9/24 approved by Chef Don. Tech arrival: anytime before noon. km Kitchen Suppression Inspection Semiannual Kitchen System Inspection
9/14 Confirmed with Henry for this Thursday at 8:30 AM km Portable Extinguishers and Kitchen Suppression Inspection ***COD*** - Annual Fire Extinguisher Inspections (2 FE) ***COD*** - Semi-Annual Kitchen Hood Fire Suppression System Inspection (PCL-300) Deficiency: Improper detector brackets for pyro Chem system. Deficiency: Pyro Chem control head does not have mounting bracket installed. Deficiency: Remote pull station is blocked by refrigerator.
Quarterly Sprinkler Inspection
7/21 - Scheduled with Mark mh Semiannual Kitchen System Inspection Kitchen Suppression Inspection
7/16 Confirmed with Cristina, This restaurant isn't open for business yet. km Portable Extinguishers and Kitchen Suppression Inspection Annual Fire Extinguisher Inspection (2 FE) ***COD - Customer to pay at time of service*** Semi-Annual Kitchen Hood Fire Suppression System Inspection ***COD - Customer to pay at time of service*** Deficiency: Improper nozzle protection, improper detection. Need to add tank,replace regulator and hose.
Portable Extinguishers and Kitchen Suppression Inspection Annual Extinguisher Inspection Semiannual Kitchen System Inspection Ansul R102-S3 (2)360 links (5)Nozzles
Annual inspection of the fire sprinkler system performed. All control valves exorcised and all flow valves tested. System operated properly at this time.
Frank called and said pull station was half way off. 734-558-4020 cell Kitchen Suppression Service Call Repair pull station. Hanging from wall
6/25 Approved by Owner, Vayaya. She picked the time that is best for her so we won't be in her way. km Portable Extinguishers and Kitchen Suppression Inspection Annual Fire Extinguisher Inspection Semi-annual Kitchen System Inspection Ansul R102-D6 (7)500 links (17)Nozzles
Portable Extinguishers Inspection