i have no ideas of what the recommendations are or mean and an approximate cost. i do not understanding the need to drill holes through the walls for testing not so good with this so far
Response from Fire Pros Inc:
Thank you for your honest feedback, we greatly appreciate it. I'm sorry for your negative experience, thank you for bringing it to our attention. We will be in touch shortly to reconcile your complaint and get you taken care of. Again we appreciate your business and we are very sorry for any confusion and will do everything in our power to help make this right!
Technician was prompt to appointment time, very willing to share his expertise and knowledge, very thorough in the inspection. THANKS!
Did a great job everything handled in 1 visit. Matt did a great job and explained the process.
BRANDON DID AN AMAZING JOB, MUCH APPRECIATED, THANK YOU
Wet In closet in bakery On riser: Replace all FDC piping from the check valve to the connection and retest the line after repair has been performed. Once piping reached 25psi it would no longer build pressure and technician discovered a sever leak at the threads inside the wall. FDC failed the hydro-static testing – leaks were present during the test meaning that the connection will not withstand high pressure and may fail during a fire. NFPA 25 (13.8.1)
Annual Exit & Emergency Lighting Inspection (62 EEs) Annual Fire Extinguisher Inspection (26 FEs) Emergency / Exit Lights and Portable Extinguishers Inspection
Quarterly Fire Sprinkler Inspection (1 wet)
Special Hazards Inspection
Annual Fire Alarm Inspection (34 devices) (Simplex 4005)
Annual Fire Extinguisher Inspection (10 units)
Annual Fire Alarm System Inspection (approx. 12 devices)