Ryan and his partner were at our plant less than an hour. Everything went well.
Annual Fire Extinguisher Inspection (14 units) Portable Extinguishers Inspection
Completed fire extinguisher inspection.
Annual Fire Alarm Inspection (24 devices) (Edwards EST 1)
NAC OFFICE IT ROOM: Div 3: Horn strobes did not sound under AC loss, and only horn sounded while AC was on, no strobes. Batteries all new in 2021 and passed load test. Charging circuits all ok. Possible power supply or wiring issue: Altronix AL600UL-ADA - repair This quote is for an alarm technician to come out and trouble shoot the issue with the Power Supply attached to the fire alarm panel which controls the horn/strobes. The above found on this inspection failed and needs attention.
Annual Fire Extinguisher Inspection (46 FE)
Annual Fire Extinguisher Inspections (7 FE?) Portable Extinguishers Inspection
Alarm Systems Inspection