The Service Technician was very professional and great to work with. However, the Company itself did not communicate very well. They never informed they were coming to do the Sprinkler Inspection. I called the company back and left messages for two different people but have not heard back yet.
The service tech that came out was very professional, friendly, and thorough. He explained the inspection process prior to getting started and then after the service was completed, walked through what was done and what to expect next. I was very impressed.
Great guys to work with. Required minimal instruction.
Jason was a great tech. We have used Fire Pros for years. We have always experienced great customer service.
Great team, guys came in and needed little to know direction. Were fast and efficient.
Monthly Fire Extinguisher Inspection (135 FE's) Portable Extinguishers Inspection
Portable Extinguishers Inspection
Annual Fire Alarm Inspection monitored by CMS- acct# FLLV19177- **also see tech notes about system being tied into Pizza Ranch
Inoperable Deficiency for FACP MECH ROOM 4190: BUILDING 4190 FACP IS STUCK IN TROUBLE AND DOES NOT FUNCTION ON ALARM. SHOULD BE REPLACED WITH MS-4, SHOULD ALSO REPLACE ALL 6 BELLS AND MAY NEED TO TROUBLESHOOT T TAPS ON BELL CIRCUIT.
Deficiency for FACP 4260 LAUNDRY: BLDG 4260 FACP HAS NO CHARGING CIRCUIT AND BATTS ARE DEAD. PANEL NEEDS TO BE REPLACED. FIRELITE MS-2
Annual Fire Extinguisher Inspection (4 FE) Annual Exit & Emergency Lighting Inspection (5 units) Portable Extinguishers and Emergency / Exit Lights Inspection
Portable Extinguishers Service Call
remove old unused alarm devices per Tyler Tran.