Great service. Found problem with humidifier and corrected as part of annual service
Doug was great and a true professional. Fixed my problem by going above and beyond. Would request him anytime I have a plumbing need.
We’ve always received great service from LBA, but this was especially good. Austin Jones should be counted as an excellent representative of LBA. He was courteous, effecient , and conscientious.
The best professional service ever!
The furnace barely fit thru the access point but it was accomplished admirably. I’m very pleased with Randy and Walter. They were polite, efficient and quick
Regretfully he only checked 1 of 3 units.
Didn't get a chance to spend much time with him, as I'm recovering from surgery! My wife was impressed, and that takes a lot.
Arrived to home January 21st. Customers kitchen faucet leaking from base. Gave customer estimate to repair and to replace kitchen faucet. Customer chose to replace kitchen faucet. Made trip to Home Depot and purchased new kitchen faucet with pull down spray. Return to home and shut off water supply to kitchen faucet. Removed old kitchen faucet. Installed new kitchen faucet and soap dispenser. Tested new kitchen faucet for leaks and proper function. New kitchen faucet now works properly with no issues. Kitchen faucet installation will have 30 day warranty through company. Thank you for choosing LBA have a wonderful day
Replaced 50 gallon water heater and added an expansion tank re worked gas pipe and changed flue over to 4â€ flue pipe.
Performed furnace maintenance. Filter does not need replaced. Completed all checks and cleanings. Complete a combustion analysis check for proper/safe operation of a furnace. Recommended replacing humidifier with a steam humidifier to increase humidity levels in the home, as well as keeping the water usage down which customer is worried about then humidifier usage. In completing a thorough evaluation of mechanical systems in the home, I found the existing water heater was 21 years old and recommended replacement of the water heater. Customer approved water heater replacement. System is heating and operational at this time.
Customer complaint of unit not heating properly after PM tasking, after PM was finished tech explained to customer about having a crack heat exchanger and a low reading on a dirty flame sensor, during PM tech try to clean dirty sensor and recommend for it to be replace, well the call back today the customer ask for it to be replace , 01/18/2021 tech replaced flame sensor than checked operation of heating mode, at this time unit seem to be working ok
Performed PM tasking on RTUs , change out filters , inspected and tighten up loose belts, recorded motors amp, then checked operation of heating mode During PM inspection tech found crack heat exchanger and a weak flame sensor that both need to be replace on Trane Unit#2 with serial number 242100911L A quote was sent to the customer to replace heat exchanger and flame sensor
Install power bent water heater.
Furnace Maintenance. Performed combustion analysis, checked temperature rise across furnace, performed safety inspection. No issues with furnace at this time. Replaced humidifier panel and repaired gas leak on abandoned line. Removed section of gas line, plugged line, retested, and re lit water water.
Estimates for water heaters. A tankless and power vent. Water heater needs to not be on chimney for safety reasons
Upon arrival urinal, lavatory, and break room sink were all backing up. Attempted to ran large cable through floor clean out, but could not unstop line. Attempted to ran smaller machine through break room sink, but could not unstop line. Reposition and screwed down wall hung lavatory so that drain could be disassembled. Ran auger from lavatory and line finally cleared. Visible cast iron is showing signs of deterioration and is the likely cause of clog.
Upon arrival the customer wanted me to preformed the quoted work on replacing the hydrant in the front of the house with a new hydrant and ball valve shut off. I tested for leaks and everything tested good.
Work completed 12/3 -changed ignition board and tested unit multiple times. Unit working properly at this time. IFC Board is intermittently supplying voltage to the gas valve on an attempt to light. I observed the unit fail to light multiple times. Unit was also able to light at times. I believe this to be related to a failure in the furnace control board. Estimate is to replace the furnace control board. Price includes all parts and labor.
Performed full heating maintenance on 3 RTUs. Changed filters, checked temp rise, checked mechanical and electrical components. Found an issue with Daikin RTU 1 intermittently lighting. Sent estimate for repair.
Ran camera in sewer and left estimates for repair
Price is for installing two air purifiers, one in each Rtu for the customers business. Price includes two RFG model PHI-PKG9-24 purifiers, wiring and labor. 12/01/2020 installed two new air purification system on Lennox RTUS after installed checked operation of new purification system everything is working ok