I can always count on Gary to be on-time, prepared and very helpful.
Always on time, Inspections are complete. Paperwork is complete. Very friendly and easy to work with.
More than willing to do what we needed. Very professional and courteous
Tech arrived on time and was able to quickly and efficiently get us ready to go.
Great job, Zac was professional and personable.
Showed up on time and knew what he was doing. Thanks again
Emergency / Exit Lights Repair EXIT / EMERGENCY LIGHTING: From our recent inspections, we noted the following service needed for code compliance - Numerous Exit/Emergency light batteries and fixtures need replacement. NiCad Batteries for Replacement - E-Light Fixtures #1, #7, #11, #16, #21, and #94 New Combo Light Fixtures as replacements. New Fixtures would be LED type as replacement for Incandescent style. LED's are more energy efficient in terms of power utilized for function and are less expensive to maintain (replacement parts - Batteries/Bulbs) E-Light Fixtures #3, #4, #76, #77, #81, #98, #101, #112, and #123 New Emergency Light Fixtures as replacements. New Fixtures would be LED type as replacement for Incandescent style. LED's are more energy efficient in terms of power utilized for function and are less expensive to maintain (replacement parts - Batteries/Bulbs) E-Light Fixtures #66, #95, #96, #100, #103, #107, #110, and #114 At the time of replacement of the previously
Annual Fire Alarm Inspection of (2) panels Silent Knight 6712 DMP and 60 alarm devices
Monthly Post Indicator Valve Inspections 2020 - PO# 40497857 / Item# 00070 **expires April 1, 2021 Monthly Inspection of (1) Dry & (1) Pre-Action Systems
Monthly Fire Extinguisher Inspection (204) Portable Extinguishers Inspection
David Reibel called in for emergency service to check the system - not able to arm. having tbl with the keypad. Nolan is the contact on site. 616-396-9914
**Commercial Fire Paperwork** Annual Fire Alarm Inspection ### 20 lift is needed.
Annual Fire Alarm Inspection (9 devices)
**Commercial Fire Paperwork** Annual Fire Alarm Inspection
Suggested: NAC 3 is in a trouble state. There are 4 NAC LINES LEAVING THE FACP. Deficiency: The duct detector is in trouble showing an open. Management has RTU shut down at this time. That will cause a duck detector open. When the RTU is fired up the duct detector may clear if there’s no other issue. Deficiency: This is information for a quote for cellular monitoring. Panel is not monitored at this time. Panel does have an onboard dialer with rj jacks.Panel is mounted on an outside wall in case an antenna is needed outdoors. Suggested: Front Annunciator has a hole in where enable it with the key. I was unable to get it enabled. Wiring is good I can read the display. The FACP is in a very back hard to find room, annunciator is at the front entrance and should be replaced for proper operation and ease of convenience for the fireman in an emergency situation Gamewell model by # GF ANN-80 or 41D2 .