Very good had the valve that we needed. Terrance delivered the part on time. Terrance was polite and very professional. He saved us from shutting part of the plant facility down on Monday. Called three other companies, and your company was the only one that came through.
No problems at all. Tech was nice and efficient
Jim and Alex were great. very friendly:)
Jared speaks excellent Spanish which is a plus for my restaurants to communicated with employees. Jared shares his knowledge with my employees on how the system works and how to keep it clean to work effectively. A+ customer service.
Excellent customer service.
4/15 - Scheduled with Brandon mh Portable Extinguishers Inspection Annual inspection of the fire extinguishers
4/15 LM for Paul and emailed inspection date/time km 4/5 LM for Paul that we need to reschedule and would like to start at 9:00 AM km 3/22 Requested by and confirmed with Paul. He'll keep equipment off until you're done under the hood. ( I estimated an hour under the hood) km 11/12 LM for Paul for new Appt. UNCONFIRMED km 9/25 Confirmed with Paul, I advised him we need to service before they fire up the equipment, he said 10:00 AM. He'll notify the store manager of our appt. km Portable Extinguishers and Kitchen Suppression Inspection Annual Fire Extinguisher Inspection (4 FE?) Semi-Annual Kitchen Hood Fire Suppression System Inspection (Ansul?) Deficiency: Electric fuel source on Henny Penny fryer and Heat Cabinet does not shut down during system actuation. Deficiency: Prep hood detector brackets are not centered in the duct. Inoperable Deficiency: Exhaust fan on prep hood not working prior to test. Deficiency: Both systems do not have a discharge warning device. Deficiency: Numb
3/18 Confirmed with Mgr. Beth. Martin will be on duty for you km Portable Extinguishers, Emergency / Exit Lights, and Kitchen Suppression Inspection Annual Extinguisher Inspection (4 FE) Semi-Annual Emergency/Exit Light Inspection (26 units) Semi-annual Kitchen Suppression System Inspection (RG 6 gal ) Deficiency: Number of Extinguishers Left at Job: 1 K class Badger is out of hydro date and needs replacing. (New) Inoperable Deficiency for DINING BY COUNTER: Emergency light above front counter and emergency light dining room south side middle failed test. Needs 2 new batteries. Deficiency for Range Gaurd RG 6 Gallon Left of Hood: 2- nozzles in left hood duct need foil seals.
Technician, please make sure they open a Corigo work order. SM Monitored by Guardian FACP at pickup door Riser location outside riser room ITV on riser 3/9/21 Confirmed with Rebecca for Tuesday 3/16/21 . Andy will be there to put the alarms in to test SM Kitchen Suppression, Emergency / Exit Lights, and Portable Extinguishers Inspection Semi-annual Kitchen System Inspection Semi-Annual Emergency/Exit Light Inspection Annual Extinguisher Inspection Deficiency: Number of Systems failed : 1 Deficiency for Amerex KP 375x2 End Cap: Amerex detect-a-wire is 3 years old and needs to be replaced. Deficiency for Amerex KP 375x2 End Cap: Clogged surface protection nozzle. Deficiency for K-Class K Class K By walk in: K-Class fire extinguisher has been discharged.
2/9 confirmed with Ms. Penny. Don't do the alarm part until the kids wake up from their naps. km Kitchen Suppression Inspection Semiannual Kitchen Inspection Ansul R102-S3 (2)360 links (5)Nozzles
3/8 Confirmed with Pastor Bill km Portable Extinguishers Inspection Annual Fire Extinguisher Inspection (7)ABC
Inspected 2 Upstairs Extinguishers that were missed from previous inspection and Replaced 1-5lb ABC Due for 6 year maintenance with New
12/1 - Confirmed with Brad mh 11/10 - Confirmed with Brad. 734-972-4992 - DO NOT MISS!! mh Portable Extinguishers and Kitchen Suppression Inspection Annual Extinguisher Inspection (3) Portable Extinguishers Semi-Annual Kitchen Inspection (1) Ansul 9 Gallon & (1) Ansul 6 Gallon Systems need to go back out and inspect the 9 gallon system Deficiency for Ansul R102 6 gallon Built into top of hood#2: Electrical connections made inside of automan, connections should be made inside handy box. Deficiency for 10 lb ABC Back door: 10lb badger extinguisher at back door is damaged and discharged. Needs small easy out to remove broken threading from hose. New hose and recharge. Deficiency for Ansul R102 6 gallon Built into top of hood#2: Pull station blocked by thermolizer and dump station? Deficiency for Ansul R102 6 gallon Built into top of hood#2: Left oven is partially outside of hood. Deficiency for Ansul R102 9 gallon Built in hood#1: Electric connections on 9 gallon system are made insi