I'm not confident I am knowledgeable enough to give a proper "review" on the quality of service or pricing since I am not trained or truthfully familiar with firesystems
that was good service
1/8 Xoichil called and requested service before 11:00 anyday. Confirmed Tuesday, tech arrival between 9 and 10 km 12/21 LM on vm km Portable Extinguishers and Kitchen Suppression Inspection Annual Fire Extinguisher Inspection (3) Portables Semiannual Kitchen Inspection (1) Ansul 6 Gallon System Deficiency for Ansul R-102 6 Gallon Right of Hood: Improper protection over 2B-Range and Grill. Deficiency: Number of Extinguishers Left at Job: 1 Deficiency: K-Class fire extinguisher out of hydro date.
12/15 Confirmed with Joanne. They leave at 3:00 PM km Kitchen Suppression Inspection Semi-annual Kitchen System Inspection Deficiency: Number of Systems failed : 1
12/3 LM for Eric (returned his call) km Portable Extinguishers and Kitchen Suppression Inspection Annual Fire Extinguisher Semi-Annual Kitchen Suppression System Inspection Deficiency: Number of Systems failed : 1 Deficiency: Number of Extinguishers Left at Job: 1 Deficiency: Range and Salamander are unprotected. Deficiency: Range is partially outside of hood. Deficiency: Deep fryers are improperly protected. Deficiency: Middle grill improperly protected. Deficiency: Right Side grill is outside of hood. Inoperable Deficiency: Electric outlets under hood not working prior to test. Deficiency: Refrigerator under hood is plugged in outside of hood with extension cord and does not de-energize during system actuation. Inoperable Deficiency: Built In make up air not working prior to test. Deficiency: K-Class fire extinguisher out of hydro date. Deficiency: 1- PCL-600 tank out of hydro date.
11/24 - Scheduled with Mike. Anytime before 4:00 p.m. They close at 5 mh Portable Extinguishers Inspection Annual Fire Extinguisher Inspection (1 FE)
10/1 Time change confirmed with Nancy...11:30 is a better time. She'll advise Alan. km 9/29 Requested and confirmed by Alan. He'll be on site for you. km 9/9 Open for leagues only per message LM to call on VM and emailed Alan. km 8/7 Still closed. km 6/25 STILL closed per message km 4/10 Closed per message Kitchen Suppression Inspection Semi-annual Kitchen System Inspection
9/28 - Justin returned call and scheduled. mh 9/25 ln on vm for Justin mh Portable Extinguishers and Kitchen Suppression Inspection Annual Fire Extinguisher Inspection K-Class only Semiannual Kitchen System Inspection
9/28/2020 - Appointment approve by Jerry for 9/28/2020 11am. Notice of Non Compliance and Repair Proposal Fire Pros, LLC recently inspected/serviced the kitchen suppression system at your establishment in accordance with local fire codes and NFPA guidelines. While inspecting/servicing your kitchen suppression system, it was determined to be "Non-Compliant" per local fire codes and manufacturers specifications. This proposal summarizes the non-compliance issues that were found during the inspection and the costs and actions needed to correct them. Fire Pros, LLC strongly recommends that your kitchen suppression system is repaired so that it will become compliant. The kitchen suppression system as-is will not work properly due to the deficiencies described below and will not properly extinguish, suppress or control a fire. This is a safety hazard and may contribute to damages and injuries to your property and individuals in the event of a fire. The Services To Be Performed section below
9/15 Service requested by Al, owner. He's reopening under a different name, but needs this serviced. There is no cooking here now. km Kitchen Suppression and Portable Extinguishers Inspection Semiannual Kitchen System Inspection Annual Extinguisher Inspection
9/10 Rescheduled due to FSM schedule change. Approved by Kelly, Dave Luce will be on site on Monday. Cannot be later than Monday...DO NOT MISS! KM 9/8 Service requested by Mike O'Neill, coordinated with Kelly. Her cell: 734-664-1799 Either she or Dave Luce will be on site. Tech arrival between Noon and 1:00 PM km Kitchen Suppression and Portable Extinguishers Inspection Semi-Annual Kitchen Suppression System Inspection R102-D6 (2)360 links (9)Nozzles Inspect fire extinguishers Deficiency for R-102 6G above sink: Automan has red button. Deficiency: 1- 10# abc fire extinguisher due for 6yr maintenance. 1- 10#abc fire extinguisher due for hydro test. 3- 5# abc kidde due for replacement.
8/13 Scheduled with Kevin mh Portable Extinguishers Inspection Annual Extinguisher Inspection
8/3 - Greg called Jim Sullivan and scheduled. mh 6/30 NA, LM on VM km TD 3.19.20 Greg said call back in April TD 2.14.20 Greg stated Jim sets up inspections, call back. Kitchen Suppression Inspection Semiannual Kitchen Inspection (1) Ansul 3 Gallon System
7/27 Approved by Pepe Luis, Owner. They don't start cooking right away, and he'll get alarms in TEST and will pay COD km Portable Extinguishers and Kitchen Suppression Inspection Annual Extinguisher Inspection Semiannual Kitchen System Inspection