Andrew did great, knows his stuff and took care of us.
They did a nice job, turns out we have a fried system.
Available, courteous, ease of scheduling work
Jose was a very knowledgeable and professional HVAC technician. A pleasant person as well and a credit to LBA.
Had a service call on an install from last year, no issues with install, still running great. Tech was professional and good to work with.
Very courteous, professional and helpful! LBA also fit me in when I needed the service asap!
Rigo did an excellent job and was a very likeable as well as professional.
Arrived quickly, explained the issues so we could understand them.
The saleman, Scott, was very professional and quick to respond to any problems/questions. Jim and Mason who installed my Ruud split heat pump system did an exceptional job. The troubleshooter Eric was extremely impressive. LBA is definitely top-shelf in this field.
Andrew did a great job installing my humidifier!
Mike arrived sooner than I expected, got right to workv and quickly homed in on the problem -- gnawed wiring. Repair was fast, and he advised me on future maintenance.
Always looking forward for rusty's arrival
Mike Carter is an amazing plumber who knows what he is doing and talking about.
Arrived on time, install went well. They got stuck in my yard - didn't bother to tell me. Overall good.
After arrival customer stated that they knew the acoil was leaking had another company out verified it I did my own verification lower right corner of the a coil it is a D with coil on SC with furnace causing higher pressure on the lower right side it is under a 10 year PNL talk to CFM and Brian give them alternative to get it fixed they are going to call CFM and let us now View visual findings from this job here - https://visionshare.xoi.io/?id=XA-12EE-EFDEF9A038E64CDB9EC96EA4AC4A391B
Arrived to remedy an inoperable air conditioning system. Upon inspection of the system found the system operating, but only cooling 10 degrees. Checked refrigerant levels and found that the system is low on refrigerant. Checked the evaporator coil for cleanliness. Checked heat exchanger and found it cracked. Talked with homeowner about repair and replacement solutions. Sat with homeowner and comfort consultant and provided estimates for new equipment. Turned off the gas to the furnace and tagged the the furnace as not safe to operate. Air conditioning system can still be run but will freeze up.
Performed cooling maintenance for both units checked all operations checked all electrical components washed both outdoor units replace filters checked charge found at the main system was low on refrigerant perform a leak search did not find any leaks at this moment inform the customer about the system being low on refrigerant added refrigerant and leak sealant system is now back to manufactures target both units were running when I left thank you for having me out today Alex
Air conditioning maintenance for a residential customer who needs their humidifier to be relocated. Humidifier was relocated to the side of the return air to better distribute the air.
Maintenance on water softener and reverse osmosis water filter. Water heater flush and tune-up.
AC Repair for a residential customer with no airflow coming from vents. Technician sent to diagnose and repair. Ducts found dirty. Duct cleaning was performed. Filters replaced. The system is now operating as it should for the homeowner.
Customer had company out to inspect laundry line that goes into floor tying into floor drain in garage going out Company determined there is a garden hose stuck in laundry line itself and Company found drain draining off to creek in daylight which is deemed illegal. Company is going to write up an estimate to install sewage ejector pump behind washer unit that has drainage going up penetrating through wall going into other room tying into 3 inch stack ABS. If company has to vent pit can be vented by mechanical vent or vent can be penetrated through wall for fresh air intake as well. Company will supply plug extension until customer can run dedicated 120 outlet over to pit. Customer is going to talk it over and get back with company in near future.
Company arrived on December 16, 2021. Customer has clogged washer line. Upon inspection company found that there are two vertical stacks behind washer to put dispenser hose in. One of stacks has garden hose stuck in it. Company attempted to pull hose out, but hose will not remove from line. After running some water company found that washer line and two floor drains run outside of house and into a ditch rather than connecting to Main that leads to septic. Tech is going to have dispatch schedule another appointment for another plumber to come out and create an estimate to have problem fixed. Thank you for choosing LBA and have a wonderful day.
Performed furnace maintenance. Filter does not need replaced. Completed all checks and cleanings. Complete a combustion analysis check for proper/safe operation of a furnace. Customer does not currently have a humidifier installed and is not interested in adding humidification. System is heating and operational at this time.
Spoke with all 3 managers of all 3 suites. No one reported a constant leak. The thrift store fill valve tube had come out of it place and got water on the floor recently, but it had been put back by the time of my arrival. Replaced the flapper in this toilet as it was constantly running. All 3 have roof leaks during rain.
Free estimate given for whole house.
Removed portion of galvanized, approximately 6â€™, above entrance water line. Installed new cut off valve and pressure regulating valve set to 70psi. Installed 50 gallon natural gas water heater with thermal expansion tank and flue piping. Tested for proper flow and function.
Estimate is for company to cut access to remove section of existing galvanized to install pressure reduction valve on main tying back into original galvanized. Company will install new 50 gallon heater with code upgrades including 2 gallon expansion tank new ball valve and water lines connecting to galvanize lines new 3/4 gas cock, 3/4 by 3/4 by 1/2 t with dirt leg and gas whip. Went over options with customer and customer wants to go ahead with the option and have company come out following day on September 10 to conduct installation. Thank you for choosing lba and have a wonderful day.
Upon arrival found that the system had taken a surge and the surge and has caused multiple components being the capacitor and others being the control system and thermostat to fail. Customer chose to have capacitor system replaced and rewired as well as control system replaced. Installed surge protection systems to prevent this from happening in the future. Installed customers old thermostat free of charge at this time. There is possible other damage on the low voltage side but no signs were showed at this time. recommended a early furnace tune up to inspect the furnace fully allowing it to run for a long period of time. Customer financed
Assisted Tyler with install of new Lenox rooftop unit. We remove the hill guards, heat strips and the barometric damper from the old system and put it on the new unit. Compressor condenser motor and blower motor all motors are operating properly at this time. The unit has a toy degree temperature split and cooling and 29Â° temperature split in heating. When we first started the unit up the condenser fan was hitting their guard so we lowered the fan blade by approximately 1 inch. The unit is operating properly and safely within factory specifications and guidelines at this time.