All very professional
Very good had the valve that we needed. Terrance delivered the part on time. Terrance was polite and very professional. He saved us from shutting part of the plant facility down on Monday. Called three other companies, and your company was the only one that came through.
No problems at all. Tech was nice and efficient
Jim and Alex were great. very friendly:)
Jared speaks excellent Spanish which is a plus for my restaurants to communicated with employees. Jared shares his knowledge with my employees on how the system works and how to keep it clean to work effectively. A+ customer service.
Excellent customer service.
Completed annual Fire Extinguisher inspection for 2022
Scheduled with GM Deanne, she'll be on duty for you. Deanne will open a Corrigo Work Order. km Kitchen Suppression Inspection Semi-Annual Kitchen Inspection (1) Ansul 6 Gallon System
12/6 Rescheduled with Chewy...km 12/1 Scheduled with Chew, manager. He'll be on duty for you km Kitchen Suppression, Emergency / Exit Lights, and Portable Extinguishers Inspection Semi-annual Kitchen System Inspection Semi-Annual Emergency/Exit Light Inspection Annual Extinguisher Inspection Deficiency: Amerex expellant cartridge is under pressurized. Deficiency: Number of Systems failed : 1 Inoperable Deficiency for Left of hood: Emergency light right side of hood needs new battery.
8/26 Confirmed with Pastor Frank for 9/2 He'll be on site for you km 8/20 LM for and emailed Andy km Kitchen Suppression and Portable Extinguishers Inspection Semiannual Kitchen System Inspection Annual Extinguisher Inspection
7/30/21 confirmed with karen for Thursday 8/5/21 sM Karen will be in @ 3:00 PM Friday. 2/1 NA at 11:30 AM. Google says they're open, emailed Karen again. km 12/21 NA no vm option, emailed Karen. km Portable Extinguishers and Kitchen Suppression Inspection Annual Extinguisher Inspection ( 5 FEs ) Semiannual Kitchen Suppression System Inspection ( 1 Ansul 3G, 1 Pyrochem 4.6G ) Deficiency: Ansul system has a red button automan. Inoperable Deficiency: Discharge warning device has dead battery. Deficiency: Three 2012 5# ABC extinguishers due for 6yr. maintenance. Replacement with hydro’d units suggested. Deficiency: Discharge warning device does not operate during system actuation on main hood system. Deficiency: Number of Systems failed : 1
8/3/21 /confirmed with Jane for Wednesday 8/4/21 sM Portable Extinguishers and Kitchen Suppression Inspection Annual Fire Extinguisher Inspection Semi-Annual Kitchen Suppression System Inspection Ansul R102-S3 (2)360 links (4)Nozzles Deficiency for K-Class K Class Kitchen: K-Class in Kitchen due for Hydro Test.
Installation Job# 421-009 Add or relocate no more than (25) sprinklers for the remodeled Verizon store
Corrected deficiency from recent inspection Replaced 1-6 liter K Class Extinguisher with New