Always courteous, reliable technicians, great communication from the company letting you know when they will arrive etc.
First checkup on 1 year old systems. This guy took the time to be sure everything was right. LBA has impressed me from day 1.
arrived to find one of the fittings on the 2â€ concentric kit was dripping. It was glued. I was able to cut the 2â€ pipe and remove the fitting, I then cleaned the fitting off and re did the primer and glue. After that correction we let the furnace run for a good hour and checked again, there were no leaks at that time. I then discovered a leak on a 3â€ pvc 90. I was able to cut it out and replace a small section of pipe. At this time I have all leaks.
Adjusted the flue pipes properly, Water leaks issues have been repaired. There is No more problems with the system.
Today I completed your annual heating tune up on both units, I checked all safety and electrical devices to ensure your system is running safely and efficiently, I cleaned system and performed combustion analysis, checked for proper heating transfer, performed humidifier tune up on main system. everything tested as it should at this time, thanks for choosing Lba, Eli
Thank you for allowing me to service your HVAC equipment today. Performed a maintenance and safety inspection on both furnaces. Inspected all electrical connections to ensure they are secure and not rubbing. Performed a combustion analysis on both heat exchangers and found zero issues. Humidifiers are on and draining properly. The MERV 11 are changed on an annual basis in the Spring. Spoke to the customer about the iWave-R and its benefits. Enrolled customer in our P3 Maintenance Program. Systems is running safely and within manufacturers specifications at this time.
Performed two full cooling inspections. Checked all wires and safety switches. Cleaned both outdoor units. Unit is operating within factory specifications at this time.
Arrived to find system not operating due to roof cap being broken. Cut intake pipe and caped it on both systems. Performed test in the heating mood to ensure system is operating properly. Tested for co in the house. Did not find any. Unit is heating at this time.
Performed two full heating inspections. Checked all safety switches. Cleaned indoor unit. Checked all components in the heating mode. Unit is operating within factory specifications at this time.
Completed cooling tune up, replaced merv 16 air filter, everything else tested as it should
Performed two full cooling inspections. Washed and cleaned outdoor units. Found older system to be low on Refrigerant. Showed customer options customer chose bronze option. Performed all work under the bronze option. Also checked all wires and safety switches. Systems are now operating within factory specifications at this time.
Upon arrival found that the air conditioner for the main floor system that hadnâ€™t been replaced had a clog the drain due to crickets getting stuck in the drain. Replaced furnace filter with Merv 13 furnace filter and replaced other systems 1 inch filter with customer supplied filter. equipment is operating properly at this time. Informed the customer to call back Monday to schedule maintenance.
Furnace inspections on two Trane furnaces.
A/C tune up. Completing a full preventive maintenance cooling check on two Trane air conditioning units.
A/C tune up service. Found the Lennox air conditioning unit to be operating properly.
Performed a furnace tune up on a Goodman system