My restaurant is now ready for building inspection! Thanks to Robert! He showed up on time, is nice, smiling and helpful, does what he has to do with expertise and efficiency. And of course, explained me what he did in the building in terms I clearly understand ( don’t forget I’m French...). I’m highly appreciative of his professionalism! Thank you for making me feel safe in my new business! And a special thank to Kathie who works in the office and is a pleasure to talk to!
Robert came to my restaurant yesterday to service the fire system. He is a very nice person, friendly and smiling which is very important to me, he explained me everything about the system making sure I understood every word ! don’t forget I’m french and I can’t know every technical terms in English ! He answered patiently and clearly all my questions. When he left, I felt very confident about the safety of my restaurant and on a personal note, was glad to have met an actual wonderful human being
Sprinkler Service Call Connie called in a service call for issues with sprinkler system at Birmingham DPS Deficiency: Sprinkler system keypad will need to be replaced by manufacture. The alarm company or manufacturer will have to be notified in order to check this further because this keypad is not sending any bad signals out it just beeps.
11/22/23 Confirmed with Fred, for 1/8/24 at 12:00pm DH / 11/15/23MV Emailed Fred regarding inspection date 11/22, waiting on confirmation Sprinkler Inspection Annual Fire Sprinkler Inspection 1 Wet System Deficiency: Sprinkler system will need to control valve signs one main drain sign which should read test and drain Deficiency: Sprinkler system will need to control valve signs one main drain sign which should read test and drain 4- control valve signs 1- test and drain sign Deficiency: Antifreeze will need two signs, one at main riser, one at system in boiler room and two signs for RPZ 2- antifreeze signs 2- control valve signs for backflow preventer RPZ Deficiency: Antifreeze system must have control valves, tied to sprinkler fire alarm
9/26/23 Confirmed with Cole H. for 9/27/23 at 1:00pmish DH / Sent email regarding inspection DH NOTE: FACP is located in basement electrical room & the RISER is located in the basement mechanical room. 8/22/23MV Emailed Cole regarding inspection date 8/23, waiting on confirmation Sprinkler Inspection Annual Fire Sprinkler System Inspection Deficiency: Sprinkler system is due for gauge change. 1 gauge Deficiency: Sprinkler system is due for a check valve internal inspection. 2- Victaulic couplings Deficiency: Sprinkler system is due for internal obstruction investigation. 3- Victaulic couplings Deficiency: Sprinkler system is due fr fire department connection Hydro test Deficiency: Sprinkler system is due for internal obstruction investigation. 3- Victaulic couplings