I think your people are always good and do a professional job
3/24/21 Confirmed with Anna for 3/25/21 Thursday SM3 Portable Extinguishers Inspection Annual Extinguisher Inspection ( 21 ABCs , 3 CO2s ) Deficiency: 2 10lb abc need recharge,1 10lb abc needs 6 year maintenance Deficiency: Extinguisher (1) 10abc needs recharge (discharged)
Kitchen Suppression Inspection
Replaced Missing Smoke Detector in Deputy Directors office and Reset System also Updated Date and time on FACP.***All Systems Normal and Reset ***
8/28 Approved by Jeff A. We used to service this all they time, we lost the KISUP tab in the switchover. No cooking so anytime between 8:00 and 4:00 km Kitchen Suppression Inspection Seminannual service of kitchen hood suppression system Deficiency: Electric fuel source outlets and electric non fuel source outlets under hood do not de energize upon fire system actuation.