Tyler always does his best and so friendly
Not only did he complete the work and do it well BUT, he helped us with one of our residents and never batted an eye. Great guy!
As always I got fast response and the appointment was made for the next day. Mike handled the problem I had and the system fully operational.
Awesome service from Mike! He was very very helpful, patient and friendly, he wanted to make sure I am fully understood the system and how to use it! I am left satisfied with ability to feel comfortable with handling the system on my own. Thank you!
**Commercial Fire Paperwork** Annual Fire Alarm Inspection
Annual Fire Alarm Inspection (243 devices) Mircom FX-2000 Alarm w/ (4) boosters
Annual Fire Alarm Inspection (145 Devices) (Notifier 5000) *needs two technician for alarm inspection
manual pull station 1st floor by 104 is bad and needs to be replaced. - repair Upon arrival system had both fuses removed. For the trouble and the signal circuit. I re installed them and system went right into alarm and trouble. I located the manual pull in alarm and it was physically broken and stuck in alarm. I removed this device from the system and the alarm cleared. I tried testing all 3 other manual pull stations but none of them put the system into alarm. This is a 120volt only National Time system. To fix we would need to replace all 4 manual pulls at minimum. Possibly need to fix issue with the 120volt wiring to the devices? As of right now system is non operational. Or recommend upgrading the system as it is very old. - repair This quote is for an alarm technician to come out and make an attempt to get the system up if possible . This system has ran its life span it is ready to be all replaced . Not certain if we can fix this problem so this quote is an attempt only . Note
Per Scott- needs service out to check system- it is not testing. CMS acct# FLV128768
Annual Fire Alarm Inspection National Time Panel (110v) 4 mps, 2 horn (all in common areas)
Honeywell Wireless Garage door contact is broken. Please quote a replacement. model 5800 RPS. - This quote has one hour for programming and installation.