Patrick was very kind and professional!
Jacob from LBA came out today to do routine maintenance and did a thorough job of checking everything, while answering my questions. Thank you!
Service men showed up on time and they were great. Professional, knowledgeable, respectful and friendly. They did a fantastic job and cleaned up when they were finished.
Will send referrals
Super same day service. I’ve had a contract with LBA for years and they’re reliable, friendly, professional and very knowledgeable.
Friendly and prompt service
Response from LBA Air Conditioning, Heating & Plumbing:
We are incredibly grateful that you took the time out to leave us a 5-Star review.
Really professional and prices are great, they always get me in .
They were very polite and did a good job. Were more interested in satisfying us than trying to sell us more.
Phil, was very professional and knowledgeable. He was friendly and answered all our questions. Great service.
09/24/2022 Change out your water main shut off also rebuild your meter and make some small repairs on the galvanized water line in order to properly connect onto the existing water line. Also change out your upstairs toilet water stop to prevent any further water damages when the water is turned back on. If any other issues arise during or after the repairs are made there will be additional costs added. Company is collecting $934 from the work performed today and collecting the other $935 along with the $8600 whole house repipe estimate on Monday.
Arrived to furnace maintenance. To begin my maintenance I began by performing a safety inspection. Here I found severe rust, pitting, and a cracked heat exchanger. Deeming this unit unsafe to operate. Therefore I could not perform anymore work on this piece of equipment. With a failed heat exchanger and the burners in such poor condition we will have someone out to quote a new system. Furnace locked out upon departure.
Company arrived Tuesday, September 20, 2022. The customer was interested and having their tub waste an overflow replacement do to a slow draining tub. Company observed the customers plumbing in the crawl space and discovered galvanized piping. Company informed the customer the slow drain could be due to the galvanized piping vs the waste and overflow, and gave options for repair. Company wrote estimates for a sewer repair for the cast underneath the house and a branch line repair. The customer was interested in the inside sewer repair and would like to look at financing options before moving forward. Company emailed the estimates to the email on file and the customer can except the estimate through his email. Company collected a 120 trip and diagnostic charge at this time to be applied to the options given. Thank you for choosing LBA and have a great day.
Arrived to diagnose a system that was unable to keep up in the heat yesterday. Performed diagnostic and did not find anything that would be an issue. Spoke with homeowner about an intermittent issue with the condenser fan motor. Mentioned that the coil could use rinsed. Homeowner will handle the condenser rinse. Air conditioning system is functioning properly at this time. View visual findings from this job here - https://visionshare.xoi.io/?id=XA-0D78-7A840B3178DA4E75A295CB31E9791E7B
Returned to clean mini split coil and blower. After cleaning was done everything was operating as it should at this time. Thanks for having me out today, Eli
On arrival customer request to replace drain line I gave her options to have it replaced with vinyl or PVC customer decided to have it replaced with vinyl. Changed out drain line and everything was operating as it should at this time thanks for having me out today, Eli
Checked all operations in the heating and cooling modes and inspected furnace filter. Filter was dirty and replaced with a customer supplied filter. Checked all electrical components and completed a combustion analysis of the furnace. Found that the oxygen levels were very low and the carbon monoxide levels were extremely high. I inspected the heat ensure there wasn’t a crack. Then upon adjusting the gas valve pressure we were able to get those numbers back within factory specifications. Checked all electrical and refrigerant components at the outdoor unit. Everything at the outdoor unit was looking good today. System is operating properly at this time.
Completed heating maintenance today. Temperature rise was in range for both stages of heating. Performed combustion analysis and levels were normal. Inspected heat exchanger and there is normal wear from the age of the furnace but no visible cracks or holes. All electrical components tested in manufacturers specifications today. Cleaned flame sensor and blew out drain lines. Replaced humidifier pad and set humidifier up for winter after ensuring proper operation. System operating as expected at this time. Thank you for choosing LBA services. Your technician today, Jake. View visual findings from this job here - https://visionshare.xoi.io/?id=XA-19DB-E1D248A3E45347C383DE3407C989EE13
Company came out for estimate work to install two new outside hose bibs frost free. Company shut water off to home and installed new bib under kitchen faucet connected to cold side tested no leaks. Company installed new hose bib out of back side of home connections made in basement tested no leaks. Company will return to install anode rod once shipped to warehouse.
Furnace tune up. Checked all task. System 15+. Checked SA RA. Checked inducer motor. Checked flame sensor and cleaned. Checked igniter. Checked heat exchanger very rusted and hot spots. Checked blower and it’s capacitor are okay. Recommended humidifier service. Made sure system ran before leaving. View visual findings from this job here - https://visionshare.xoi.io/?id=XA-19DB-7212687CC81044C2819E8343DA947342
Checked all operations in the heating mode and inspected furnace filters. Both filters were dirty and replaced with customer supplied filters. Checked all electrical components at the furnaces and completed a combustion analysis of both units. Both units were operating within factory specifications. Systems are operating properly at this time. View visual findings from this job here - https://visionshare.xoi.io/?id=XA-E865-94615F5350874025B740CD229656712F
Arrived to AC maintenance. Upon arrival I had the thermostat call for cooling and made my way to the indoor unit. Here I replaced the air filter with truck stock, checked for proper temp split/blower operation, and flushed the condensation drain. On the outdoor unit the compressor and fan were drawing correct amperage. The refrigerant temps/pressures showed a properly charged unit. The outdoor coil had started to build up debris throughout. I removed all panels from the outdoor unit and cleaned the coil with water. Customer signed up for our membership program and we will continue to schedule maintenances in the future. AC running upon departure.
Checked all operations in the cooling mode and inspected furnace filter. Furnace filter was dirty and replaced with a customer supplied filter. Checked all electrical and refrigerant components at the outdoor unit. Found that the unit has a failed capacitor. System is twenty years old and uses R-22 which is no longer manufactured. Customer is holding off on repairs and is going to look into replacement next season. System is operating properly properly at this time. Today we also rewed View visual findings from this job here - https://visionshare.xoi.io/?id=XA-178F-E9C62BF021A648898B7CF74EDFF479E0
Company came out for faucet replacement in kitchen. Customer supplied faucet install company removed existing faucet from water and sink and installed new delta stainless faucet. Company provided 2 year labor warranty on work performed today. Thank you Carol for choosing LBA and have a wonderful day!!!
Arrived to do performance maintenance. Turned on the air conditioning system at the thermostat. Started inspection with the furnace. Measured power consumption and measured the temperature split. Flushed condensation drain line. Checked blower to see if there is any play in the bearings. Checked system air filter and replaced it with homeowners supplied filter. Moved inspection outside and checked the coil for cleanliness and excessive vibration. Found that the condenser coil was heavily coated in dust and debris. Measured power consumption of the compressor and condenser fan motors. Verified operation of all mechanical and electronic components. Found that the capacitor for the compressor motor was performing outside factory specifications. Verified system refrigerant charge. With homeowners approval performed an extensive coil cleaning and installed a new capacitor. Air conditioning system is functioning properly at this time. View visual findings from this job here - https://vision