator
Installed new toilet valve and flapper also new shut off valve for toilet
Installed new flapper
Angered first floor entryway toilet to clear stoppage and clean bowl
Conducted a full furnace tune up on 2005 American Standard furnace. Found the flue piping to be very brittle from rust and lots of pitting and rusting on heat exchanger. Customer wants to look into replacement options.
Lennox air conditioner not cooling. Found the a/c low on R-22 freon and a failing TXV.
Spring maintenance air conditioning tune up on a Lennox 13ACX air conditioner.