horn strobes are all up by others -ground fault on panel. Customer request we troubleshoot.
Alarm Systems Service Call
Emergency / Exit Lights Repair
Emergency / Exit Lights and Portable Extinguishers Inspection
1/22/2020 - Peter Pokryfke 269-598-1061 called in to have the system switch-tested to confirm the deficiencies were taken care of. I told him between 7-8am. Kitchen Suppression Service Call Switch-test to confirm make-up air shut down. Per deficiencis noted on 10/25/19: Exhaust fan on basement hood system shuts down after approximately one to two minute delay. Exhaust fan should stay running. Air curtain on main and range hood does not shut down during system actuation.
Met with Jerry. FACP states open Circuit 4th floor There’s Currently no Access to Suite on 4th floor have to Reschedule to again Access Contact Jerry to Re-Schedule.