Jose was very nice to deal with and very explanatory on what he was doing as he was doing it and if he Was questioning a situation he did not hesitate to call up on one of his coworkers who helped him out. LBJ is lucky to have a young individual like Jose.
Expertly done and nice.
Guys did a nice job
10/24/2020 10:14:02 AM - Option 1 <a clicktracking="off" href="https://partsgatorstorage.blob.core.windows.net/proposals/10242020 31801 PM - 1 - 4-102420101402-Travis French-Proposal-Copy.pdf?sv=2014-02-14&sr=b&sig=jQ0oSXGAbHO4vYjUlLkrUzSX2MKBb7VVeadInf%2FPMnw%3D&st=2020-10-24T21%3A42%3A28Z&se=2520-10-24T21%3A47%3A28Z&sp=rw" target="_blank">View PDF</a>
Installed 3 new filter. Nothing further at this time.
Install new 40 gallon gas hot water heater with all code upgrades and haul old unit off for disposal. Installing new Rudd 40 gallon gas with 8 yr warranty. Also had to clear drain in basement, at no additional charge. Would not drain.
Checked the boiler for no heat. Found the boiler on and heating normal. Manager informed me that the boiler was shut down by the inspector during a recent inspection. The manager restored power to the boiler himself. Verified operation of the boiler and tested all of the safeties. Added water to the system to the proper pressure of 10-12 psi. Checked the expansion tank water level for proper cushion. Checked the pilot flame signal at the flame safeguard. Checked the blower belts and operation of the air handlers with the hot water coils. System is running normal at this time.
Upon arrival the only garbage disposal that was a badger 5 was clogged. I tested the disposal by pushing the button underneath the disposal and turning it with a key. After that I turned the disposal on at the switch and the disposal started to drain. I ran lots of water and the drain never backed up. Everything tested good.
Upon arrival customer took me to his fireplace. He had called in saying that he was needing work on his insert. He turned on the switch and the pilot light came on and the fireplace lit up I removed great and inspected piping. Nothing out of the ordinary except for it was dirty. Customer said that sometimes it goes out. And I explained we just deal with the piping to the insert not the internal parts of the inserts. He said that the office said that we worked on inserts. I explained that we donâ€™t work on the internal parts of an insert. And that there would be an $89 service fee. Customer said that they shouldâ€™ve been explained to him that we donâ€™t work on the insert before sending us. And he did not feel that the $89 service fee was a fair charge. I waved service fee And apologized for the inconvenience and misunderstanding.
Cause of issue was that there was no pressure in the boiler. After letting some water in from the pressure reducing valve discovered that it was leaking from the air separating valve. Tightened valve and boiler pressure was back up and heating all the zones. Recommend and getting maintenance done and airing up expansion tank. Tune up quote will be on invoice. Thank you
Performed full heating preventative maintenance on one rooftop unit checked all electrical and mechanical components, changed all filters.
Checked the Lennox unit heater for the warehouse for no heat. Found a inline fuse in the 120 volt supply curcuit to the unit with a loose connection at the fuse holder. Removed the fuse from the curcuit. Started the unit and verified operation. The fuse is not needed as the unit is protcted by the breaker panel. Lba installed the unit 12/14/17. The unit has not been serviced since the install. Warranty.
Performed full heating preventative maintenance on two unit heaters, retrieved forgotten tools
Checked downstairs toilet which is slow flushing. Ran water in sink and flushed toilet multiple times. No back up could be seen in floor drain or main stack. Issue is in or near toilet. Gave option for resetting toilet so that further inspection could be done. Work declined at this time.
Met Bob on site to look at the truck wash bay tube heaters that the flues are rusted out on. Took pictures and sent the details to Brett for scheduling time and material repairs.
Performed full heating preventative maintenance on 2 unit heaters and one furnace. Checked all electrical and mechanical components changed one filter.
Performed heating tuneup on furnace. After completing tune found fuel delivery system was still releasing gas after system satisfied and completed heating cycle, after addressing this concern with customer he decided to proceeded with repair. Installed new fuel delivery system and system is running within manufacturers specs at this time.
Upon arrival drain assembly on wall hung lav was broken and leaking. Drain could not be repaired due to the condition of the sinks bracing. To properly repair sink it would need to be removed from the wall and properly braced to the wall. This would require cutting into sheet rock and installing wood bracing behind the wall. Estimates submitted.