Izzy was prompt, very courteous and took care of my furnace problem right away. I will definitely call LBA again for my Plumbing and HVAC needs.
Rick was very professional knowledgeable and great to work with!! Quick service fixed the issue at a very fair price!!
Phil was Very professional and very cordial. He explained what needed to be done to perform the job. In my opinion I would recommend LBA and Phil.
Very professional and courteous.
Upon arrival the customer water heater in the womenâ€™s bathroom in the ceiling was heavily corroded and leak. There werenâ€™t getting any hot water from it as well. I quoted them a new 30 gallon electric water heater with a complete code upgrade that will take 2 people to install. Also in the workshop there is a bathroom in the back of the building thatâ€™s not getting any hot water at all as well. The 50 gallon gas water heater is 14 years old and needs to be replaced. We can replace it with a complete code upgrade that comes with a protection pan and a expansion tank. This will be a 2 man job to install as well. Both jobs will be time and materials.
Upon arrival found board and blower motor to not be engaging when being called. Causing the safety switches to cut circulation to furnace due to overheating. Gave customer options as far as repair, Customer wants an estimate on a new furnace rather then go with repair Scott will be out tomorrow
Upon arrival found combustion motor to no longer be operating. Manufacturer was no longer open nor available for pricing. Based on age of the unit Scott will be coming out to give an estimate on the furnace today. I will be following back up with customers tomorrow.
Changed customers setting on fan motor to high, supply Line to small for mid low setting when on heating. Changed it to high when trying to be above 72Â°. System did not shut down at any time after testing. Customer wants to get on the P3 maintenance plan but wants to call in and talk to Angel for setting it up.
Helped with repair
I assisted with the install.
Upon arrival I found an alarm code for low air flow. I checked and found the contactor for the supply air blower to have been tripped due to a spike in amperage. I also found the pre filters to be very dirty, so I replaced them. After resetting the contactor and replacing the air filters I never saw a spike in amperage on that contactor the unit is operating at signed at this time.
Amazon is going to repair water hammer problem before addressing hangers. Cannot give a bid due to time restraints when work can be done. I will talk to Mike with Glab about job
Upon arrival the customers main line was backing up into the floor drain in the house. I had to cable the main line stack in the garage of the house. I took my cable all the way out and ran water in the laundry room. Everything tested good.
Customer water heater wasnâ€™t working properly. Told the customer it could be the flame sensor or it need to be cleaned. Presented pricing to the customer and the didnâ€™t want to pay overtime pricing on repairs. Collecting trip charge.
Arrived to find system heating but not properly. Found the system to be extremely dirty. Showed customer options. Customer wanted the bandaid option. Performed all work under the bandaid option. Unit is heating properly at this time.
Performed the safety inspection On air handler, All safety switches are corresponding correctly to specifications. Heat strips are rated to be running at 24 Heat strips are running at 16 A checks out great. Performed an indoor blower test, Indoor blower motor is working to specification. Performed an electrical analysis 240 V going to furnace stable and secure a furnace and receiving adequate electricity. Changed out filter completely cleaned all surfaces and inside air handler. Drains are drains properly. Recommended humidifier, customer has no need for one.
Observed noises from makeup air units 2 & 3 were due to cupping of the drive pulleys. The dual drive pulley on the motor wears over time and due to cupping the belts do not sit straight in the pulleys. Due to the new angle of the belts, they self correct their orientation on the blower pulley creating a popping noise. New blower drive pulleys and belts were recommended on all units. This is for the replacement of one dual drive pulley (1 5/8" X 7") and two BX65 belts on each of six makeup air units. Pulleys will be replaced and properly aligned, belts replaced and tension set per manufacturers recommendation. Finally, all units will be tested for proper operation.
i Performed the quoted repair. I replaced the ax-38 belt and adjusted the tension.