Andrew was very knowledgeable and communicated well
Easy guy was very nice and respectful
Wish there had been a bit more clean up afterwards. Other than that it was great
Zach and Travis were very knowledgeable! They informed me every step of the way.
***VEC serving air movement system tested 4.3 outside of manufacturers tolerance*** ***air movement system fault. Motor bearings worn allowing side to side shaft movement*** I performed a safety and maintenance inspection on the furnace system. During my inspection I discovered two faults within the air movement system. First fault I discovered was that the voltage enhancement component tested outside of the manufacturers tolerance. Second fault was the motor serving the air movement system, the bearings were worn to the point that the shaft was allowed to have side to side movement. I explained my concerns to the customer and went into detail as to what to look out for and listen for in the progression of symptoms if no repair was made at this time. I presented repair options to the customer and the customer chose the silver level HC4C main air movement system renovation option. Work completed included removal and replacement of the air movement motor and voltage enhancement componen
Completed final installation of all fixtures for master bath addition, installed customer supplied soaking tub faucet and tested all fixtures for operations . Everything working as it should at this time. ( project is completed).
Set toilet complete, set two sinks with customer supplied fixtures, turned on water and tested for leaks, none found at this time. Customer needs to make access for me to be able to install customer supplied soaking tub faucet and will then be completed.
Attempted to determine the max gpm flow rate , would have to shut down water system and cut full port into 1 1/2 to be 100% sure and also to perform draw test.
Slow floor drain ran machine branch line . 30 day warranty bandaid repair
Estimate for plumbing work
Installed compression stops for all fixtures, installed shower trims less/ body sprays, set toilet bowl only due to painting needed. Still need return visit to install body sprays and finish setting tub and faucet. Friday- Cut in drain for soaking tub. Cut out opening to correct size for tub. Installed under mount soaking tub with waste and also trapped, and tested for leaks. Installed body sprays in corner shower. Also made access in drywall to trap tub, not to be responsible for any repairs. Finish is complete less installing tub faucet if needed. Noted: customer not available for payment at time of completion, left voicemail.
After customer chose option.I removed old tub shower valve. And installed new tub shower valve wall rough. Left trim kit with owner minus tub spout. After owner is done with wall they will call us and we will set trim . At no cost.
Arrived to find unit operating properly.. Also check the temp split the return was 75Â° in the supply was 55Â° is a 20Â° temp split. Found thermostat on the same wall as the oven so when the customer uses the oven the oven will heat up the wall and cause the unit to run longer. Unit is operating at factory specifications at this time.
Completed cooling tune up, replaced filter and drain line
Gave estimate for New lav faucets to fix hot water issue
Put in a shut off on the hot side water. Customer got a P3 agreement with us. Turns out the shower valve is bad and needs replaced. Customer said they will remodel the bathroom and will give us a call back to repipe.
Plumbing inspection of whole house