Kamp is an excellent partner!
Response from Fire Pros & Fire Systems of Michigan:
Thank you for leaving a review, we greatly appreciate your feedback! Camp is an awesome asset and we want to create value for you and your organization, Thanks again and have a fire safe day! Also if you have time, please visit Google and leave us a review there as well, we would greatly appreciate it!
Matt was wonderful
DD POOL MEZZANINE: Point M1-15 pool mezzanine duck detector is in trouble excessively dirty unable to clean it. Fire pros to order a new smoke detector head Model Simplex 4098-9714 - repair
Completed quoted work
Local bell is loose and can be tightened, need to replace bell. (1) 110V Horn/Strobe with weather proof box Caulk Hardware to mount to brick wall Riser in boiler room in mechanical room across from kitchen/ gym Breaker in located in electrical room across from boiler where riser is, panel marked as Emer LTG panel, breaker #6 Sprinkler system has own shut off, do not need to shut down water to entire building - repair
Annual Fire Alarm Inspection (346 devices)
Annual Fire Alarm Inspection (49 devices)
per james order a new simplex 4098-9714 smoke for gym area.
Deficiency for SD AUDITORIUM CEILING LIGHTING MEZZ: Smoke alarm located above the cat-walk above the stage in auditorium mounted to the ceiling is damaged and, giving a no answer trouble on the Simplex FACP. Jim Hicks stated they have had a lot of roof work a lot of pounding right above there and there is water on stage floor within 1 to 2 feet of smoke detector. **I am unable to get to that smoke detector now for model number but, all other smoke detectors on this site are 4098-9714**
Mike to meet new maint supervisor and show panels, how to check, how to reset. Calling CMS etc. While onsite verify that signals are coming in properly- Dawn mentioned getting messages from CMS that they were not.
Portable Fire Extinguishers-NFPA 10 Code: From our recent Inspections, we noted the following service needed for 2020 code compliance - (4) Fire Extinguishers missing from cabinets and (2) other units outdated for required service. (6) NEW 5#ABC EXTINGUISHERS PROPOSED TO REPAIR Portable Extinguishers Repair
Portable Extinguishers Inspection
Portable Extinguishers and Kitchen Suppression Inspection