Doug was great and a true professional. Fixed my problem by going above and beyond. Would request him anytime I have a plumbing need.
We’ve always received great service from LBA, but this was especially good. Austin Jones should be counted as an excellent representative of LBA. He was courteous, effecient , and conscientious.
The best professional service ever!
The furnace barely fit thru the access point but it was accomplished admirably. I’m very pleased with Randy and Walter. They were polite, efficient and quick
Regretfully he only checked 1 of 3 units.
Didn't get a chance to spend much time with him, as I'm recovering from surgery! My wife was impressed, and that takes a lot.
Jason was courteous, worked quickly, and explained everything.
I am pleased to say, I loved Matthew, he was friendly, very professional and knows his stuff. I am very very pleased with his service. I will be contacting him in the near future.
At time of arrival found furnace air filter was heavily compacted with drywall dust and debri causing the system to trip the high limit safety switch. With the clogged filter supply temperature was at 153 and 66 return air Temperature. Customer supplied me with one of his air filters and system is running within manufacturers specs at this time. Supply temperature was at 130 degrees and return at 71.
Reconnected meter. Included in original estimate
*****ATTIC**** Checked air filter, Took heat rise, performed combustion analysis for oxygen level and flu gas, CO Level and flu gas, flu gas temperature, poured and clean the burners, clean the flame sensor, pulled and cleaned the blower motor, Inspected heat exchangerâ€™s. Furnace is working properly at this time.
Whole house plumbing inspection Ruud water heater with thermal expansion tank No Pressure regulator valve Pressure is 80 psi Recommended repairs 1. Master lavatory emergency stops 2. Master lavatory faucet/ pop up assembly 3.guest emergency stops for lavatory
Upon arrival gas had been turned off to home due to a gas leak near furnace. Performed gas test Pressurized line from meter to fixture valves 15lbs. for 15 minutes. Soap tested all fittings Small leak found at gas drops to furnace. Replaced 90,riser, and ball valve to furnace. Pressurized line again and monitored for leaks. Also tested for leaks after valve at furnace only. No leaks found.
Unable to perform gas leak search because gas company has put a lock on the gas meter need to return after gas company unlocks the digital gas meter.
Replaced air filter Merv 13, Replaced water panel number 35, took temperature rise, performed combustion analysis, check flu temperature, CO2 levels, and oxygen in flue gases, Pulled and cleaned the burners, clean flame sensor, pulled in clean blower motor, inspected the heat exchangers, wipe down the inside of the cabinet and the outside. Furnace is working properly at this time.
Customer had pop-up assembly broken in upstairs bathroom. Customer also had new delta showerhead wand he wanted installed in upstairs shower and old shower head move down to master bathroom shower. Went over options with customer and customer chose automatic P3 agreement with company and Band-Aid level repairs on both pop-up assembly and showerhead replacement. Company cannot warranty any customer provided parts of both showerheads. The company can honor 30 day warranty on installations themselves for pop up assembly and shower heads. After running water through both showerheads and filling sink multiple times to test pop up assembly all installations are testing properly at this time.
Customers lavatory sink in upstairs hallway bathroom was clogged. Customer has old lead line conducted band aid level cleaning. Hit blockages at 2 and 6 ft in line brought back sludge and hair. Then installed new p trap and tighten up pop up assembly and tested line multiple times and line is open and flowing properly at this time. Thank you for choosing lba and have a wonderful day.
Rebuild backflow preventer and test three additional backflowsOrder parts
Arrived at customers residence to address high humidity levels in home I replaced a eco net thermostat with another eco net thermostat. The one I replaced was reading 71% rh the new I installed was reading 57% rh. Dan is going to give me a call in a couple of days after letting the system run for a few days, and let me know what the new thermostat is reading. I also used a psychrometer to read the humidity level at his thermostat and it was reading 50%rh. My dry bulb read 74 degrees and my wet build was 62 degrees.
Installed customer supplied faucet on laundry sink in downstairs lower level and tested for operations. Customer aware of work covered is labor only.
Upon arrival I performed a backflow test on two backflow preventer â€˜s. . Backflow serial number 66223 number one check valve held at 5.5 relief valve did not open check valve number two held at 2.2 this back flow did not pass. Backflow serial number 67367 number one check valve held at 7.5 relief valve opened at 1.5 check valve to held at two psi. Iâ€™m ordering a rebuild kit and create an estimate for rebuild and to test three additional backflows
Meet with the customer on site to quote installing two air purifiers in the existing Rtus for the business. Quoted the scope of work. Emailed the quote and the pdf of the air purifiers to Tim Goodheart.
Arrived at residence to find condensation on customers wall by fireplace up close to his vaulted ceiling there is a 2x4 skylight which is approximately 2â€™ away from problem area when checking temp by the problem area it was 80 degrees and the house was 70 degrees. Upon departure the humidity level in house was at 58.