Representative was on time and completed work as required.
Checked the York rooftop S# N1K6997882 for refrigerant leak in the micro channel condenser. Found the right side compressor unplugged and void of refrigerant. Added nitrogen to locate the leak. Found the leak in the center of the South side of the condenser. Reseached the replacement coil. Called Keith and explained the options for repairs. Sent him a quote for repairs.
Performed pressure test on gas line per city inspector request. Gas line test has been passed at this time bye inspector.
Performed boiler tune up
Full tune up on the Jones Knight boiler and repairs