Both George and Tony were professional and exceptional in their work and skills sets. Appreciated having them not only service our site but offer some advise and educate my myself with their knowledge and expertise.
Pleasant nature, explained everything - pleased with the service rendered.
Completed Service Call. Fire Alarm System Functions as designed also contacted EMCOR dispatch and informed them that Fire Doors hold open and release properly. ***All Systems Normal and Reset ***
12/9 Called Tony to remind of 7:00AM appt. km 11/25 Last appt. missed due to the birth of Tony's child! Rescheduled for 12/10 at 7:00 Tony will leave a key for us. Called Lt. Boyce in RH fire to advise of appt. 248-841-2713 Notified Jennifer at all points alarm to put alarms in test. km 11/10 Tony called for service due to Fire Marshal issue. Do not miss! Understands no cooking km Portable Extinguishers and Kitchen Suppression Inspection Annual Extinguisher Inspection Semi-Annual Kitchen Suppression System Inspection Ansul R102-S3 (2)500 links (1)360 link (6)Nozzles Deficiency: Number of Systems failed : 1 Deficiency: K-class fire extinguisher out of hydro date.
12/4 Reminder sent via email. km 11/30 Confirmed with Adam. They are closed on Mondays, so there won't be cooking. EMailed confirmation km Kitchen Suppression Inspection Semiannual Kitchen Inspection Ansul R102-15gal (3)500 links (12)Nozzles Ansul R102-S3 (2)360 links (5)Nozzles