Izzy was knowledgeable, professional, and courteous. He did did a great job and also explained his recommendations and rationale very well!
The service man was very nice.
What happened to getting the filter replaced?
Thanks LBA for the great service today! Fast and efficient!
Estimate was not given by the day given. Phone call to office has not resulted in a solution still waiting
Easy to get appointment, friendly yet professional. Problem taken care of ASAP. Reasonable price.
Upon arrival, the customer informed me that the Rheem RGPS-07EAMER furnace system wasnâ€™t operating properly. They went on to tell me that it seemed like it was trying to operate but the flames would drop out and only cold air came out of the supply vents. After further investigations, I discovered that the flame sensor was reading a low microamp reading and wasnâ€™t able to prove flame due to the flame sensor being dirty. I spoke with the customer about my discoveries and presented repair options. The customer chose the bronze level HM15B basic flame safety system renovation option. At this time I cleaned the flame sensor and afterwards I recorded a microamp reading range of 2.8-3.5 whereas upon arrival the readings were .2-1. The customer chose the bronze level for replacement of the component which I will complete Thursday 1-23-20 during the furnace tuneup. The customer used their synchrony credit line to pay for todayâ€™s services. Thank you
Upon arrival main line had backed up through floor drain in basement. Warranty service confirmed Ran auger 100â€™ . Hit obstruction at approximately 35â€™. Suggest camera be ran
Upon arrival commode was slow filling due to buildup in lines. Replace short portion of water line and installed new stop.
Complete a furnace tuneup and safety inspection on furnace. All safety switches are working to their specification. Perform the indoor blower test, indoor blower motor is working within guidelines. Recommend cleaning blower motor. performed an electrical test, high-voltage and low-voltage communicating properly within furnace. combustion motor is recommended to operate no higher than 1.92 A it is operating at 1.9 A. Would recommend replacing combustion motor. Due to the age of the unit Gave customer options for repairs but also recommended may be looking at options of a new system.
Performed a safety inspection, all safety switches are working to specification. Cleaned all safety switches in recalibrated. Performed combustion analysis, combustion motor is operating within guidelines. carbon monoxide is being pushed out of the house properly. Performed electrical test, all electrical from low-voltage wiring to high-voltage wiring communicating properly. Performed indoor blower test, indoor blower motor is working within specification.Furnace is running to specification. Would recommend cleaning blower motor. Also water heaters from 2001 would highly recommend replacing water heater. Does deteriorate on the inside, recommended lifetime 12 to 15 years
Upon arrival, the customer informed me that the Lennox G43UF furnace system was making a loud and unusual noise while operating. After further investigations, I discovered that the inducer assembly is responsible for the noise. The customer requested that I look at the blower motor as well. The VEC serving the blower motor tested outside of the manufacturers tolerance so I recommended that that component be replaced but I found the blower motor to be in good working order. The inducer is pulling 2.2 amps and the motor is rated at 2.35 amps. I tightened the motor to the inducer housing, the housing to the collector box and the collector box to the furnace attempting to resolve the noise caused by vibrations which the noise remained. Something in the inducer assembly is out of balance which is causing the abnormal vibrations in turn creating the noise. Lennox inducer assembly part number 83m56. The customer chose the gold level HM8D complete combustion exhaust renovation option but has
Performed a safety inspection, all safety switches were responding to manufacture specification. Performed combustion check, combustion motor is operating within manufacture guidelines and properly distributing carbon monoxide out of the house. Performed indoor blower test, indoor blower motor is working for specifications. Would recommend a deep cleaning on blower motor. Performed an electrical test, 120 V going to furnace secure and stable at furnace. Low-voltage wiring secure and stable from board to thermostat. Low-voltage wiring communicating properly. Furnace is working to manufacture specification.
Performed furnace tuneup, all safety switches were corresponding to specification. Completely cleaned safety switches and recalibrated. Performed an electrical test, 120 V going to furnace Secure and stable at furnace. Low-voltage wiring stable and secure from thermostat to board. Low-voltage wiring communicating properly. Performed combustion analysis, combustion motor is operating within guidelines and properly pushing carbon monoxide out of the house.Completely cleaned all cabinet space with the furnace would recommend doing a deep clean on blower motor and blower motor wheel. Could cause restrictions down the line and failures. Furnace is working to manufacture Specifications.
Made adjustment to Toto flush valve on left side urinal on 3rd floor, service performed under warranty by LBA. Tested for operations and also adjusted water pressure. No charge.
Today I completed your annual heating tune up, I checked all safety and electrical devices to ensure your system is running safely and efficiently, I cleaned system performed combustion analysis, checked for proper heating transfer, recommended replacing downstairs system due to a very rusty heat exchanger, everything else tested as it should at this time, thanks for choosing Lba, Eli
Hot water heater goes out. I relit water heater and called tech support and went through diagnostic. They said gas company needs to come out and check gas pressure. They suspect chamber sensor has failed . Relit water heater.
Installed uv light bulb... customer is very happy
Upon arrival customer took me to the drinking fountain. They have been getting a sewer gas smell. I removed cover from drinking fountain. And it didnâ€™t have a p-trap it was piped without p-trap. And due to incorrect rough in adding a p-trap isnâ€™t possible. Customer told me to remove it and cap waist and water.
Upon arrival master bath toilet was backed up with paper. Work done: Augered commode and test with water and paper
Replace the inducer motor and fan with a customer provided motor and us providing the fan Replace the inducer motor and the inducer fan and tested the system and heat mode. The furnace is running every time I turn it on with no apparent issues.