Annual Fire Alarm System Inspection.
Annual fire alarm system inspection.
Performed troubleshooting to determine why zone 5 RTU #5 was disconnected in the FACP.
Checked system due to NAC troubles.
Thank you for the opportunity to submit the following proposal. Please don't hesitate with questions or concerns. Reach out if a phone call or a site meeting is needed to go over anything on the proposal. Thank you again for this opportunity to provide life safety and fire protection services. Our goal is to expand our professional relationship exemplifying integrity, honesty, and to be mutually beneficial for the future. Fire Pros Additional trip needed to fix deficiencies following our annual fire safety inspection(s): FIRE ALARM SYSTEM Please reference our repair quotation details as outlined below. Price includes all materials and labor to complete the mentioned service(s). We appreciate your business! Alarm Systems Repair FACP FRONT ENTRANCE: 2 batteries in main Fire Alarm Panel are due for replacement. dated 2013. BOOSTER MECH THROUGH TRASH ROOM: 1 battery in Fire Alarm Dialer in furnace room 2nd floor due for replacement. dated 2013.
Fixed several issues with the alarm system.
Kitchen Exhaust Cleaning Cleaning