Rick is very good. I trust his assessments and advice.
Our technician Rick, does an excellent job of explaining the issues with our systems and then actually performing the repairs. We feel very comfortable with his integrity and skills.
Checked the drive thru split system for no cool. Found the blowers running on the twin furnaces with no condenser operation. Found the breaker off to the condenser in the breaker box in the mechanical room. Turned on the breaker and verified operation. Evaporator split was 22-23 degrees after restoring power to the condenser. Customer advised that there was a electrican on site yesterday making repairs. Appears that the breaker was turned off during electrical repairs by mistake.
Checked the building for comfort issues, customer noted that the unit in the drive thru section runs more than the lobby area unit. Verified the operation of both systems in cooling. Checked the supply registers and found the drive thru system serving the north areas of the lobby causing the complaints. Explained the layout of the registers to Bob. Advised without zoning the two systems the issues will continue. Customer will ajust the thermostats to overcome the mixed zones.
10/22/19-Checked the twin gas furnaces for the lobby for no heat. Found the blower motor and control board failed in the right side unit. Found the smart gas valve failed in the left unit. Will pick up parts and return to make the repairs---10/23/19-made repairs to the twin furnaces. Verified operation in heat and cool. Repairs were approved by Bob Nauman.
Lennox heat pump with not shut off
Advised customer on the operations of the heat pump/ air handler and the set points on the thermostat.
Straighten out low voltage wiring at air handler on the add a wire control
$88.00 to us postcard special needs do run capacitor out of range customer wants to wait for now on the repair