The furnace barely fit thru the access point but it was accomplished admirably. I’m very pleased with Randy and Walter. They were polite, efficient and quick
Regretfully he only checked 1 of 3 units.
Didn't get a chance to spend much time with him, as I'm recovering from surgery! My wife was impressed, and that takes a lot.
Jason was courteous, worked quickly, and explained everything.
I am pleased to say, I loved Matthew, he was friendly, very professional and knows his stuff. I am very very pleased with his service. I will be contacting him in the near future.
Kent was kind & knowledgeable about the work being done.
Angelina has the technical skills and the “people “ skills that make her an asset to LBA, and a pleasure to deal with as a customer.
I arrived to check on a noise they thought might be related to a repair we made on the 11th. I was unable to find any issues with the mini split or any of the three RTUs. The only thing I can think of is the condensation pump running.
Ran camera in sewer. Line is open and draining, was able to go all the way to city sewer. Line gets our normal warranty
Cabled the main line for the 88 dollar special. I brought back roots and test the line by flushing water down it many times. Everything tested good.
Purchase Order: 3600136385
I found the condensate drain line clogged I cleared the line. The blockage was causing condensation to over flow th catch pan.
Checked Rtu for lobby for no heat. Found furnace shut down on fault code #3. Reset fault code and check unit operation. Found mud dauber nest in inducer motor housing preventing motor operation. Removed nest for inducer housing and verified unit operation the unit is heating properly now.
Completed furnace tune up and humidifier tune up. All drains are draining properly. All wiring high voltage and low voltage stable and firm. Safety switches cleaned and recalibrated all cabinet spaces have been cleaned and checked. Combustion performance checked and passed. System is working to manufacturing specifications.
Camera sewer line Give estimate for repair
Upon arrival the customer main line was backing I cabled the line through the cleanout outside on the left side of the house and brought back lots of roots.
Purchase Order: 3600117961
I replaced the circuit board, and tested the furnace and the air conditioning both are working at this time.
Met Phil Marley at the site to look at the process piping issues.
Th circuit board is sending signal to the out door unit and the inducer motor. It is send zero volts to the blower motor. The coil is freezing up and causing more damage.
Met Michael and looked at issues with the process chiller piping to the fermentation tanks. Called Dave V. to check if we were interested in moving forward with repairs. Will return with a plumber to quote repairs. No charge per Dave.
Estimate for sump pump