Very pleased with John (Reed) & Matt (Pearo) and there knowledge of our systems and sprinkler and standpipes. Inspections were done in a detailed manner.
Semi-annual Fire Extinguisher Inspection (46 FE) Semi-annual Industrial System Inspection Semi-annual Exit & Emergency Lighting Inspection (43 units) Portable Extinguishers, Industrial/Dry Chemical Suppression, and Emergency / Exit Lights Inspection
Annual Fire Alarm Inspection
Deficiency: Jockey pump control valves are not monitored lock and chain shall be installed. 2- breakaway locks 2- 1’-0” steel braided cable Deficiency: Jockey Pump control valves are not identified signs shall be installed for proper identification. 2- control valve signs with chain Deficiency: Manual fill valve is not identified a sign shall be installed for proper identification. 1- control valve sign w/chain Deficiency: Dry ITV is not identified a sign shall be installed for proper identification. 1- ITV sign w/chain