Completed sensitivity testing on all smoke detectors
Completed Annual extinguisher inspection for 2018
Completed Annual Fire Alarm Inspection's for 2018
Patched leak in garden center.
Removed 4 dry pendants for testing, replaced with new.
Annual Exit & Emergency Lighting Inspection (23 units) Annual Fire Extinguisher Inspection (19 FE) (Leave monthly tags with our standard tags) Inoperable Deficiency: replace exit light in gym by lockers room Inoperable Deficiency: replace 5 1.2v battery with leads for exit lights Emergency / Exit Lights and Portable Extinguishers Inspection