There is a short reporting on Main Panel NAC 2 even though wiring disconnected and end of line resistor in its place.
System is going in and out of NAC trouble every 20 seconds.
Completed annual Fire Alarm and Extinguisher inspections for 2019
6 Smoke Detectors were Replaced and Tested. ***All systems normal and reset ***
Cleared NAC TBL ***All systems Normal and Reset ***
Completed Emergency Service Call
Completed Emergency Service Call after false Alarm
Completed Annual extinguisher and Fire Alarm inspections for 2018
Completed Annual Fire Alarm and extinguisher inspections for 2018