Michael came, did his work and left. Answered my questions. Was polite and professional.
Replace the blower motor and belt in AHU- 1 located above the ceiling in the in the dining room. Check cooling operation the unit is cooling fine now the temperature split is 21*.
Arrived on site for lack of cooling in the dining room. Found Ahu #1, not cooling due to a seized up a blower motor. Informed Hazim of findings and he wants the wait until Tuesday to make repairs. Advise customer to shut the unit off until repairs are made to prevent any damage to unit.
Measured hood and provided drawings of existing equipment
I met with a second balance company and assisted with equipment access and discussed the previous list of issues and modifications.
Reroute discharge under floor and cover pit
Estimate to reroute sump discharge and cover pit Will do work Thursday
A/C tune-up on Bosch ground source heat pump. No problems found.