Doug arrived to finish previous work started by another technician. There were a few hurdles to overcome, but Doug was insightful, efficient and professional. His experience was on full display, and I appreciate his advice.
Andrew was very knowledgeable and communicated well
Easy guy was very nice and respectful
Wish there had been a bit more clean up afterwards. Other than that it was great
Returned to customers residents to do a quality check on previous install. Re-ran gas piping from furnace to the existing gas Line, re-attached gas piping hangers to support gas line. Also re-routed water heater gas line so the new humidifier would be able to be serviced. Disconnected the flexible gas line from water heater and hard piped the water heater with black iron. Removed all the water in the water heater overflow pan before lighting water heater. Sealed around the roof jack where the pvc flue penetrates roof. Also added a piece of 2" pvc to the top of concentric kit so that the escaping flue gases from the furnace would not get sucked into the intake of the concentric kit.
Found that drain line for furnace and humidifier were ran into emergency drain pan to water heater, ran drain lines to dedicated drain pipe
Performed furnace tuneup on two systems, performed safety inspection on both systems. All safety switches are corresponding correctly, completely clean and re-calibrate to safety switches. System closer to garage has a crack on Secondary heat exchanger. Would have to take primary and secondary exchanger out and replace both. Second system downstairs heat exchanger is intact and performing to specification. Performed an electrical test, high voltage stable and secure at furnace 120 V communicating properly. Low-voltage wiring stable and secure at board and thermostat. Low voltage wiring communicating properly. Second furnace in basement is performing to manufacture specification. Gave customer options and recommendation for replacing heat exchanger. Customer has scheduled an appointment with Scott to go over options. Scott will be out tomorrow at 9 AM
Estimate for joco sump pump
Performed a full heating and humidifier inspection. Checked all wires and safety switches. Cleaned indoor units. Systems are operating within factory specifications at this time.
Installed complete tub/shower trim and checked for operations in downstairs hall bath.
I preformed a whole home plumbing inspection.
Checked all operations in the heating mode. Cleaned out housing a furnace and tested all operations of all safety switches. Furnace filter was ok at this time. system is now operating within factory specifications.
***VEC serving air movement system tested 4.3 outside of manufacturers tolerance*** ***air movement system fault. Motor bearings worn allowing side to side shaft movement*** I performed a safety and maintenance inspection on the furnace system. During my inspection I discovered two faults within the air movement system. First fault I discovered was that the voltage enhancement component tested outside of the manufacturers tolerance. Second fault was the motor serving the air movement system, the bearings were worn to the point that the shaft was allowed to have side to side movement. I explained my concerns to the customer and went into detail as to what to look out for and listen for in the progression of symptoms if no repair was made at this time. I presented repair options to the customer and the customer chose the silver level HC4C main air movement system renovation option. Work completed included removal and replacement of the air movement motor and voltage enhancement componen
Completed final installation of all fixtures for master bath addition, installed customer supplied soaking tub faucet and tested all fixtures for operations . Everything working as it should at this time. ( project is completed).
Set toilet complete, set two sinks with customer supplied fixtures, turned on water and tested for leaks, none found at this time. Customer needs to make access for me to be able to install customer supplied soaking tub faucet and will then be completed.
Attempted to determine the max gpm flow rate , would have to shut down water system and cut full port into 1 1/2 to be 100% sure and also to perform draw test.
Slow floor drain ran machine branch line . 30 day warranty bandaid repair
Estimate for plumbing work