Your guys are always here when they say they are going to be, and are super friendly!
Firepros and Matt were great. Called to schedule a fire extinguisher inspection 3 days later Matt showed up did a quality, quick, and knowledgeable inspection.
Gary was so good to tap most all the snow from his feet when he came in. Courteous and polite. He got right to work, and completed work with utmost professionalism. We've always gotten great service from Fire Pro Services. Ann W at HW Farms.
Very professional and inclusive, follow up reporting is key.
Gary always comes in with a smile on his face, knowledge about our extinguishers and helpful tips.
Wet: Install the missing handle on the main drain for system #2. Wet: Install the missing handle on the inspector test valve for system #2. Wet: Install the missing handles on the (2) PIVs located on the south side of the building. Wet: Remove and replace the painted sprinkler head in the maintenance room on the 1st floor. NFPA 25 (184.108.40.206.1) Any sprinkler that shows signs of any of the following shall be replaced; (6.) Paint other than that applied by the sprinkler manufacturer. Wet: Peform the 5-year flow test on the standpipe. NFPA 25 (220.127.116.11) A flow test shall be conducted every 5 years on all automatic standpipe systems to verify that the required flow and pressure are available at the hydraulically most remote hose valve outlet(s) while flowing the standpipe system demand. Perform a 5-year Hydrostatic test on the Fire Department Connection (FDC). NFPA 25 (13.8.5) The piping from the fire department connection to the fire department connection check valve shall be hydros
Return (2) 5# Halotron extinguishers pulled for 6-year service at inspection 5/5/2021
Per Chris they have several FE they need recharged Portable Extinguishers Service Call
Annual Fire Extinguisher Inspection (5 FE) Portable Extinguishers Inspection
Annual Fire Extinguisher Inspection (17 FE) Portable Extinguishers Inspection
No charge call to send signals into monitoring after cell upgrade- and label transformer for cellular.
This quote is for Fire Pros to provide the equipment and labor for the 5G upgrade.
Semi-annual Kitchen Suppression System Inspection PCL 3 GAL AB Bakery PCL 2.4 GAL AB Deli Semi-annual Fire Extinguisher Inspection (16 FE's) Semi-annual Exit & Emergency Lighting Inspection (40 units) Kitchen Suppression, Portable Extinguishers, and Emergency / Exit Lights Inspection
Portable Extinguishers Inspection
Annual Fire Extinguisher Inspection (7 FE)
Annual Fire Alarm Inspection (9 devices) (Firelite MS-2)
Semi-annual Fire Extinguisher Inspection (6 FE) Semi-annual Exit & Emergency Lighting Inspection (9 units) Semi-annual Kitchen Suppression System Inspection (Pyrochem PCL 300 & Range Guard RG-4GM New Badger Head) Portable Extinguishers, Emergency / Exit Lights, and Kitchen Suppression Inspection