Jesse did my annual furnace tuneup yesterday. He came early in the 4-hour appointment window, and was finished in well under an hour. In four years I've never had any trouble with the furnace or air conditioner they installed, and this year he even said my filters didn't need to be changed. The technicians always clean up afterward, and scheduling service is easy. Highly recommend!
LBA first saved my chilly butt three years ago when my furnace went out. In January, of course. 24 hours later, I had a new system that's saving me lots on utilities. Five months later they replaced my entire sewer line in 3 days with a lifetime guarantee against tree roots. Since then, they've only had to come out for scheduled maintenance and filter changes, but every time, the technician is on time, courteous, and professional. LBA may be a little pricier than some companies, but I think you get what you pay for.
I arrived to find that the boiler pressure was at 30 psi in the pressure relief valve was dripping. I relieved the pressure and turn the boiler on. With the boiler heating, the system was reaching 30 psi of operating pressure and the pressure relief valve was opening. I suspect that there is an issue with the expansion tank not absorbing the The water pressure as it heats and expands. The house is being sold as is and the customer will need to think about the repairs that need to be made. I quoted $1400 to abandon the steel expansion tank and install and bladder type expansion tank with an air separator. I also quoted $625 to drain the system so I can further diagnose why the water is not getting to The steel type expansion tank.
Arrive to find a faults in the exhaust removal system. Left quote for repairs. Customer is thanking about the repairs or replacement of the system. Will take $89 off of repair if repairs are done by next Friday April 19th 2019. Unit is running but not operating properly at this time.
Replaced outside hydrant
Replace two outside hydrants
Replace voltage Absorption system in carrier system
Water heater not heating. Found and repaired damaged wiring.
Spring preventive maintenance cooling system tune up on a Lennox XC17 air conditioner in Avondale.
Bathroom drain clogged had to auger line
Kitchen drain repipe.
Planned maintenance furnace tune up on a Lennox G61 heating system.
Air conditioning maintenance on Bryant system
A/C tune up service. Full preventive maintenance cooling check on a Lennox air conditioning unit.