The furnace barely fit thru the access point but it was accomplished admirably. I’m very pleased with Randy and Walter. They were polite, efficient and quick
Regretfully he only checked 1 of 3 units.
Didn't get a chance to spend much time with him, as I'm recovering from surgery! My wife was impressed, and that takes a lot.
Jason was courteous, worked quickly, and explained everything.
I am pleased to say, I loved Matthew, he was friendly, very professional and knows his stuff. I am very very pleased with his service. I will be contacting him in the near future.
Kent was kind & knowledgeable about the work being done.
Angelina has the technical skills and the “people “ skills that make her an asset to LBA, and a pleasure to deal with as a customer.
Toilet shifted bolts slid out of place . Pulled toilet installed plastic Jonny bolts and reset toilet. Call back
Performed a full heating inspection. Checked all wires and safety switches. Also performed a safety inspection of the heat exchanger. Heat exchanger is operating properly at this time. Checked the performance of the system. Unit is operating within factory specifications at this time.
Upon arrival the shower faucet kept leaking. Customer had replaced the old cartridge themselves months ago and couldnâ€™t get the new cartridge to work right. I presented the customer with pricing and the decided to try another cartridge themselves and see if that works. Collecting trip charge today.
Upon arrival customer took me to the master bathroom where the toilet was leaking from the base of toilet and the shut off valve. After showing options customer chose the bronze package. I pulled the toilet and installed a new wax ring. Then I shut off the water and replaced leaking shut off valve. And checked for leaks.
Old prv was starting to fail so I replaced it with a new prv. Everything tested good. Customer had a $25 coupon
Conducted unit inspections on (4) split AC units, and (2) unit heaters. Inspected all cooling and heating functions from the thermostat. Inspected all operating temperatures, motors, blower wheels, and belts. All inspection checkout sheets have been filled out and submitted. All deficiencies have been noted, and quoted for repairs.
Inspected visible plumbing in restrooms and utility closet , basement doesnâ€™t have a ADA accessible restroom , utility room sink has broken drain pipe in wall . All others checked out looked in good working order .
Estimate for sump pump and clean out The biggest problem is with landscaping and gutters. Homeowner said there was 2â€™ of water in backyard. Nothing you do in the house will stop this much water from getting into basement.
Floor drain was backing up so I cabled the line all the way out and poured gallons of water done. Everything tested good.
Apon arrival I found the unit to be cooling with a proper temperature split at the rooftop unit. Inside temperature was not satisfying. I checked the roof top unit for any electrical or mechanical issues and found none. I went back into the suit and started checking supply temperature in the space, this is where I found 3 supply ducts to be disconnected above the grid ceiling. The return air drop is only a foot away from the supply and was pulling the supply air back out of the building. I secured the supply ducts and now we are getting supply air to all rooms. The type of flex duct used in this space is designed for exhaust air not climate controlled air. If we continue to have air flow issues I will recommend us coming out to quote installing the proper ductwork.
Conducted light preventative maintenance. Inspected all electrical wiring. Checked the supply and return temperatures and correct cooling charge. Changed all filters.
Customer concerned with water from around basement tile shower, determined issue is not with plumbing. Believed to be tile grout.
Second stage cooling has shut off on an internal thermal overload. Compressor can not be worked on untill the unit has cooled. ***Second stage cooling not operating properly. Found the compressor was not getting high voltage power from the contactor. Replaced the contact, compressor is now receiving high voltage power but still not operating. Tested the compressor and found the motor has failed internal windings. The compressor will need to be replaced for cooling operations. A quote has been submitted for all repairs.
First stage cooling has a restriction in the drier filter. Filter will need to be replaced for the unit to operate properly. ***Replaced liquid line drier filter. Recovered refrigerant from the first circuit and found the unit to be 13 lbs low on charge. Pressure test shows there is no leak in the line set. Unit has been charged with 13 lbs of r-22. Inspected the liquid line temperature across the drier filter to ensure no restrictions. All repairs have been made, circuit 1 is now cooling properly.
Trane RTU system not cooling properly. Found the first stage cooling to have a restriction in the drier filter. Drier filter needs to be replaced. The second stage cooling compressor has shut off on an internal thermal over load, issues will need to further diagnosed when compressor has cooled off. A quote for all repairs has been submitted.