Tech was able to enter home through rear basement door with COVID restrictions, plus, with my health I have difficulty with the steps and I'm on O². I did briefly talk to him in the basement, but, I had to return back upstairs. My thanks to "David" and the LBA Team for coming out. Will continue with their service.
I am not sure if my hot water heater was completely flushed.
Very easy to work with.
To be honest, the price was to say the least absolutely high! For the amount of time and materials, including what I would provide, the labor cost seems outrageous.
At time of arrival found furnace with the error code 55 stating pressure switch open, as I was about to start troubleshooting I touched the wire and system started to run and heat up as normal. Went ahead and cycled the system multiple times and system kicked on and cycled as should.
At time of arrival found exhaust piping for the furnace clogged up with some debris and causing a restriction and not allowing exhaust fumes to vent. Hi presented options to repair the exhaust piping from the outside of home to the furnace, but customer stated his son can take care of it for them in the morning. No other work performed at this time
88 dollar furnace inspection. Performed combustion analysis, cleaned furnace, replaced filter, checked temperature across furnace, tested humidifier, checked furnace components for reliability. Performed safety inspection and gas leak check. No concerns with furnace reliability or safety at this time. Water heater shows signs of previous exhaust drafting issues (Plastic rings around draft hood on top of water heater are melted). I checked the draft on the water heater and found at this time it is drafting properly.
Upon arrival disposal was leaking from casing, and the kitchen faucet was not properly set. The lavatory faucet was loose at counter. Replaced disposal with like model disposal. Checked for leaks and proper function. Reset kitchen faucet. Reset lavatory faucet.
Performed full heating preventative maintenance one two rooftop units and four twinned split systems. Checked all electrical and mechanical components, changed all filters. All but one of the split systems are operational one split has a bad ignition board and one has an inducer motor with bearings going out. A quote has been sent via email to the customer.
Assisted with heating PM.
Viewed faucets to be replaced. Gathered information for estimate to replace 3 lavatory faucets and 2bar sink faucets.
Performed Tasking on RTUS and Split System , change out filters inspected heat exchanger for cracks change electrical wiring for loose connection recorded motor amps, checked operation of heating mode, everything checked out ok no problems to report at this time
Upon arrival water was coming out on floor at men and womenâ€™s public bathroom. Menâ€™s side tank to bowl gasket was leaking.And handle is broken. Replaced take the bow gasket and handle checked operation no more leaks.
Upon arrival I found that the gas line was cut going to the furnace through the wall. I gave customer estimate on having gas lime ran but they excepted another quote from a different company at this time.
Estimate for water repair. Strongly recommend exact leak is located by underground leak detection company.
Upon arrival found that the system is extremely dirty and in pretty poor shape. Found the immediate issue was the flame safety system. Found that the air movement system has a bad capacitor and the system is in desperate need of extensive cleaning as well as needs an air movement system cleaning. Would recommend replacement over repairs. Customer was unable to make all these repairs at this time and was not approved for financing. Repaired flames safety and vacuumed out furnace cabinet. Replaced furnace filter. Furnace is heating at this time.
Upon arrival the customer floor drain was backing up. Customer said he plunged the floor drain and put liquid drano down the floor drain. I had to cable the line through the cleanout in the floor drain and my cable started to come back out at me. I began to run the laundry and the water never backed up. I explained to the the customer that the laundry line should be draining into the floor drain and recommend a tech specialist come out to give a bid on a new floor drain. Customer declined at this time. There is no warranty on work that was done today.
Upon my arrival customer had unit turn off at the disconnect, unit back on to troubleshoot the call for no heat, unit cycle on everything seem to be working but supply fan is not coming on , I found loose connection on terminal board slot number 10, tightened wire than checked operation of heating mode everything is working ok Work was donâ€™t on REZNOR model# RPB-400. Serial# BSA3062009020
Estimate for water heater. Homeowner has no email