We’ve always received great service from LBA, but this was especially good. Austin Jones should be counted as an excellent representative of LBA. He was courteous, effecient , and conscientious.
The best professional service ever!
The furnace barely fit thru the access point but it was accomplished admirably. I’m very pleased with Randy and Walter. They were polite, efficient and quick
Regretfully he only checked 1 of 3 units.
Didn't get a chance to spend much time with him, as I'm recovering from surgery! My wife was impressed, and that takes a lot.
Jason was courteous, worked quickly, and explained everything.
I am pleased to say, I loved Matthew, he was friendly, very professional and knows his stuff. I am very very pleased with his service. I will be contacting him in the near future.
Cause of problem was that the a/c had a failed voltage enhancer. Customer chose bandaid repair which allowed me to replace failed enhancer. A/c is also a little low on refrigerant. Presented options and customer decided to decline on recharging the a/c. A/c is currently cooling properly.
In the bathroom in the back of the office the customer wanted me to replace one lavatory faucet next to the toilet. I replaced it with a single handle meon faucet. I tested for leaks and everything tested good.
Apon arrival I found that filter was extremely dirty and causing system to not work as it should. I also found that the drain line was plugged and I Gave customer estimates. He did not want to do any repairs at this time. I did not charge trip charge due to office not quoting. I informed customer I could temporarily unplug drain line for $68 with no warranty or guarantee. Recommended replacing air filter every month. I also noticed that the bearings in the blower motor sounded very rough and I recommended having that replaced.
Conducted HVAC site survey.
I performed a safety and maintenance inspection on all 3 systems. The work I performed included changing all filters, cleaning all condensate drains, checking temperature readings, checking amp readings, and cleaning all 3 outdoor coils. After my inspection I found that the systems operating the basement and the bedrooms were operating within factory specifications at this time. However, I found that the kitchen system had a small leak in the evaporator coil. Customer Wants to have new coil installed. Iâ€™ve attached an estimate with this invoice. Thank you
Estimate for lavatory faucets
Estimate for water heater Flue on existing gas water heater is installed incorrectly. Single wall flue going thru floor boards from basement. Flue will need to be replaced up into house and probably to roof. Recommend electric water heater. Homeowner will need to have electric ran to water heater area
Checked the York Rtu serial number NKKM107999 for the West treatment areas for no cool. Found the 8.5 ton unit off on high pressure. Found the North condenser fan with the motor unplugged and the wires to the motor wrapped up in the South fan blade. Made repairs to the wiring. Routed the wires back to the motor and secured the wires to prevent future issues. Started the unit and verified operation. Found the unit cooling normal with a 21 degree split after repairs. Explained the repairs to Mark the contact on site.
Installed new Zoeller M73 sump pump in basement and tested for operation, also made sure area drain at patio was working properly. Also augered toilet in downstairs and tested out, recommended a replacement due to poorly flushing.(no warranty). Left quote for back up pump only.
Estimate for sump pump and drain
Performed maintenance inspection on a Trane Air conditioner. Checked all the electrical components and refrigerant for proper pressures and temperatures. Filter was clean at this time. Washed outdoor condenser coil. Air conditioner is operating under manufacture specifications.
Installed Ruud 16 seer condenser and coil.
Upon arrival found both the voltage enhancement system and the performance enhancement system had failed at this time and weâ€™re not allowing the refrigerant pump to turn on. After Speaking with customer customer decided to repair both components that had failed. Replaced both components and checked refrigerant charge system is now cooling within factory specifications i also replaced the furnace filter.
Upon arrival the urinal we just worked on was leaking from the shut off key. I had to turn the key all the way on for it to stomp leaking. I checked for any other leaks and tested it by flushing a number of times. There were no leaks and everything tested good.
Performed PMA on the Mitsubishi mini-split. I clean the washable filters, and the condenser coil. Tested the unit in cooling. No recommendations at this time the unit is cooling as design. Customer inform me that we no longer need to maintenance the rooftop units and I informed the office we will be changing the maintenance agreement as soon as possible.