Steve is the Man. Hard to believe someone this good doesn't work for Amazon or the pentagon. Nothing he can't fix. Might put him on our payroll.
Response from LBA Air Conditioning, Heating & Plumbing:
Thank you so much for the kind words. We will be sure to share your praises with Steve! Thank you again for the awesome review!
We would survive with out Steve
Steve Rayburn!!! BOOM
Once again Steve came in from KC and was on the job before 7:30 He was ready to go and had the old ice machine out and a new machine up and running with in 4.5 hours and just as he was packing up his tools up when our reaching in freezer stopped working He jumped in and got it running and had parts ordered before he left
Steve was on the job and was working at 7:35 He doesn’t waste any time standing around talking other then to ask a few questions and never seems to take a break And he is always on time coming from the KC area to Lawrence he’s always within 5 minutes of the appointment time just amazing
Ask for Steve. He’s the best in kc
Steve came in on a Sunday at 7 am to make a hour drive to Lawrence to service a non working wall in freezer The freezer was full of product and Steve was able to get the walk in up and running in less then an hour and then went home and researched the codes that where displayed and reached out to us to visit about what he had found He was terrific
We changed companies so we could keep working with Steve
We would not be up and running with out Steve R LBA has a fantastic employee in him
We have had other service co and by far Steve R has them all beat A pleasure to work with Nothing he can’t fix ❗️
We always get great service and don’t look anywhere else for service
Michael came, did his work and left. Answered my questions. Was polite and professional.
AC repair - Found transformer blown. Contactor found to be the issue. Thermostat was not functioning and was replaced.
$89 Drain Cleaning Special - Main Sewer Line Cleanout. Cleared the clog and gave homeowner tips on avoiding clogs like that in the future.
Air Conditioning Maintenance for a residential client. Found unit to not be cooling to standard. Checked refrigerant and found it to be low indicating a leak. Homeowner approved filling with 1lb 9.0z 410a refrigerant and dye pack. Scheduled dye check.
Performed and completed a full heating maintenance today at West Lawrence Dentistry on (1) Trane RTU. Removed old filters in the rtu and replaced them with brand new filters. Inspected the heat exchangers, no issues found. Cleaned and checked flame sensor. Checked capacitors, inducer amperage draw, and blower amperage draw. Inspected blower wheels, blower bearings, blower belts, and the blower motor. Inspected electrical connections, no issues found. Verified temperature rise between the supply and return duct. The rtu is heating properly at this time and operational.
12-23-21 At the Supply house trying to get parts breakdown of the parts needed to rebuild the front of the four-drawer cooler. Located some but not all. Leave this ticket as a project
12-23-21 True 4 drawer cooler is not working. On 12-17-21 Made refrigeration repairs to the unit. Today I did find the evaporator has accumulated some ice. Due to the thermostat not shutting the unit down. I repaired some wiring to the thermostat works properly. I also added about 2 ounces of R134a refrigerant to the system to maintain a 20Â° evaporator. Also added some form tape to the drawer ceiling plate. Still working on parts to seal the doors are properly. Also installed a new outlet in the wall supplied by customer.
12-16-21 Under the grill 4 draw cooler Removed existing evaporator and condenser unit, Installed new condenser unit, evaporator, liquid line dryer and capillary tube. System is currently under a pressure test . Iâ€™ll be back in the morning to check and charge system. While on site took a look at the beer tap refrigerant system. Found the condenser coil dirty and also the condenser fan motor not working properly. I will pick up a motor and return and install tomorrow.
12-15-21 Picked up and confirmed material theTrue 4 draw cooler
12-7-21 Wrote a proposal to make repairs To the under the grill cool and e-mailed to James
12-7-21 no trip time started at my house True 4 drawer under the grill cooler check out. Unit is still not maintaining temperature, this does he have issues with the door seals, That we know about. 11-29-21 I serviced the unit and also it is a refrigerant. Today I did a full electronic leak search, still not finding any leaks. Today I remove the evaporator cover found the evaporator was iced over. With the evaporate exposed. I did another leak search, not finding any leaks. I cleaned up the evaporator area and evaporator fan blades. Reinstalled all the covers and doors start the system. Pressures look good, however, we are going to give a quote to replace the condenser unit, evaporator coil, and the capillary metering tube. Itâ€™s understood the unit should be replaced. however, To get a new unit, take months to get. Thatâ€™s why weâ€™re going to propose this repair. Once I get the information from the supply house I will write up a quote.
11-29-21 mon. My time started it at my house so no trip charge. Under the grill, 4 door cooler. It is not working, Found the condenser and the condenser fan motor blades very dirty Pull the condenser unit clean the fan blades and the condenser coil. There is a heavy heavy concentration of cooking grease debris all around this unit. Reinstalled the condenser unit, and tested the operation. Decided to put my gauges on, system is running either with a restriction or a little low on Freon. Recover the refrigerant, vacuum the system and reinstall R134A,per the manufacturers. 8 ounces System was low on refrigerant I did not do a leak search due to the condition of this unit. They will be replacing this unit,probably in January or February. If the system loses charge quickly will have to make a repair. or will just add refrigerant until they get it replaced. True 4 draw under the grill cooler Model TRCB-79-86 Serial 1-4132624 Refrig unit AEA4440YXA Refrigerant R134a 8 oz
10-22-21 thur Kitchen salad prep table not working True TSSU-48-12 Found the compressor was tripped off, due to the condenser fan motor is not running. Removed and cleaned the condenser fan motor allow compressor to cool down compressor is working. I will pick up a new condenser fan motor also a star kit for the compressor and some evaporator coil cleaner Schedule to come back tomorrow morning to install.
9-17-21 True reach-in cooler repair Model T-23 Serial 8021227 Picked up new evaporator fan motor at the supply house. Remove existing evaporator fan motor and pan. Clean the evaporator coil and The surrounding area. Installed new evaporator fan motor. Tested for proper operation working at this time NOTES Evaporator motor and cleaner weâ€™re picked up on a separate job #93316688-101 I spoke to Jerry he will put my parts into this Job There is a picture of my parts pick up ticket
9-13-21 Installed customer supplied Hoshizaki ice machine KM-1601SWJ All fittings for water supply and drain all matched up to the existing unit after install ran and cycled the ice machine about four times. They are gonna let it run till probably 3 oâ€™clock. Then dump the ice and then refill and I can start using it. While on site had a true reach in cooler not working. T-23 Found the evaporator fan motor very hot and the The parade or real dirty Iâ€™m going to order a new evaporator fan motor, than were going to pull and clean the evaporator I have parts on order at united
8-16-21 Walk-in freezer itâ€™s not working properly Left side evaporator fan motor is starting and stopping. After numerous phone calls to the manufacturer,found out the evaporator fan motors are not rated for low temperature and humidity. I found this because I could not cross the existing evaporator fan motorâ€˜s over to any OEM part. I have located the motors I need to speak with James and Mark concerning replacing them and cost. 8-20-21 Picked up parts for 23 street brewery Need to speak with Rick B before any kind of billing." 8-24-21 Walk-in freezer Installed 2 low temperature evaporator fan motor and fan blades. Tested for proper operation. Tested system for proper defrost cycle with defrost termination control. Evaporator fan in walk-in freezer is working at this time. Notice during the call on 8-16-21 There was ice hanging from the condensate line in the freezer. Today I pulled back some of the insulation and found that the 3/4 copper condensate pipe had burst but als