3/13-Mike confirmed the kitchen suppression inspection aware of alarms NW Kitchen Suppression and Portable Extinguishers Inspection Semiannual Kitchen System Inspection Annual Extinguisher Inspection Deficiency for R-102 3G right of hood: Upstairs system Deep Fryer is undetected electric fuel source does not shut down during system actuation. Deficiency for R-102 3G right of hood: Upstairs system automan has red button. Deficiency for R-102 3G right of hood/in black cabinet: Downstairs system automan has red button.
Special Hazards and Portable Extinguishers Inspection
Annual Fire Extinguisher Inspection (5 FE) Annual Emergency/Exit Light Inspection (16 units)