Excellent service and very respectful
Was very quick in repairing humidifier line to furnance!
Great service! Nick and Al were extremely courteous, professional and honest. We recommend them without reservations! Thank you.
David was professional and friendly.
I am amazed how something so big for me is trivial to a plumber. LBA was able to send someone out the next morning. Phil was cheerful and knew his business. He recommended a solution and quickly replaced the defective shutoff and adjusted the overflow. Sweet.
Explained everything. Even did a small favor for me before he left
I had my pipes ran through with a video to see any issues. It was quick and easy and my tech explained as he went.
Austin was very polite and professional and cleared my clog in no time!!
Installed 50 gallon ruud natural draft Water Heater with 2 gallon expansion tank with a water heater safety pan. Also re-piped water heater with new 4â€ metal flue pipe
88 dollar main line opening special. Customer had mainline back up not allowing them to use any water in household itself. After further diagnostic confirmed customer had accessible clean out located to the right of back door of House. Sent cable machine through accessible clean out and got stuck approximately 25 feet in where cable machine finally push through and water started to drain from line. Had customers start running water through all plumbing amenities to test line itself in line was still backed up so company and continue to run through trouble area and hit multiple blockages between 25-40 ft. Line started to drain and flow properly while bringing cable machine back company brought back multiple clumps of roots and believe that thereâ€™s a problem area at the 25 to 35 foot mark in line itself. Going to schedule for camera specialist to come out and inspect line. No warranty on line itself thank you for choosing LBA and have a wonderful day.
Today I completed your annual heating tune up. I performed combustion analysis and tested all safeties. I checked your air filter and cleaned flame safety system. Everything tested as it should at this
Performed electric furnace tune up. Replaced customer supplied filter. Tested system operation. Checked amps on electric strips, checked blower motor capacitor. System is heating and operational at this time.
Annual P3 heating visit. 2 year old Ruud furnace. Cleaned furnace, checked temperature difference across furnace, performed combustion analysis, tested and inspected humidifier, performed safety inspection, tested for gas leaks, tested furnace components for reliability. No concerns with furnace safety or reliability at this time, furnace is running within manufacturers specifications.
Thank you for allowing me to service your HVAC equipment today. Performed maintenance and safety inspection on the furnace and humidifier. Replaced the humidifier water panel and left an air filter for future use. Inspected all electrical connections to ensure they are secure and not rubbing. Performed a combustion analysis on the heat exchanger and found zero issues. System is running safely and within manufacturers specifications at this time.
P3 Furnace Maintenance Tuneup- Inspected thermostat, Inspected/Replaced air filter, checked for Co-(0ppm) Checked for Gas leaks-(None). Inspected and tested all motors, all motors are operating within the factory specifications. Tested all safety sensors, all sensors are operating correctly at this time. Inspected heat exchanger- heat exchanger shows some rust, no cracks or holes are visible, heat exchanger appears to be safe at this time. Cleaned inside and outside of the furnace cabinet. Performed combustion analysis, readings came back normal. Performed humidifier maintenance, replaced water pad, cleaned drain line and inside of humidifier, humidifier is set for the winter. All heating ops are normal at this time.
Today I completed your annual heating tune up. I performed combustion analysis and thoroughly tested system. I spoke with customer on his concerns for the system and he stated he had interest in having a humidifier installed as well as have ducts cleaned. I gave him estimates on both. I also found that the voltage enhancement system was testing near failure and gave customer estimates to have that fixed. Everything else tested as it should at this time
Performed furnace maintenance. Filter does not need replaced. Completed all checks and cleanings. Complete a combustion analysis check for proper/safe operation of a furnace. Humidifier is operational. System is heating and operational at this time.
Performed heating tuneup on furnace. Replaced air filter was over a year old. Replaced water panel for humidifier. Inspected all electrical components and electrical wires. Checked temperature rise. Furnace is running within manufacturers specs at this time. While I was checking for any gas leaks found water heater valve is leaking, I purposed a new water heater and recommended to not run water heater at this time because of hazardous condition. Will return tomorrow to replace water heater between 12-4
Motor coupling had broken on boiler pump. Coupling had been replaced two years ago. Inspected and replaced coupling and motor mounts. Re assembled and tested. Boiler is operating as it should be at this point
Upon arrival the customer main line was backing up into all 3 bathrooms again. We were out last Wednesday and had to pull one of the toilets and cable the line out. When I arrived here today the main line was not clogged anymore and flowing properly. I recommend that we needed to get a camera specialist out to look at the main line and quote them new power flush toilets and outside cleanout. Customer declined at this time and said they will go with camera specialist the next time the main backs up again. This was not a go back.
1-25-21 mon Performed heading check on 1 split system furnace See attached check out sheet Also updated the filter list
P3 Furnace Maintenance Tuneup- Inspected thermostat, Inspected/Replaced air filter, checked for Co-(0ppm) Checked for Gas leaks-(None). Inspected and tested all motors, all motors are operating within the factory specifications. Tested the voltage enhancement system, tested all safety sensors, all sensors are operating correctly at this time. Inspected heat exchanger- heat exchanger shows some rust, no cracks or holes are visible, heat exchanger appears to be safe at this time. Cleaned inside and outside of the furnace cabinet. Performed combustion analysis, readings came back normal. All heating ops are normal at this time. Upon inspection of the system, found the the unit currently does not have a humidifier installed, presented options to customer. Customer would like to have a humidifier installed and will pay when the the install is finished. Will set a time to return for install.