Got someone to come out the same day I called. I know this isn’t always possible but it sure was nice. The technician was very friendly and was able to fix things to my satisfaction. I’ve been doing business with LBA for a couple years now and I’m always pleased.
Michael was here at the earliest part of the time window and got my air conditioner serviced quickly so I could get on with my day. He practiced all the COVID precautions and was very friendly.
I would like for the same technician to come back.... Thanks!!!!
Jesse did my annual furnace tuneup yesterday. He came early in the 4-hour appointment window, and was finished in well under an hour. In four years I've never had any trouble with the furnace or air conditioner they installed, and this year he even said my filters didn't need to be changed. The technicians always clean up afterward, and scheduling service is easy. Highly recommend!
LBA first saved my chilly butt three years ago when my furnace went out. In January, of course. 24 hours later, I had a new system that's saving me lots on utilities. Five months later they replaced my entire sewer line in 3 days with a lifetime guarantee against tree roots. Since then, they've only had to come out for scheduled maintenance and filter changes, but every time, the technician is on time, courteous, and professional. LBA may be a little pricier than some companies, but I think you get what you pay for.
Performed full heating preventative maintenance on 3 unit heaters and 1 RTU checked all electrical and mechanical components changed all filters . A quote was sent via email to replace a capacitor. All units are operational at this time.
Assisted with heating PM
Performed PM on AHU, inspected heat exchanger, recorded motors amps, checked all safety change out filters checked operation and heating mode
Assisted in Completing heating maintenance checks and changing filters. All units are operating properly at this time.
Talked to Mike about the issues heâ€™s having with system. He showed me a video of the outdoor unit making a lot of noise around 10am this morning. When we ran it, we could not re create issue. Was most likely cause by the rain and freezing rain this morning. We also set the thermostat to let he heat pump run for 15 minutes before the auxiliary electric heaters come on, because they were coming on right away. Everything is working as it should be.
Customers had multiple issues main reason for being called out was slow drain in lavatory sink for female restroom in upstairs office area. Company went ahead took apart p traps and ran 100 machine through drain and was able to open up blockage found orby beads in line itself and informed customer also informed customer about transitions for drains and to be careful putting things down drain itself. After putting everything back together company can confirm line is open and flowing at this time. Company also conducted a task of replacement of garbage disposal in kitchen area after installing new garbage disposal tested everything for operation everything is testing OK at this time.
Performed heating tuneup on furnace. Replaced air filter. Inspected all electrical components and electrical wires. Inspected heat exchanger did not find any cracks at this time. Found gas leak above furnace shutoff repaired using bandaid repair. Performed combustion check on heat exchanger. System is running within manufacturers specs at this time. Left with furnace running.
We arrived on site and notified the customer that we were here to change out the ignition board on Lennox rtu # 4 model # KGA120S4BH3Y serial # 5613K04858 we replaced the board the unit fired up and we verified operations unit was operating within factory specifications.
Assisted with full heating PM
Performed full heating preventative maintenance on five rooftop units, checked all electrical and mechanical components, changed all filters
Found condensate pump unplug, so I plugged pump back into operation and poured about 5 gallons of water into condensate pump found no problems there, remove panels and checked evaporator drain pan for any kind of debris pan looks clean at this time, blew out all condensate drain line, ran unit in heat mode for about 15 minutes maybe during the cooling season debris could have formed and caused am issue at the time but everything is working ok donâ€™t see any water buildup All work was perfect on Lennox#1 model-G26Q4/5-100-6 serial-5899A06822
Nobody by that name here. Maintenance done by property management company
Checked air filter, took heat rise, performed combustion analysis for oxygen levels in fluegas, CO levels in Flu gas, and flu gas temperature, clean the flame sensor, pulled and clean the burners, Polled and clean the blower motor, inspected heat exchangerâ€™s. Furnace is working properly at this time.
Spoke with Ron, I have sent over quote to replace heat exchanger. I have completed commercial replacement form and sent over information and pictures of site to LBA estimated for quote for replacement. Carrier 2007G10316
Performed full heating preventative maintenance, checked all electrical and mechanical components, changed all filters