Fron the initial install to noe everything has been first class
Job created so I could create and email a repair estimate.
Upon arrival, I found that the pilot light wasnâ€™t lit again. After further testing, Aaron and I determined that the thermocouple needed replaced. We still have a slight concern that the gas valve itself may have an intermittent fault but at this time the gas valve is operating as it should. The customer paid for the band aid level HM1A repair on 11-26-19 job#34955865 which on todayâ€™s invoice I have credited the entire amount of that repair because to get a replacement thermocouple we needed to be at the bronze level repair or a higher level. The customer paid the difference between the two repair options today 12-2-19. I will create an estimate for the proposed repair to the makeup water system and email that to the customer when completed. Thank you
I conducted a complementary boiler maintenance from the boiler installation last year. I found out the system is operating properly and safely within factory specifications.
We performed a maintenance and safety inspection on the hot water boiler system. We found the system to be operating within the manufacturers tolerances at this time. During the inspection, while putting the inducer motor assembly back together, the threads on the inducer housing for one screw were stripped and we had to use a tap to re-thread the component in order to re-install it. After completing the inspection the system was operating as it should. Furthermore, the customer purchased an annual recurring P3 boiler membership. Thank you
Arrived on site for no cooling. Found unit starting to ice over when I arrived. Thawed unit out and check refrigerant charge. Found 2*superheated and low suction pressure. Verify blower operation the blower motor is working fine. Check cleanliness of air filter the filter is ok at this time. Discovered dirty evaporator coil causing air flow restriction. The coil will have to be removed and cleaned. The coil is 15years old and starting rust in the lower section. Removing coil could cause refrigeration leaks. Informed customer of findings and he opted to replace Condenser and coil. Gather info for Zach S to estimate equipment. No charge due to previous trips.
Checked the 18,000 btu split system for too warm complaint. Found the space temp at 76 deg with the setpoint for 72 deg. Checked the evaporator split and found a 21.6 deg drop accross the coil. The unit is running at full capacity at this time. The building is a uninsulated brick structure and the load is greater than the system can handle at high temps and humidity. Explained the findings to Amanda. She stated that they turn up the stat when they leave at closing time. Advised the customer to not set back the thermostat during high load conditions when they leave to help the system keep up the next day.
Service technician was on site 4 hours ago and system appears to be slowly dropping temperature at 78 suggest customer wait over night to see operation in the morning temperature split still good at 22 degrees may need to clean evaporator coil and comb condenser coil if problems persist.
Upon arrival Jesse stated tang the a/c was not able to keep up it got up to 80Â°. I checked the unit and found the filter to be very dirty causing a restriction in air flow. I replaced the filter checked the temp split. The unit is operating properly at this time.
Carrier split system not cooling properly. Found the out door condensing coil dirty with debrie not allowing for correct airflow and heat rejection. The coil has been washed and cleared of all debris. The indoor air filter has been changed. Unit is now cooling properly at the correct pressures and temperatures.
Installed Ruud furnace and AC and coil with a new return drop and boot and humidifier, water heater.
Arrived to find out the indoor coil was frozen. After the coil was thawed, I found that the system was low on refrigerant. I performed an electronic refrigerant leak search and found a non-repairable leak at the indoor coil. The customer requested to have refrigerant and the internal leak sealer added to the system to get them by this summer. The customer will call at a later time to have somebody come out and quote new equipment pricing.
Air handler ac
I found the system shut out do to low pressure. The system is very low on R22.
Upon arrival jesse stated that the a/c was accidentally turned on and they noticed a rubber burning smell. After inspecting the unit i found that the capacitor was burned i believe due to weak connections. I replaced the capacitor and wire connections. I also noticed there was water in the blower wheel housing, i removed the blower assembly and cleaned it out. I reinstalled the blower assembly and tested the unit it is now operating properly at this time.
Performed a full cooling inspection. Washed and cleaned out outdoor unit. Check all safety switches. Unit is operating at factory specifications at this time.