Matthew was our technician. He called to let us know when he would be here and was on time. He was friendly and very knowledgeable and professional. We will request him again (if need be) and recommend him to anyone needing services.
Very professional and personable employees. We always use LBA because their techs are so knowledgeable and friendly. The office personnel is very efficient and professional as well. We have complete confidence in this company.
As always, the company is top notch, starting with the office staff and dealing with the service people. I had Nick yesterday, very helpful and professional. Today I had Drew to assist me - LBA is so very lucky to have him - professional, courteous and very caring.
On time , clean , polite
The tech did call me to get my approval for service on the humidifier. The tech was courteous and professional, as always.
Customer kitchen drain was backing up. I cabled the line and ran gallons of water down. Everything tested good. Customer also wanted to renewal there p3
Apon arrival I found that the voltage enhancement system had failed, called customer and he decided to go with bandaid option, I completed a cooling tune up and unit tested as should at this time, thanks for having me out today, Eli
I found the system low n refrigerant and preformed a bronze level repair. Ambient temperature 85 Inside dry bulb 79 Inside wet bulb temperature 68 Suction gauge temp 51 Suction line temp 67 Super heat 16 Discharge gauge 99 Discharge line temp 96 Sub cool 3. We discussed replacing the coil if the leak sealer doesnâ€™t work.
Arrived onsite to inspect 20 split systems that provide for a wing that is getting remodeled. I found that all the furnaces were from 1990 and are 29 years old there were many furnaces that were found with a failed heat exchanger. With the heat exchanger failed it runs the potential to let carbon monoxide into the air stream which is an extreme safety risk due to this safety risk all the furnace that were found like this were red tagged and disabled on heating. The heat exchanger is a major component of the furnace and is not replace able and will require the unit to be changed out to gain proper heating back to these rooms. I will notate the issues found below bye room number. #507 This unit was found with a low temperature split on cooling reading a 12Â° split out of the recommended 18-20Â°. It appears that this unit is low on charge but we will need to attach our guages to the unit and check the pressures to determine this is the issues and then we can determine if we will need to
Perfromed full cooling inspectuon. Replace air filters, wash condenser coils, test electrical compontes, inspect wiring, and cooling operation.
We performed the full cooling pma. We washed all the condensors and changed all the filters checked blowers, contactors, capacitors, amp draws, and temp splits. All the units are operating properly at this time.
Air conditioning maintenance
Ruud summer air conditioner tune up
Performed a furnace safety and performance inspection on a Lennox furnace. Also performed a tune up on a Lennox air conditioner
Spring check before summer preventative maintenance
Air conditioner is stuck on
Installing backflow prevention device on water driven backup sump pump as required by code also install bonding grounds to csst gas pipe system to bring gas line up to code, replacing t&p valve on water heater thank you so much, Rich