Very punctual and let’s you know what he is doing from beginning to end
Great service experience, serviced suppression system and made sure all cables and links were cleared and properly functioning. Outstanding job.
Both George and Tony were professional and exceptional in their work and skills sets. Appreciated having them not only service our site but offer some advise and educate my myself with their knowledge and expertise.
Pleasant nature, explained everything - pleased with the service rendered.
We enjoyed their customer service. Excellent!!
Sprinkler Repair **COMMERCIAL FIRE PAPERWORK ATTACHED: The tech will remove and replace the outdated water gauges. NFPA 25 (126.96.36.199) Gauges shall be replaced every 5 years
4/4/23 Confirmed with Tony T. for 3/5/23 in the afternoon DH Sprinkler Inspection Quarterly Fire Sprinkler Inspection (1 Wet System)
3/1/23 Confirmed by Jim S. for 3/2/23 at 12:00pm DH Sprinkler Repair The tech will remove and replace the outdated water gauge. The 6" water flow switch failed to report to the alarm panel. The tech will replace the switch. The tamper switch on the main OS&Y valve must be adjusted to operate properly. Currently, it is within the required time.
2/28/23 Sent email regarding inspection DH Sprinkler Inspection Annual Sprinkler System Inspection Deficiency: could find no record of a five year inspection. no lift Deficiency: System gauges are due for a change a total of three
2/28/23 Confirmed with Becka B. for 3/8/23 at 8:00am / Sent email regarding inspection DH Sprinkler Inspection Annual Fire Sprinkler Inspection (1 Wet System)