First checkup on 1 year old systems. This guy took the time to be sure everything was right. LBA has impressed me from day 1.
Performed two full heating inspections. Checked all safety switches. Cleaned indoor unit. Checked all components in the heating mode. Unit is operating within factory specifications at this time.
Completed cooling tune up, replaced merv 16 air filter, everything else tested as it should
Performed two full cooling inspections. Washed and cleaned outdoor units. Found older system to be low on Refrigerant. Showed customer options customer chose bronze option. Performed all work under the bronze option. Also checked all wires and safety switches. Systems are now operating within factory specifications at this time.
Upon arrival found that the air conditioner for the main floor system that hadnâ€™t been replaced had a clog the drain due to crickets getting stuck in the drain. Replaced furnace filter with Merv 13 furnace filter and replaced other systems 1 inch filter with customer supplied filter. equipment is operating properly at this time. Informed the customer to call back Monday to schedule maintenance.
Furnace inspections on two Trane furnaces.
A/C tune up. Completing a full preventive maintenance cooling check on two Trane air conditioning units.
A/C tune up service. Found the Lennox air conditioning unit to be operating properly.
Performed a furnace tune up on a Goodman system
Warranty repair. Set up thermostats.
Conducted a full furnace tune up on a tempstar unit.
Conducted a full a/c tune up on a 17 year old Ducane in Olathe KS 66062.
Found a 15year old Trane a/c to be low on refrigerant.
Inspection of two full HVAC systems, water heater& softener.