Outstanding work by Rigo - complicated issue, excellent diagnosis and execution.
Again LBA came thru with flying colors gelping us out with great service. Explanation of issue, giving options to choose from and again explaining what solutions were being put into place and what to do shoukd it happen again.
Rich came out on a holiday weekend to fix an emergency sewage backup. He Was super nice and professional. We loved working with him!
Great installation of new boiler. Left basement immaculate.
Great service from nat
I arrived to find the humidity was high. Upstairs the humidity was much higher. We have decided to add a whole home dehumidifier.
Upon arrival customer took me to the basement where water has been leaking. There is an active leak coming from two areas hydrant which isnâ€™t leaking when in the off position. And from inside of wall. I showed him options and he decided to wait and talk to insurance. And paid the service call
Upon arrival the customer informed me that their upstairs AC unit was not running at all. Additionally the customer stated that they have checked all the breakers and they seem to be energized but the unit still wasnâ€™t responding. After further investigations I discovered that the float switch in the auxiliary drain pan was open due to water being in the pan. I determined that there was a blockage in the condensation line that was preventing the water/condensation to escape through the pipe. I presented repair options to the customer and they chose the band aid level water removal system rejuvenation. Work completed included: Purging out the line with compressed nitrogen, emptying all of the water out of the condensation pan and auxiliary pan, applying condensation pan treatment tabs and performing a quick operations check to ensure the water removal system was operating as it should. After completing the repair, I discovered that the refrigeration circulating pump was not operati
Check second floor unit for no cooling. Found compressors locked out on high pressure. Discovered condenser fan #2 shorted to ground. Informed Mark of findings and her approved repairs over the phone. The next day I located parts in town and pick them up from supplier. Return that morning and replace condenser fan# 2 along with blade and fuse. Confirmed cooling operation the unit. The unit is cooling fine now.
I get there and the customer said he needed plumbing work estimated and that he was already quoted his hvac work by someone else.
Arrived to find system operating properly. When system shuts off it makes a noise depending where the refrigerant is within the system. So the system will make some noise. System is operating within factory specifications at this time.
Check all three units #1 and #2 were working fine but unit #3 was was not operating. Found one leg of power was not connecting fully. I check the breaker panel. It was fine so I found the only connection in between the breaker box and the disconnect at the roof and found one of the wire nuts to have come loos in a junction box on the roof next to the unit. I tightened the two wires and taped the wire nut. Tested functions of unit #3 and everything is working fine. Warranty no cost to the customer.
Assisted with service. Cody billed for my hours
Upon arrival checked 5420-6 found failed board replaced now operating well also found 5408-2 with a short to ground compressor found 5512-7 with a damaged motor and blade estimate to replace asblade will not arrive until tommorw and found failed transformer on 5500-4 replaced and now operating well. Replace condenser fan motor and blade for space 5512-7 found damged
Installed new 40 gallon gas hot water heater with code upgrades.
Performed pma inspection and filter change. Wash condenser coils, flush condensate drains, test electrical components, check fan motors and belts. Test cooling operations.
Homeowner only wants lining done sewer line is 14â€™-15â€™ deep under large shed. He will call back if nobody can do what he wants
Upon arrival the customers floor drain in the basement was backing up from the sewer. Customer told me last time they got the main line cabled they brought back roots. I cabled the main line and brought back lots of roots. Then I ran gallons of water to see if the main line was still backing up. Everything tested good.
Upon arrival found that refridgerant pump compressor was out on internal overload. Cooled down the compressor with water from the hose to allow compressor to be operating within optimal factory temperatures. Found that the voltage enhancement system was not distributing the correct amount of power to operate the refrigerant pump compressor. Proposed options to customer and customer chose silver option allowing me to complete all silver repairs today system is now operating with factory specifications. Will return for boiler maintenance this fall.
Replace existing 40 gallon gas hot water heater with all code upgrades.