Steve is an awesome guy to work with.
Steve is great guy to work with.
Estimate for water heater replacement. Discussed pros and cons of tank water heater vs tankless water heater. Homeowner is opting for an electric tank water heater.
Seasonal A/C tune-up and HVAC safety check. Calibrated thermostat and adjusted dampers. Everything else looks good. A/C system is ready for summer.
Air conditioning maintenance for a residential homeowner. Inspected unit for cooling. Found no issues. Customer declined new filter.
7-18-22 Tue Bindery area duct heater not working. Spoke to Billy on site and used their scissor lift. Found newer duct heater draft safety switch was tripped. Manually reset the safety. Start the furnace and check draft. While on site, pulled and cleaned the pilot assembly and the flame sensor. Unit is working properly. Due to the location of this building they have issues with Highwinds, may have caused the limit the trip. There is an older unit next to this one that is completely disabled.
7-21-21 Replace belts on the 2 package unit on the ground The Lennox unit, had to realign the belt and check tension, Go bells for supplies. Billy and I did a walk-through the office attic area Visual on one horizontal furnace, we may have some issues. The main air handler above the menâ€™s bedroom filters need to be replaced would give them better airflow. Checked exhaust fans on the press both are working evenly.
7-1-21 Hose-out the production area Trane package unit, Billy and I remove the top panel with the condenser fan motors and expose the condenser coil. This coil is solid until he gets to the last 3 feet and then it splits out to three different sections. We use coil cleaner,supplied by the customer. Using the garden hose we clean the condenser it took approximately six passes to get the Cottonwood out of the coil. We also use evaporator coil cleaner on the evaporator coil and hosed out the evaporator coil This package unit is on the ground with side return and supply, so we were able to hose out the evaporator without making a big mess. Reinstalled all the panels that we removed. Started the AC system unit is working at this time
6-24-21 Air conditioning for the main printing area itâ€™s not keeping up found unit has clogged filters. also we need to hose out the condenser coil Iâ€™m gonna do this next week