Completed annual Fire Extinguisher and emergency light inspections Also Replaced Pull pin for Mechanical Room Extinguisher that was missing
Completed sensitivity testing on all smoke detectors
Completed Annual extinguisher inspection for 2018
Completed Annual Fire Alarm Inspection's for 2018
Patched leak in garden center.
Removed 4 dry pendants for testing, replaced with new.
Annual Exit & Emergency Lighting Inspection (23 units) Annual Fire Extinguisher Inspection (19 FE) (Leave monthly tags with our standard tags) Inoperable Deficiency: replace exit light in gym by lockers room Inoperable Deficiency: replace 5 1.2v battery with leads for exit lights Emergency / Exit Lights and Portable Extinguishers Inspection