Your guys are always here when they say they are going to be, and are super friendly!
Firepros and Matt were great. Called to schedule a fire extinguisher inspection 3 days later Matt showed up did a quality, quick, and knowledgeable inspection.
Gary was so good to tap most all the snow from his feet when he came in. Courteous and polite. He got right to work, and completed work with utmost professionalism. We've always gotten great service from Fire Pro Services. Ann W at HW Farms.
Very professional and inclusive, follow up reporting is key.
Gary always comes in with a smile on his face, knowledge about our extinguishers and helpful tips.
The Central Station is a run of multiple troubles from this panel that need corrected. Here is just a few 16:45:19 AN975507 E608 20WT - Timer Test with Trbl zone: 0, SYSTEM OFF NORMAL, 38 TRO990 - Trbl (C) SMS/Email SENSOR TROUBLE, AN975507 E321 TRO513 - Trbl (C) PR-CL 0 Sec BELL CIRCUIT . Please fix issues. Perhaps going into programming in the history and finding it that way.
Annual Fire Extinguisher Inspection (7 units) Portable Extinguishers Inspection
Annual Fire Extinguisher Inspection (15 units) Portable Extinguishers Inspection
Semi-annual Kitchen Suppression System Inspection PCL 3 GAL AB Bakery PCL 2.4 GAL AB Deli Semi-annual Fire Extinguisher Inspection (16 FE's) Semi-annual Exit & Emergency Lighting Inspection (40 units) Kitchen Suppression, Portable Extinguishers, and Emergency / Exit Lights Inspection
Annual Fire Extinguisher Inspection (21 units) Portable Extinguishers Inspection
This quote is for fire pros to provide the cellular equipment for monitoring the fire alarm panel. This quote includes the equipment programming and testing . The location of the cell unit will be by the fire alarm panel.
Emergency / Exit Lights and Portable Extinguishers Inspection Semi-annual Exit & Emergency Lighting Inspection (11 units) Semi-annual Fire Extinguisher Inspection (5 FE)
Semi-annual Fire Extinguisher Inspection (72 units) Portable Extinguishers Inspection
The handle for inspector valve #3 is missing. A new one will need to be installed. The ITV is located at the north side stairwell.
Wet: Install the missing handle on the main drain for system #2. Wet: Install the missing handle on the inspector test valve for system #2. Wet: Install the missing handles on the (2) PIVs located on the south side of the building. Wet: Remove and replace the painted sprinkler head in the maintenance room on the 1st floor. NFPA 25 (184.108.40.206.1) Any sprinkler that shows signs of any of the following shall be replaced; (6.) Paint other than that applied by the sprinkler manufacturer. Wet: Peform the 5-year flow test on the standpipe. NFPA 25 (220.127.116.11) A flow test shall be conducted every 5 years on all automatic standpipe systems to verify that the required flow and pressure are available at the hydraulically most remote hose valve outlet(s) while flowing the standpipe system demand. Perform a 5-year Hydrostatic test on the Fire Department Connection (FDC). NFPA 25 (13.8.5) The piping from the fire department connection to the fire department connection check valve shall be hydros