Pat M was very good and fair.
Great service! Rigo Medina walked me through the maintenance steps and explained what was being checked and why. He listened to my questions and answered them in a professional manner. Love the fact that, before the appointment, an e-mail with a picture and a short biography of the service technician is being sent out.
I'm a very particular person when it comes to doing things right...these guys nail it every time.
Eric is knowledgeable and was very helpful.
Found two (10uF) run capacitors out of tolerance, and will need to be replaced for condensing unit #3, and airhandler unit # 4. Rtu #4 will need to be diagnosed for a short in the electrical controls. Replaced run capacitors for airhandler unit #4, and condenser unit #3. Diagnosed RTU# 3. Performed electrical resistance test on the compressor and proved the motor has been shorted to ground causing the compressor to fail. All repairs have been quoted. Diagnosed RTU#4. Electrical resistance test has proved both compressors are shorted to ground and have failed. All repairs have been quoted. Due to cost of repairs and the age of the existing equipment, would recommend to replace both units. Units are eleven years old, and the average lifespan of well maintained equipment is fifteen years. Data for both failed units has been recorded for equipment replacement options.
I found the system shut off due a failure in the voltage enhancement system and the system is very dirty. I preformed a bandaid level repair.
Conducted preventative maintenance on seventeen cooling systems. Inspected all electrical and mechanical cooling functions. All motors and capacitors have been tested for correct electrical tolerances. All blower wheels have been checked for correct airflow and rotation. Cleaned all outdoor condensing colis. All condensate drains have been flushed. All filters have been changed. Inspected evaporator coil return and supply air temperature differences for the correct charge on units. All deficiencies have been quoted for repairs.
Replaced old water heater 40 gallon gas water heater. Tested with water and everything tested good.
Water heater relit
Replaced laundry box
I performed the furnace tune up on a Lennox furnace
Multiple issues on day and night equipment
Bryant air conditioning unit not running. Found and replaced a failed capacitor.
Laundry line clog
Opening clogged drain
Replace high pressure and low pressure for furnace.
Men's urinal repair