Corbin checked everything and replaced a part. Then after he left, called his supervisor to ask his thoughts on the issue before returning and fixing something else.
Jesus and Jacob were prompt and professional. Jesus did an amazing job of explaining the processes and workings of the units. He provided information about how to keep the units working efficiently.
The technician was straight forward and made recommendations. He did not try to oversell his sales pitch. That usually turns me away from a company when they do that.
Arrived to call for Ecobee thermostat stating the house temperature had risen three degrees even though the call for cooling had never stopped. Upon arrival I starting performing my inspection at the outdoor condenser. The compressor was pulling correct amperage and the refrigerant temps/pressures showed a unit charged within spec. The fan however was pulling less than spec amps and the duel run capacitor had lost capacitance on the fan side. It was performing at 3.5 mfd when spec is 4.7-5.3. With customers approval I replaced this. On the indoor unit I found a dirty air filter that I recommended replacing more often to allow better airflow over the indoor coil. The temp split over the coil performed within spec. I then checked blower operation with it pulling correct amperage and the capacitor that feeds it operating within spec as well. If this issue continues while the AC is running this is an insulation issue rather than an AC not operating properly issue. AC running upon departure