Service persons were helpful and well trained.
The Technician was professional and the whole procedure was very quick.
Technician was very professional and explained everything. The whole process was pretty painless :)
Fire Pros is fast, efficient and very punctual. Technicians are very professional.
The techs were great to work with, quick and efficient,
Annual Fire Extinguisher Inspection (28 units) Portable Extinguishers Inspection
Completed auto fryer inspection
Per Call from Becky Abbott - There are (4) Exit Signs that were noted as failed on a HUD Inspection. Need to be repaired on Tuesday, November 1st Portable Extinguishers Service Call
FACP BOILER MECHANICAL: Panel in alarm upon arrival and has power trouble as well. Checked the charging circuit and it is at 14.4 volts. Dropped power and panel died. Batteries are at 8.8/9.0 volts. Panel has a bad charging circuit and needs to be replaced. It is a Fire-Lite MS-4 panel. Both batteries need to be replaced as well. (2) 12V 7AH batteries. Zone 2 is the zone in alarm and trouble. Tried to resistor the zone, the trouble light goes off but the alarm remains. - repair This quote is for the replacement of the bad fire alarm panel. This quote includes. Panel Replacement, Installation & Testing. If permits are required an additional quote will be provided.