He was very through on making sure that everything was up to par.
Annual Alarm Inspection
Portable Extinguishers and Emergency / Exit Lights Inspection
Arrived on-Site Building B Fire Panel Reading Act Trbl 1 & 2. Customer states no changes were done with phone lines, phone lines have 52 volts dial tone. And have good tone. While monitoring both lines, attempted sending signals, Panel is communicating on Act # 3249 Receiver Phone # 1-800-218-1313, Panel Dialer is not hitting receiver. The receiver is not answering. Contacted Interstate Security Monitoring Center had them patch us to on-call technician they answered and said they would have to make a site visit to determine if it’s a receiver issue. Customer arranged with interstate to have them out in the morning. FACP will remain in trouble until receiver issue is resolved with interstate security.
Alarm Systems Inspection
Completed annual Fire Extinguisher/Emergency light and Smoke/CO Alarm Inspections for 2019