Water heater inspection special with flush Company flushed and inspected all amenities on state select water heater 75 gallon 1. Shut off for cold side of water heater is gate valve which is operational. 2. Company also vacuumed out dust around burner assembly. 3. Ran water to ignite burner for testing. 4. Tested pressure for pressure regulating valve which is operating at 60 psi 5.Tested thermal expansion tank which is operational but is undersized. 6.Inspected gas line With leak detection Final report and conclusion is that Everything on water heater is testing ok at this time. Recommended repairs 1. Expansion tank replacement for code requirements. Customer does not want any estimates at this.