LBA has been our provider for years and continue to demonstrate their excellence in quickly working through any issue and explaining it in detail. Very happy with the service and continuing to use LBA in the future.
Very good technician. Some confusion over $89 fee
Great personality and very knowledgeable
Nick, was great from the time he got to our house until he left. He thoroughly evaluated our unit and clearly indicated what he had found. We would gladly welcomed back any time.
At a routine service it was discovered that my air conditioner had some major problems that could have made it stop completely. Andrew worked late to service it and keep it running and returned the next day to complete the job. He was extremely knowledgeable and professional. A bad situation was turned into a positive experience! Thanks LBA!
Arrived early Saturday afternoon which saved us from paying the after 5:00PM rate. The job was taken care of promptly and professionally.
Friendly, helpful and courteous
We requested a Stevens sump pump but were not told they are not available. Hopefully the Zoeller that was installed will last 7 years like the one he replaced
Cleared drain line on unit above women's restroom water level now dropping.
Estimate to perform electronic leak search on 3 ton split system heat pump. After the leak is located and another quote will be submitted for repairs. 9/20/19--Found the refrigerant leak in the back side of the evaporator. Took a picture of the leak and sent the photo to Michelle by email. Sent the info to Zach for quoting equipment replacement.
Error code 10 on middle tankless unit , reset unit and ran through cycles , tankless is working fine at this time .
Completed heating tune up and humidifier tune up, replaced humidifier panel and replaced merv 13 air filter, everything else tested as it should at this time, thanks for having me out today.
Estimate for toilet with haul off Will do job Monday morning
Checked all operations in the heating mode for both furnaces. Performed combustion analysis on both systems as well as checking carbon and oxygen levels. Cleaned off blower wheels as well as both the furnaces themself. Both furnace filters were good at this time. System is operating within factory specifications at this time. Very nice meeting and talking to you
Checked all operations in the heating mode. Performed a combustion analysis as well as checking oxygen and carbon levels. Cleaned blower wheel as well as the furnace itself, furnace filter needed to be changed and furnace is operating within factory specifications at this time. System showed to not be cooling properly. Upon further inspection of outdoor unit system showed to be low on refrigerant. Spoke with customer over the phone about recharging system back to factory specifications and or setting up appointment with design specialist. Also recommended that system be replaced as well. Customer did not want to do either and said he would charge system himself with his refrigerant. System is now cooling at this time.
Upon arrival customer took me to the basement where main shut off valve was no longer operating.I showed option for replacement Chris chose the bronze with 6 month warranty.I drained house and replaced valve .Then turned water back on checked for leaks and purged air out of lines. Called Pat for est. on gas piping and water softener. Pat will give est.
Estimate for gas line and water softener
Check Apt 210 for no cooling. Found unit cooling with low temperature split. Check refrigerant charge and discovered low suction pressure and high superheat which indicates a low refrigerant charge. Informed Michelle of findings and she opted to recharge system instead of leak search. Charge unit with 5lbs of r22.
Customer stated that the condenser was making a loud noise and the temperature increased 3Â° before they called for emergency services. I arrived and tested cooling operations. I could not duplicate the noise and cooling issue at this time. I checked all electrical connections and refrigerant pressures and temperatures. The system is operating within factory specifications. There is no signs that the system had frozen at any time. The customer does have a nest thermostat and it did not have the common wire attached. I added the common wire to the thermostat and to the furnace control board to eliminate the possible intermittent issue when nest thermostats do not have the fifth wire connected. 85 deg OAT 11.5 subcooling. Required subcooling is 11 Temperature drop across the indoor coil is 21 degrees Amp draw on compressor is 8.0. RLA is 12 Filter is clean Outdoor coil is clean
Estimate for sump pump and pit with backwater valve
Upon arrival found that the main components outdoors were not starting due to a voltage enhancement system failure. After speaking with the customer the customer chose gold option which allowed me to rebuild the outdoor control panel and restore the system back to clean condition. Some damage could have been caused to the main components From this failure but no damage was showing at this time. System is now operating within factory specifications.
Conducted preventative maintenance on RTU systems. Inspected all mechanical and electrical cooling operations. Inspected conditions of all blower wheels and belts. Inspected all motors and capacitors. Cleaned all outdoor coils. All filters have been replaced. All deficiencies have been quoted for repairs.
Performed a full cooling and heating inspection. Washed and cleaned outdoor unit. Checked all wires and safety switches on both units. Checked the performance on the indoor unit. Both units are operating within factory specifications at this time.