Andrew Graves was the best. Skilled, kind, caring, and diligent. He was on top of parts and service for my boiler. He brought heat back to my home and my will you live! Lol heat is everything. And I think LBA and Andrew for restoring mine.
Did a wonderful job.
We have been with LBA for many, many years. They have always taken care of our needs, quality service, great technicians, very professional, really know what they are doing. Thanks LBA!!!
Technicians were thorough, neat and professional
Completed furnace tune up, humidifier had been shut off. Changed filter for 2nd floor, main floor filter still good. Completed a combustion motor test 2nd floor over amping, first floor reading right at the highest amperage. Blower motor to 2nd and first floor reading accurate. Inspected high-voltage and low-voltage wiring, for both systems the high voltage and low voltage wired into ports and secured properly. Performed a gas leak inspection none found. Cleaned all safety switches and recalibrated. Checked drains for 90% furnace, draining properly. Informed customer the heat exchanger is starting to accumulate a lot of rust, On main floor inspected furnace for any heat exchanger cracks. None were found. Due to the age of the systems any minor or major components may fail at any time.
Today I completed your annual heating tune up, I checked all safety and electrical devices to ensure your system is running safely and efficiently, I cleaned system, performed combustion analysis, checked for proper heating transfer, tested humidifier operations, everything tested as it should at this time, thanks for choosing Lba, Eli
I conducted a performance and safety inspection for the furnace. During the inspection, I found that the thermostat was not reading the indoor humidity accurately. I replaced the thermostat under the manufacturers Parts warranty.
I returned to replace the blower wheel and housing for the third level air handler.
I returned to make repairs to the boiler system. The rails that support the burners had rusted and failed allowing the burners to fall to the floor and that created a dangerous combustion scenario. I ordered parts next day air and made the repair today 11-15-19. After completing the repair I tested the performance and safe operation of the boiler system. Additionally, I bled all the air out of the circuit. The boiler system is again operational. The lowest radiator has a restriction and isnâ€™t allowing water to flow correctly. I brought this to the customers attention but due to the location and little need for heat in the area it provides, the customer isnâ€™t interested in repairs. Additionally, the customer purchased an annual recurring boiler P3 membership with us. Per Scott, we will be providing a new estimate for replacement equipment because we originally quoted a steam boiler replacement and the system is in fact a hot water boiler. Scott will also do everything that is poss
Performed routine maintenance per contract. Checked (2) 3 ton units, (1) 5 ton (1) 6 ton, (1) 8.5 ton (2) 10 ton, 1 (20) ton. Changed filters and checked all electrical components and heating components. Issues were found on 5 units, 3 had no electrical power. 2 need blowers cleaned and belts tightened. 1 unit is operating at 50 percent heating capacity due to a faulty gas. Please see accompanying repair proposal for details. All other units are operating properly at this time.
Check 2 Cambridge Engineering units for no heating. Found north unit not heating because of a open air temperature sensor. Sensor will need to be replaced to get unit operational. Found no power to north unit. Trace conduit down to electrical panel found all breakers in the on position. Advised customer to contact an electrician.
Remove waist piping and install new rough plumbing. Waist only. No sheet rock repair.
Quoted to repairs for hot water issue.
We will have to come back on another day to do the work. Customer will schedule for the water to the building to be turned off. Collecting trip charge today.
In the back of the house under the deck I replaced the outside hydrant. Tested for leaks after and everything tested good.
Performed PMA on 7 rooftop units. Replace air filters, checked all electrical and mechanical. Created estimates for repairs found. The smaller building across the parking lot has two rooftop units and both have cracked heat exchangers and had to be shut down for safety. I check with the manufacturer. These heat exchangers are still under factory warranty but it will take two to three days to get once we order them. The factory warranty covers the part but not installation. Rooftop number five is also not heating you to a safety flame rollout switch that needs to be replaced. For further information please see check out sheets and estimates.
Purchase Order: 3600136394
Check twin furnace # 2-west for no heat. Found bad blower run capacitor. Replace capacitor and confirmed furnace operation. The furnace is heating properly now.
Performed the preventive maintenance for the heating season. I checked the amp draw of the blower motor and inducer motor, I made sure that the blower wheel and belt were in good working condition, I took readings of the capacitor to make sure that it was within the manufacturer's recommended tolerance, I looked over the heat exchanger to make sure there were no cracks or holes, I took a temperature split reading and I changed the filters.