Jim has been our service provider for a very long time, he has always given us the best service and has been extremely professional and friendly.
On time, professional, super thorough, and gave me some great tips for the future. Extremely satisfied!
I'm not confident I am knowledgeable enough to give a proper "review" on the quality of service or pricing since I am not trained or truthfully familiar with firesystems
that was good service
Portable Extinguishers and Emergency / Exit Lights Inspection
5/13/22 Confirmed with Jim for Tuesday 5/17/22 sm /5/4/22 called and let Vm SM Portable Extinguishers and Kitchen Suppression Inspection Annual Fire Extinguisher Inspection (3) Portables Semiannual Kitchen Inspection (1) Ansul 3 Gallon System
4/28/22 Confirmed with Brenda for tuesday 5/3/22 She will putthe alarms in to test SM Kitchen Suppression Inspection Semi-Annual Kitchen Suppression System Inspection Deficiency for Ansul R-102 6 Gallon Right of Grill Hood: Electric outlets under fryer hood and grill hood do not de energize upon fire system actuation. Deficiency for Ansul R-102 6 Gallon Right of Grill Hood: Ansul system does not have a discharge warning device. Deficiency: Number of Systems failed : 1
4/14 LMF or Ken km ATTN: Kenneth Poucket PH: (734) 558-6532 EMAIL: email@example.com . RE: FIRE EXTINGUISHERS & EXIT/EMERGENCY LIGHTING - NEW EQUIPMENT . Kenneth, Thank you for your consideration of FIRE SYSTEMS OF MICHIGAN, LLC. as a service provider for your organization. We appreciate the opportunity to keep your facility fire safe and code compliant. Per your request, we propose to supply and install the New Fire Extinguishers & Exit/Emergency Lighting needed. Below is a listing of our proposed work scope - as well as a cost for the service. . Portable Extinguishers Service Call FIRE EXTINGUISHERS: Service to provide and install (2) New 5#ABC Fire Extinguishers for coverage in facility as requested. NOTE: Includes the New Extinguishers, Standard Wall Mounting Brackets, Location Identification Signage, 1st Year of Annual Certification (Tagging), and Installation as per NFPA 10 Code EXIT / EMERGENCY LIGHTING: Service to remove (2) non-functioning E-Lighting
Completed annual Fire Extinguisher inspection for 2022
11/29 LM and emailed Greg with appt. km 11/23 FSM Running too late. It's too close to his opening..he's cooking now. Requested TUESDAY at 10;00 AM km 11/22 Scheduled with Greg...call him if you can't make it! km Kitchen Suppression Inspection Semiannual Kitchen Inspection (1) Ansul 3 Gallon System Deficiency: Number of Systems failed : 1
Notice of Non Compliance and Repair Proposal Fire Systems of Michigan recently inspected the fire extinguishers at your establishment in accordance with applicable state statutes, local fire codes and NFPA guidelines. While inspecting your extinguishers, they were determined to be "Non-Compliant" per local fire codes. The attached proposal summarizes the non-compliance issues that were found during the inspection and the costs and actions needed to correct them. Please contact me as soon as possible to review the attached proposal and schedule the repair to your fire extinguishers. I look forward to working with you to bring your extinguishers into compliance. To discuss this proposal, please contact: Rob Harrison Phone: (616) 588-0746 Email: firstname.lastname@example.org EQUIPMENT REPAIR AGREEMENT This Agreement between FIRE SYSTEMS OF MICHIGAN (Company) and you (the Customer) provides for repair services only on the equipment indicated on the "Scope of Work" and "Services to Be Completed
10/12 Complete semiannual when you're doing the repair. km Kitchen Suppression and Portable Extinguishers Inspection Semi-Annual Kitchen Suppression System Inspection Annual inspection of fire extinguishers Deficiency: Number of Systems failed : 1
9/28 Confirmed with Mike, Ok's hydro K guard. Also write a deficiency report on the hood suppression. km Portable Extinguishers Inspection Annual Fire Extinguisher
Completed annual Fire Extinguisher inspection for 2021