Always helpful, friendly and professional.
Much appreciated both Dalton (plumbing) and Corbin (AC) Friendly and highly professional
Polite and wonderful service
The service person was early, personable and kept me informed every step of the way. The work was completed quickly and he even changed my furnace filter
Noah did a great job with the plumbing work. He explained things well, and was quick and efficient with the fix. Very happy with the work he did!
Andrew was a great partner in developing the repair/replacement plan for this project. He was flexible, patient and creative and a pleasure to work with on what might have been a long slog.
I was able to schedule an appointment quickly, which was great. Patrick Krisman is a very knowledgeable and patient HVAC technician. He thoroughly evaluated all heating and humidifier equipment and provided recommendations to make the equipment perform better. He kindly answered all my questions about how I could extend the life of my HVAC system.
Response from LBA Air Conditioning, Heating & Plumbing:
We are so glad that Patrick did such an awesome job on your HVAC Heating maintenance and your humidifier tune-up! Thank you so much for the awesome review; we will be sure to pass along your kind words to Patrick!
Patrick was able to diagnose the problem, fixed it and then taught us how we can correct the issue in the future if it happens again. Thank you!
To wake up on a Cole winter morn with no heat is a downer. I called LBA and within a little over an hour Patrick was at my home fixing the problem. He took pictures inside the furnace to show me the problem and explained the pictures. He was helpful and worked carefully and with knowledge of my problem. I a very grateful he was the tech that came to my home.
Nicholas did a great job. Professional, friendly & knowledgeable. Give that man a raise!
Arrived to do a dual performance maintenance. Used thermostat to control the system. Set system to heating and started inspection with the furnace. Performed combustion analysis to ensure a safe and efficient flame. Tuned the gas valve to bring the combustion gasses into factory specifications. Verified operation of the humidifier. Found that the water panel is heavily coated in calcium buildup and the solenoid valve has a restriction to the flow of water. Verified operation of all mechanical and electronic components. Found that the capacitor for the blower was performing well outside factory specifications. Cleaned and retested the flame sensor. Measured airflow for combustion air. Checked heat exchanger for damage to ensure proper venting of flue gasses. Checked blower wheel for cleanliness and to see if there is any play in the bearings. Measured a temperature rise. Performed an electronic gas leak search. Switched system to cooling. Measured the temperature split between return an
Hyper-cleansed approximately 100’ of sanitary sewer from stack c/o in basement and video inspected. Found clay tile line to be in fair condition, less future root intrusions. Cast found to be in poor condition and recommending replacement, with options being presented for replacement with lining for outside part of sewer. Thank you for choosing LBA for your service provider.
Completed heating tune up today. System kept shutting down due to leaving air temperature sensor. Removed it and let the system ramp up fully. This was due to the higher ambient conditions that the system is running under at this time. Placed temperature sensor back in the ductwork. Performed combustion analysis and everything checked out properly. Replaced air filter with one homeowner provided. No gas leaks detected during my visit today. Cleaned furnace cabinet. Performed humidifier tune up and set humidifier for winter season. Inspected heat exchanger. Has some visible thermal stress but no cracks or holes. System operating as expected at this time. Thank you for choosing LBA services. Your technician today, Jake. View visual findings from this job here - https://visionshare.xoi.io/?id=XA-0D78-CC814DA857A94E5994F9BEDEDAD6D731
Arrived to remedy a system that is not operating properly. Inspected the furnace and confirmed call for cooling and measured a 5 degree temperature split. Inspected the condenser and found that the capacitor and contactor are performing outside factory specifications. Checked the refrigerant levels and found that the system is low on refrigerant. Performed a leak search and found that the evaporator coil is leaking refrigerant. Spoke with homeowner about repair solutions. With homeowners approval installed a new capacitor and contactor, and charged system to factory specifications. Called and ordered the evaporator coil. Will coordinate with the office to arrange a time for installation. Air conditioning system is functioning properly at this time. View visual findings from this job here - https://visionshare.xoi.io/?id=XA-0D78-BAA209E65F6E41E0A48AE80233578BCE
Installed frost proof hose bib in front of house.
Performed furnace maintenance on two systems. On the basement unit the the flame sensor (cleaned), inducer motor, igniter, and blower performed within spec. I replaced the humidifier pad on this unit. The combustion analysis showed a proper burn. On the attic unit the flame sensor was originally performing below spec. I cleaned this, bring it back within tolerance. The Merv 16 air filter is due replacement and the customer will buy her own and replace. The inducer motor, blower, and ignitor were performing as they should. The combustion analysis was within spec as well. Systems running upon departure.
Company arrived Friday, September 16 of 2022. Customer was having issues with their mainline backing up. Upon arrival company had the customer run water main line are specific to the floor drain. Company Truman issue to be the main line and perform the main drain clearing special. Before cabling company inspected the line via Camera and discovered multiple root intrusions, and couldn’t get passed approximately 71’. Company cabled the line the full distance of the machine and back (100’) company reinspected the line via camera and discovered a flowing line but 75% of the root intrusions to still be intruding. Company recommended a hydro jet and will email the estimate for the customer to decide. Thank you for choosing LBA and have a great day.
Ac maintenance. Checked all task. Checked temperature split. Checked air filter left 1in while construction is going on and left Merv 16 for them to change out with when there all done. Checked refrigerant level. Checked duel capacitor. Checked out contractor. Checked out coils and cleaned. Checked electrical wiring and components. Made sure system ran before leaving
2n1 maintenance. Checked all task. Checked indoor unit everything well with range system only 4years old. Recommend replacement of humidifier. Checked outdoor unit everything well within range. No recommendations outside. Cx declined recommendations for the moment. Made sure system ran before leaving.
View visual findings from this job here - https://visionshare.xoi.io/?id=XA-0D78-23B22FDC82C3484C87F9D220BC28C6A3 Completed cooling maintenance today. Customer will replace air filter. All electrical components tested in manufacturers specifications today. Refrigerant charge looks good at this time. With customer approval I performed an extensive coil cleaning to the system. System is operating as expected at this time. Thank you for choosing LBA services. Your technician today, Jake.
Perform a heating maintenance check all operations checked filter checked drain lines checked temperature split checked blower motor checked inducer motor clear inducer port clean flame sensor check igniter check humidifier replaced humidifier pad upon customers request say humidifier to work to check CO levels check for gas leaks system is running within manufacturer specifications thank you for having me out today Alex View visual findings from this job here - https://visionshare.xoi.io/?id=XA-19DB-91909EA8BB11498C8DDAEE15BAF5644A
Company arrived Tuesday, September 13, 2022. The customer was having issues with their bathroom sink not draining. Upon arrival company discovered galvanized piping and informed customer of possible causes. After purchase of the perfect service family membership company attempted a branch line cabling on the customers main level guest bathroom sink. Company cabled until the blockage cleared. Company was unable to reassembled the trap to the galvanized piping due to old threads, company connected the trap to the galvanized piping via fernco and tested for functionality. Company verified with the customer and can conclude a flowing drain at this time. Thank you for choosing LBA and have a great day.
Performed plumbing evaluation. Water heater is new and in excellent condition. Treated basement lave and garbage disposal with Endure. Customer purchased bottle of Endure. Advised to treat drains every 30 days. Advised Studor vent will need to be installed in basement lave when p-trap is replaced.
Checked all operations in the heating mode and inspected furnace filters. Checked all electrical components at the furnace and completed a combustion analysis of both units. Both units are operating within factory specifications. Systems are operating properly at this time. View visual findings from this job here - https://visionshare.xoi.io/?id=XA-19DB-E9E70E15559D421FA0E319C9F5D1420F
Upon arrival I found that the blower motor had failed at this time. This blower motor is a specialized blower motor and due to the cost and concerns of the age of the system customers looking into replacement.