The technician did a great job
Michael did a great job!
From start to finish, the guys at LBA were phenomenal! If you’re looking for a company to meet and exceed your heating and plumbing needs, stop looking! You have found them! Not only did Kevin install my plumping needs, exactly as I wanted. He went ahead and upgraded my hot/cold washer lines, potentially avoiding an expensive and messy disaster. If that wasn’t enough, he actually patched more than a few holes in my garage, without hesitation. And all the work done by LBA is backed by a 1 year warranty! Long story short, I am more than happy with the services provided by LBA and will refer all friends and family, who want friendly, professional, heating and plumbing work done. Thanks again LBA!
Pat was very reasonable on price and a friendly guy. Kevin will be here tomorrow to install a mop sink. So far so good.
Diagnosed the problem quickly. Very thorough.
Nice team and very helpful in resolving cooling issues.
Arrived on site to gather information on adding a vent to the day room for additional cooling. I found that the best way to get cooling in the data room would be adding an additional vav box just for the data room. I have submitted the information to my boss and he will be sending a quote
7/11/19--Checked the Col-met paint booth for no operation after a power surge yesterday. Found the booth lighting contactor with the coil shorted, the 5 amp fuse for the curcuit blown and the fan curcuit relay with the contacte welded. Replaced all three. Started the booth and found the coil shorted for the intake and exhaust fan contactor. Will pick up the contactor and return to finish as the shop is closing for the day. 7/12/19--Replaced the contactor. Started the booth and checked operation. Found the booth operation normal with the exception of the cool down timer. Will pick up the part and return to finish. Booth is operational without the timer. 7/17/19--Replaced the timer. Verified operation in spray, bake and cool down.
Replaced batteries in first stahl in menâ€™s restroom and tested for operations. Replaced automatic flush valve mechanism on handicap stahl in womenâ€™s restroom and tested for operations. Measured domestic water temperature at all hand sinks, found temps to be no hotter than 105-111. Within health department standards.
Systems voltage enhancement system was found the be out of variance at this time. Spoke with customer about repairs and customer chose the gold uptown at this time. Replaced the voltage enhancement system as well as the voltage distribution system. Washed out the outdoor unit with extensive coil cleaner. System is operating within factory specifications at this time.
Completed cooling tune up, everything tested as it should at this time, changed filter and thoroughly cleaned unit
Checked the three Trane Rtus for comfort complaints. Found the North unit cooling normal with a 20 deg split. Found the center unit with the thermostat bypassed by others due to a short in the thermostat wires. Located the short in the green blower wire. Replaced the green wire with the unused blue wire. Verified operation with a 20 deg split. Found the South unit with a short to ground compressor and the electrical plug blown out. Quoted replacing the compressor and passed unit information to Zach for quoting the unit replacement. Washed the dirty condensers in the North and center units for maximum capacity.
Arrived to find water removal system clogged. Showed customer options customer chose silver option. Performed all work under the silver option. Also removed all water in the drain pan. Performed safety testing to insure system is operating properly at this time.
Upon arrival Thermostat was reading code 53. Code 53 means a fault in the outdoor temperature sensor. Customer chose platinum repair allowing me to replace the outdoor sensor and itâ€™s low-voltage lines as well as replace the outdoor refrigeration line insulation. checked all operations in the cooling mode and washed out the outdoor unit performing a P3 maintenance on the air-conditioner. Will not need maintenance until fall service.
Installed mini-split in garage/art room .Tested operation.
Upon arrival customer stated that system was not cooling at this time. Upon further inspection found that the systems voltage enhancement system was out of variance at this time. Spoke with customer about repairs and customer chose the gold option at this time. Replaced voltage enhancement system, voltage distribution as well as extensive out coiling cleaning performed as well. System is operating within specifications at this time
Temperature and pressure relief needs replaced per home inspection.
PMA for B - Office / Common and D - Phone Room
PMA for B2's, J- Public RR, and E1
Performed a Two full cooling inspections. Washed and cleaned outdoor units. Checked all wires and safety switches. Units are operating within factory specifications
Found that unit had gone of on high pressure due to painters covering unit