Very professional and courteous.
Great service and price.
Rigo is great! Found our problem and took active steps to get it solved.
I appreciate being able to schedule service on Saturday without paying an additional charge, all while receiving outstanding service.
LBA provides outstanding service. Scott McKinley is easy to work with and takes the mystery out of installation. Chris Stewart expertly handled the installation the next day to accommodate an unexpected travel schedule. I truly enjoy working with a company who puts their customers' first. Thank you!
Returned call to customer about emergency service. He asked how much it would cost . I told him 138. Plus task. He declined service at this time.
Purchase Order: 3600136402
Assisted in CPMA Quote for repairs have been emailed
Performed cpma, changed all filters and inspected electrical and mechanical functions. All system
Checked the twin Carrier upflow gas furnaces for no heat after we performed the PM. Found the flue mounted manual reset limit switches tripped on both. Reset the switches and tested both the heat mode. Found both heating normal after resetting with the room temp rising to setpoint and the units cycling off. Warranty
Found gas line to unit heaters cut in attic. Will need to have plumber run new gas line to unit heater.
Performed a full heating inspection. Checked all wires and safety switches. Cleaned indoor unit. Performed test on heating elements. Heating elements are operating properly. Unit is operating within factory specifications at this time.
88.00 Main line special. Ran large machine and came up in hole house trap. Couldnâ€™t clear main . No charge. House trip must be removed to clear main.
Performed cpma on all of the units. Checked all electrical and mechanical functions. Upstairs system is struggling due to age and wear on units. Units are from 1997 and the units downstairs are from 1999 they are also struggling to keep up with the heating. Units are functional at this time however i do reccomend replacement as soon as possible. Theses units are rated to last for 15 years and they are 20 and 22 years old.
Changed out board
Upon arrival water coming from base of water heater. After discussing options with the customer he chose the bronze package water heater replacement with six month warranty. Installed and checked operation and for leaks.
Arrived to find fault in voltage enhancement system. Showed customer options. Customer wanted quote and our design specialist to come out for replacement options. System is not heat at this time.
Limit switch failure and flue where disconnected, customer choice the bronze. Did bronze repair pressure switch was shutting off and on. Customer said he couldnâ€™t pay more at this time
Upon arrival rtu-1 thermostat was blank. After finding which unit it belonged to I jumped power at the thermostat base and the rtu-1 kicked on and ran properly. I replaced the thermostat and tested the unit in heating mode and it is operating properly at this time.
Upon arrival the customers kitchen drain was backing up. I cabled the line from underneath the sink and couldnâ€™t get the clog. So I had to go through the cleanout in the garage where the clog was 5 feet out. I tested with gallons of water and everything tested good.