Fire Systems of Michigan's technicians provide excellent, quality service time and time again - one of the best contractors in my experience.
Gary Beckon of Fire Systems of Michigan performed the annual inspection of our facility's (80) fire extinguishers in a timely manner and a quality of work focus. It was his first time in our facility, yet he need minimal guidance to execute the work.
My hero today. Replaced a damaged Fire Panel
Very nice technician and excellent service!
Wet Pump rm se corner: Perform a 5-year internal assessment of system piping that is due. If an obstruction is present, this can render the sprinkler system not properly operate in the case of a fire (20' lift needed). NFPA 25 (184.108.40.206) An assessment of the internal condition of piping shall be conducted at a minimum of every 5 years or in accordance with 220.127.116.11 to inspect for the presence of foreign organic and inorganic material. Wet Pump rm se corner: Perform a 5-year internal inspection of the Fire Department Connection (FDC) check valve. NFPA 25 (18.104.22.168) Check valves shall be inspected internally every 5 years to verify that all components operate correctly, move freely, and are in good condition. Wet Pump rm se corner: INFORMATIONAL PURPOSE ONLY: The hydraulic Placard on both of the systems describes the system design and capacity. These are currently missing. We suggest that the customer reaches out to the installing company to request this information. This would be
Portable Extinguishers Repair
Notice of Non Compliance and Repair Proposal Fire Systems of Michigan, LLC. recently inspected/serviced the kitchen suppression system at your establishment in accordance with local fire codes and NFPA guidelines. While inspecting/servicing your kitchen suppression system, it was determined to be "Non-Compliant" per local fire codes and manufacturers specifications. This proposal summarizes the non-compliance issues that were found during the inspection and the costs and actions needed to correct them. Fire Systems of Michigan, LLC. strongly recommends that your kitchen suppression system is repaired so that it will become compliant. The kitchen suppression system as-is may not work properly due to the deficiencies described below and may not properly extinguish, suppress or control a fire. This is a safety hazard and may contribute to damages and injuries to your property and individuals in the event of a fire. The Services To Be Performed section below describes the work to be done t