George was very informative and very professional. Over all, very satisfied with his work!
very happy with service
Installed 2-5 lb ABC’s and 1-6 liter K Class Extinguisher with Seals and Tags
Notice of Non Compliance and Repair Proposal Fire Systems of Michigan, LLC. recently inspected/serviced the industrial fire suppression system at your establishment in accordance with local fire codes and NFPA guidelines. While inspecting/servicing your industrial fire suppression system, it was determined to be "Non-Compliant" per local fire codes and manufacturers specifications. This proposal summarizes the non-compliance issues that were found during the inspection and the costs and actions needed to correct them. Fire Systems of Michigan, LLC. strongly recommends that your industrial fire suppression system is repaired so that it will become compliant. The industrial fire suppression system as-is may not work properly due to the deficiencies described below and may not properly extinguish, suppress or control a fire. This is a safety hazard and may contribute to damages and injuries to your property and individuals in the event of a fire. The Services To Be Performed section below
1/13 Service requested by Connie. She understands the non-compliance. This store will be torn down and rebuilt brand new maybe this year, but meanwhile, they want to keep the links changed etc. km Kitchen Suppression Inspection Semiannual Kitchen System Inspection Ansul R102-S3 (3)360 links (4)Nozzles Ansul R102-S3 (3)280 links (5)Nozzles Ansul R102-S3 (3)360 links (5)Nozzles Deficiency: Number of Systems failed : 3 Deficiency for Ansul R-102 3 Gallon Right of Grill Hood: Discharge warning device does not operate during system actuation on all three systems. Deficiency for Ansul R-102 3 Gallon Right of Grill Hood: Improper nozzle protection over grills. Deficiency for Ansul R-102 3 Gallon Right of Grill Hood: Filet Fryer and Grill Hood systems have red button automan.