He was very informational and knowledgeable
Inspection at property went very well.
Great service, friendly and professional
Fast, and courteous!
They were very knowledgeable and very personable and friendly! They took the time to explain what they were doing and why! They didn’t waste any time they got right to it! When they come out I don’t have to worry about babysitting though they know what they’re doing they just do it and get it done!
Chris was really easy to work with right from the start he took time to explain to me what he was doing and he was very knowledgeable! I really enjoyed working with him! Thank you very much!
Great, professional work every time.
Completed Annual Fire Alarm inspection for 2020
Arrived on-Site NAC 1 Trouble on FACP Checked Batteries with load tester. Batteries failed load test and require replacement. Per. Francie they will be replacing NAC PNL Batteries. FACP will remain in trouble until batteries are replaced.
Kitchen Suppression Inspection
Kitchen Suppression, Emergency / Exit Lights, and Portable Extinguishers Inspection
Inoperable Deficiency for BAY/WAREHOUSE: Remote capable Combo light fixture and remote head are BAD. Tried installing new batteries, but fixture and emergency lights stay lit continuously. Need to replace: ** Remote capable combo light fixture ** Remote light fixture to match combo voltage Annual Fire Extinguisher Inspection (7 FE's) Annual Exit & Emergency Lighting Inspection (9 units)
Annual Fire Extinguisher Inspection- (1 in the basement)
FIRE EXTINGUISHERS: From our recent inspections, we noted the following service needed for code compliance - (6) 5# ABC BADGER EXTINGUISHERS WITH HOOK BRACKETS OVERDUE FOR 6 YEAR MAINTENANCE - we propose to repair - Portable Extinguishers Repair
FIRE EXTINGUISHERS: From our recent inspections, we noted the following service needed for code compliance - (12) 5# ABC BADGER EXTINGUISHERS WITH HOOK BRACKETS OVERDUE FOR 6 YEAR MAINTENANCE, INCLUDING ONE THAT REQUIRES RECHARGING SERVICE. NEED (1) REPLACEMENT HOSE STRAP - we propose to repair - Portable Extinguishers Repair