I think it was a bit of a challenge as the water did not want to shut off but Russ got it to work
During an exhausting fire watch, with several problems to fix, the team were quick to get parts and be on sight as soon as they could. During a difficult week it was great to feel like Fire Pros was on my side when others were making things difficult. A big thanks for all you all did.
His was great on response time. tech seemed to know what he was doing didn't have the right tools
Response from Fire Pros, LLC:
Thank you for leaving your review! We greatly appreciate your feedback and are glad that we provided you valuable service! At your convenience, please consider sharing your experience on Google as well. https://tinyurl.com/yylegs7q Thanks again and have a fire safe day!
Annual Fire Alarm Inspection (145 Devices) (Notifier 5000) *needs two technician for alarm inspection
Annual Fire Alarm Inspection (243 devices) Mircom FX-2000 Alarm w/ (4) boosters
Battery connection to the board in building 4 facp is getting loose and goes into trouble if you move it just right. System still functioning and charging batteries. If issue gets any worse custlmer will call and panel can be replaced with firelite ms-2. - repair
Portable Extinguishers Inspection
FACP ENTRANCE FOYER: FACP IS SHOWING A STROBE TROUBLE FOR ROOM 324, 326, and 328. NEED TO QUOTE LABOR TO COME BACK AND TRACK OUT THE ISSUE. - repair SD ROOM 409: NEED 1 SOUNDER BASE, AND 1 SMOKE HEAD TO FIX ROOM 409. ALL OTHER MISSING SMOKES HAVE BEEN FIXED. Customer has an open quote for 5 smoke detectors and bases. - repair
Jeff called in- strobe in room 331 keeps going on showing trouble on panel- nothing in the room. Jeff called back 6/23- said he is also having an issue in room 403- found smoke detector was completely disconnected- would like you to look at that one also. 269-986-9679
check system- keeps sending loss of central poll- Gordy pinged it - it only had 1.5 bars. Call Cyndi next week for appt- she will have someone meet you. DO what you can to increase signal strength- if equipment is needed consult management.
Per Scott- 269-365-6760- needs service out to check system, they have an alarm going off. NOT emergency service.