Kevin helped me understand my Heating and air. Kevin is the only guy I want at my House. kim and Bill Hickey
Warranty call company installed electric Rudd water heater for warranty and customer called back in saying that water was still not hot. Upon arrival noticed tankless system feeding hot water tank temperature was set at 135 and heating elements in Rudd tank were factory set at 115 Causing elements to trip on relay system. Went ahead and pushed reset button On heater and elements started firing then adjusted temperature to 125 on both elements and turn the temperature down on tankless system going into tank itself to prevent water heater from overheating. After turning heater back on water started to heat back up use temperature gauge to test water after waiting 10 to 15 minutes and water temperature was up to 120 and still climbing checked voltage on both elements in both elements are firing properly everything is testing OK at this time.
Customers two year old Ruud 50 gallon electric water heater is leaking from base. Went Ahead and checked pressure on household itself, pressure regulating valve and thermal expansion tank or operational customers incoming pressure is at 65 psi so company can honor manufacture warranty on replacement of tank itself. Company will also replace 4.5 gallon expansion tank and Company Will honor 30 day installation warranty on new heater expansion tank. Company returned following day on August 6, 2020 to conducted warranty swap out of 50 gallon electric ruud water heater. Company Also installed two new ball shut offâ€™s for hot and cold side, New 4 gallon expansion tank with pressure set at 68 psi. After installation was complete turned water on to test all fittings and fill tank itself after tank was full turned on electric elements to start heating tank itself, Can conclude that installation is testing OK at this time and customer will have 30 day warranty on installation itself. Thank yo
Performed an air conditioner tuneup and safety inspection. Air conditioner is operating and working to manufacture specification based on compressor motor and fan motor readings, refrigerant levels. indoor temp Difference 20Â°. Performed a safety inspection, condensation drain draining properly. Electronic air cleaner, cleaned filters for electronic air cleaner. All high-voltage and low-voltage wiring stable and secure. 240 v properly supplied air conditioner And Low-voltage wire communicating properly.
Job is to big for service I will discuss with construction about doing it
I performed a safety and maintenance inspection on both the furnace system and the AC. I found everything to be operating within the manufacturers tolerances on both systems at this time. I performed a thorough cleaning of the outdoor unit and the blower wheel/compartment. The customer purchased a Merv 13 replacement filter today. Thank you
I arrived to find the condenser very dirty, not allowing the extraction of heat from the house. When I checked the filter it was very dirty and wet. I checked the refrigerant levels and they are fine. I cleaned the condenser and replaced the filter with a customer provided filter.
Installed new recirculating pump
Sump pump out
Leak search in basement
Trane spring ac tune up preventive maintenance
Replace outside hydrants.