The furnace barely fit thru the access point but it was accomplished admirably. I’m very pleased with Randy and Walter. They were polite, efficient and quick
Regretfully he only checked 1 of 3 units.
Didn't get a chance to spend much time with him, as I'm recovering from surgery! My wife was impressed, and that takes a lot.
Jason was courteous, worked quickly, and explained everything.
I am pleased to say, I loved Matthew, he was friendly, very professional and knows his stuff. I am very very pleased with his service. I will be contacting him in the near future.
Kent was kind & knowledgeable about the work being done.
Angelina has the technical skills and the “people “ skills that make her an asset to LBA, and a pleasure to deal with as a customer.
Found that thermostat and furnace were not wired correctly,
Furnace ac and pump
Water got on the circuit board, the blower motor comes on but does not stay on. Itâ€™s been running for 15 minutes now.
Lennox RTU not cooling properly. Condenser fan run capacitor was found to be failed. Capacitor has been replace. Unit was found low on charge. Unit has been charged with 3 lbs. of r22. System is cooling properly at this time.
Conducted preventative maintenance on 2 Lennox RTU system, and 1 Mitsubishi mini split. Inspected all units for proper cooling functions. Checked all electrical and mchanical operation. Checked all motors and capacitors for proper electrical tolerances. Cleaned all coils and washable filters. All filters have been changed. All deficiencies have been quote for repair.
Completed the following recommended repairs that were noted during the cooling pma. Rtu 1 (front unit) : Replace the 2 pole blower contactor that was found to have some moderate pitting. Replace and tighten the AX62 belt. Connect gages to check the refrigerant charge. Rtu 2 (middle unit): Replace the condensate drain trap. Rtu 3 (back unit) : Replace the AX54 belt, adjust the pulley to increase airflow, and replace the drain trap.
I arrived to find that the furnace had water damage inside the air circulation compartment. After further testing, I found that the control circuit and the air movement system was not working due to water damage. I presented repair options to the customer and the customer chose the bronze repair option for the air movement system and the basic repair for the control circuit. After making the repairs, I tested cooling operations and the system is now cooling properly at this time.
Customer called about a water leak in garage. We started our search for the leak in the garage. We ran water in master bathroom shower,lav,and toilet. No leaks found. Upon further inspection. We traced 3 inch vent through roof and saw day light. Customer had said.they saw water in garage after rain. Collecting trip charge and diagnostic fee.
Showed up to the landlords address to look at the water heater. The tenant was home and let us diagnose the issue with the water heater. I call the landlord to get authorization to do the work and the landlord never answer the phone. I called twice and left a voice message. The office also called and left a voicemail as well. We will bill the trip charge.
I performed the full cooling pma. I changed the filters, washed the condenser coils, and checked the electrical and mechanical components of the units. Please see the checkout sheets and repair quote for additional details.
Found unit number 3 out on high head pressure not bringing on condenser fan motor upon further diagnoses found capacitor not sending proper voltage to the motor replaced with customer supplied 7.5 capacitor and unit is now operating properly.
Installed warranty blower wheel for mini split unit.
Conducted preventative maintenance on all air conditioning units. Inspected the electrical and mechanical cooling operations. Inspected the condition of the blower wheel, and bearings. Inspected the indoor coil temperature difference to ensure correct cooling charge. All coils have been washed. All filters have been changed. There are no deficiencies at this time.
Completed installation of new compressor on unit 54 circuit 1 including acid away and new filter drier now operating well used 6 lbs of customer supplied R22 and 1-4l500 belt also reconnected low pressure switches both found operational original leak was found to be from a leaking schraeder port that had no cap replaced core and installed all new caps unit now operating well.
Upon arrival found server room unit 54 tripping breaker found second circuit out of refrigerant with an electrically failed compressor and low pressure switches disconnected also found crack in the belt price to repair and replace to be sent over