We have been a customer for many years. The technicians are friendly and professional. Communication is timely and the recommendations are helpful.
Courteous and efficient
Fast service. Hugely overpriced, so elected to do it myself.
We had a very good experience with your serviceman. Thank you for sending him. we would like to have him next time.
Very happy with the LBA service. They called to ask if their technician can come earlier than scheduled and Andrew arrived on time. He was friendly and professional.
Arrived to find the ignition system has failed showed customer options. Customer chose bottom option. Replaced ignition system and performed safety testing. Unit is now heating properly at this time.
Upon arrival moen kitchen faucet with motion sense was leaking under handle. No other leaks found under cabinet. Work Done: Replaced cartridges and seals in fixture. Disassembled, cleaned, and removed any debris from any reasonably accessible water way. Replaced batteries in motion sense faucet and checked for proper function. Cleaned workspace.
Replaced evaporator coil that has a leak with new evaporator coil.
Performed pma inspection. Found the east Lennox RTU NON operational do to a shorted service disconnect. The west Lennox Rtu is operating properly at this time with no issues.
Replace garbage disposal. Bronze package with a six month warranty. Installed and checked operation.
arrived at the home the wire size was 8/3 on a 30 amp breaker, max on unit is 35 amps the minimum was 30 amps. This is the preferred size for this amperage. I read the inspectors note he was worried the wire was too big. He also wanted us to put a few staples on the wire. I completed his task.
Due to the weather and metal rooftop we Will need to reschedule for another time to come back next week to finish the maintenance on the rooftop units and exhaust fans.
Were unable to finish pma due to the weather. We will come back next week to clean the coils and check the exhaust fans
We finished the scheduled maintenance and safety inspections on 13 RTUs and mini split. Most of the RTUs are operating properly However a few have issues. We will send quotes after we finish the whole building.
Assisted with maintenance
Assisted with maintenance
Assisted Jerry with pma
Performed PMA. Replaced air filters, cleaned condensers, condensate drains, and economizer filters. Tested cooling functions, checked all electrical, and mechanical components. For further information please see check out sheets and estimates.
Conducted CPMA on (6) RTUs and (1) split system. Inspected all electrical and mechanical cooling operations. Inspected all motors and capacitors electrical tolerances. Inspected condition of the blower wheel, and belts. Cleaned all outdoor coils, and replaced all filters. Checked for correct cooling temperatures. All deficiencies have been quoted for repairs.
Checked all operations in the cooling mode. Furnace filters are OK at this time. Found outdoor unit to be extremely dirty upon customers request performed an extensive coil clean on both units. Found main floor system to be low on refrigerant proceeded to perform an electronica leak search and found a leak in the heat media transfer coil. After speaking with customer customer decided to replace heat media transfer coil a $425 credit was applied from the manufacture towards this repair. Will return April 3, 2020 to perform and Complete quoted repairs