Love working with Angelina but your prices are way too high.
Very knowledgeable. Friendly. Accommodating
He took us through the proposals professionally.
Nathaniel was here bright and early in the morning. He had the problem resolved in a few minutes.
Nate was great...quick, friendly and professional. And I was not overchy
I was not able to finish diagnosing the no cooling issue due to heavy rain and lightning. Will return to finish job
Completed air conditioning tune up, repaired low voltage circuit. Everything else tested as it should at this time
Estimate for bathroom rough in and laundry rough in installing cust supplied water heater
Installed sump pump
Unit was found to have a loose thermostat wire at the control panel. Wire was reconnected, and cooling functions have been inspected. This unit has already been quoted for repairs found during the PMA inspection. Unit has a high temperature coil split. Unit blower motor needs to be further inspected for proper airflow. Further inspection may need to be conducted to ensure the unit is charged properly. Service performed today will not be billed on the invoice. PMA inspection was recently conducted, and correcting wiring issues is apart of the PMA check outs.
We performed the full cooling maintenance on 2 rooftop hvac units. We washed the condenser coils, cleaned the condensate drain traps and economizer filters, checked all electrical and mechanical components. We noted several deficiencies for both units. Rtu 1 is currently not operating properly. Please see the checkout sheets and repair estimates for additional details.
In the menâ€™s bathroom the toilet kept running when flushed. I replaced the old diaphragm with a new one and tested by flushing lots of water. Everything tested good.
Customer had sump pump in the basement that failed, it was approximately 20 years give or take a couple years. I replaced the pump but also installed a check valve To protect the pump from short cycling. After installation I tested for leaks everything good. I also used zip ties to straighten the electrical wire for pump.
Estimate for new water service
Customers hallway bathroom shower And tub pressure was very low. I replaced the whole shower valve to get rid of the Koehler brand. Also cut a hole in the wall to access the back side. I had to replace the trim kit for the handle. After installation I tested for leaks everything is good.
Performed a full cooling inspection. Washed and cleaned out outdoor unit. Checked all wires and safety switches. Unit is operating within factory specifications at this time. Also changed Merv 16 filter.
Checked the electric furnace for burnt odor and breaker trippage during a heat cycle yesterday. Found the electric heat sequencer with the M1 and M2 contacts burnt up and the the wiring damaged. Replaced the sequencer and repaired the wires. Verified operation after repairs.
Customer has battery backup sump pump check valve that needs replaced. The customer has it sealed at this time and would like regular hours for the repairs. We will have to call in the morning to schedule a time to come back out.
Customer was not onsite had to e mail quote .
I found the system very low on refrigerant. We discussed tho options of replacing the coil or charging the system and adding a leak sealing treatment. Based on age of the equipment and the fact that they are going to get new systems in two years we decided to go with the refrigerant and sealer. After charge Superheat 17 Subcool 5