gary was great to work with
Fire pros was great to work with. They came right out inspected all our fire extinguisher. Services the ones that needed done. Gary was the tech the came out and he really knowledgeable and extremely nice. I will definitely be doing business with them again.
Thank you Fire Pros!
Very pleased with John (Reed) & Matt (Pearo) and there knowledge of our systems and sprinkler and standpipes. Inspections were done in a detailed manner.
Annual Fire Extinguishers Inspection (4 FE) Portable Extinguishers Inspection
Stand Pipe, Obstruction Investigation, Hydrostatic Testing, and Sprinkler Repair
Obstruction Investigation Repair
Annual Fire Extinguisher Inspection (50 FE) Annual Fire Extinguisher Inspection (50 FE) Portable Extinguishers Inspection
Annual Fire Extinguisher Inspection (50 FE) Deficiency: Number of Extinguishers Left at Job: 7 Need (6) NEW 10# ABC and (1) 5# Hydrotested to finish job Townhouses 1013, 1101, 1103, 1107, 1109, and 1115 need NEW TOWNHOUSE 1113 needs hydrotested unit
7- East wall: Perform a 5-year internal assessment of system piping that is due for systems #1, #3, #5, #7, #9, & #11 . If an obstruction is present, this can render the sprinkler system not properly operate in the case of a fire. The customer will provide the lift. NFPA 25 (188.8.131.52) An assessment of the internal condition of piping shall be conducted at a minimum of every 5 years or in accordance with 184.108.40.206 to inspect for the presence of foreign organic and inorganic material. 1- East wall: Perform a 5-year internal inspection of the system check valves for all 12 systems. NFPA 25 (220.127.116.11) Alarm valves and their associated strainers, filters, and restrictions orifices shall be inspected internally every 5 years unless tests indicate a greater frequency is necessary. 1- East wall: INFORMATIONAL PURPOSE ONLY: The 5-year Hydrostatic test of the FDC is due. Although, due to the inaccessibility of the check, the requirement of permits, and specialty equipment, the testing can no
Inspected fire extinguishers on (3) buses
Jason called and said that there having Dact issues and wants his phone lines checked . Jason knows this will be emergency call .
Picked 8 fire extinguishers for service and exchanged 1 on site that failed.
Completed kitchen suppression system inspections
Completed quoted job. Plumber will need to install gas valve that Chris Gardner will drop off.