Very professional and simple transfer of documentation.
Very knowledgeable, they helped me resolve issues that most companies would not touch. I would never recommend a different company. Service technician-John was very educated in fire suppression and safety.
8/14 Cannot reach Travis. New appt. not confirmed yet. 8/10/23 confirmed with travis for Monday 8/14/23 Brent no longer there SM Confirmed sM' 4/10/23 Scheduled Via email. SM Portable Extinguishers Inspection Annual Fire Extinguisher Inspection (3 FE?)
Fire sprinkler system is in the oil change pit. Sprinkler Inspection Annual Fire Sprinkler System Inspection Deficiency: Sprinkler head box needs one head added. Deficiency: Flow switch has been disconnected and damaged a new flow switch must be installed and wired to outside bell. or alarm system if one is available if not the 110 bell 🛎 will have to be also iinstalled as it is not there anymore. Deficiency: Sprinkler system is due for gauge change.
3/22 Scheduled with Chris. km 3/22/23 Left VM SM Portable Extinguishers and Emergency / Exit Lights Inspection Annual Fire Extinguisher Inspection (5 FE?) Annual Exit/Emergency Lighting Inspection (10 EE)
3/20/23 Backflow has been repaired DH 1/16/23 Backflow is still broken will need to repair before inspection DH Annual Fire Sprinkler Inspection (1 Wet System) 5-Year Internal Due: FDC Hydro Due: Deficiency: Pipe burst in between first and second valve. Released main drain and closed first valve. Inoperable Deficiency: Backflow replacement for frozen backflow . See pictures for all info . Deficiency: Found Lower Riser Control Valve closed and no pressure on the Fire Riser. Inoperable Deficiency: The backflow on the sprinkler system has been damaged in a freeze it has not been replaced at all therefore system is totally in operable at this time.
1/16/23 Backflow is still broken will need to repair before inspection DH Sprinkler Inspection Annual Fire Sprinkler Inspection (1 Wet System) 5-Year Internal Due: FDC Hydro Due: Inoperable Deficiency: The backflow on the sprinkler system has been damaged in a freeze it has not been replaced at all therefore system is totally in operable at this time.
Sprinkler Inspection Annual Fire Sprinkler Inspection (1 Wet System) Deficiency: Missing ball drip on FDC pipe 1x1/2” bush 1/2 street 90 1/2” ball drip Suggested: Suggest removing sprinkler heads due to garage door has been removed 1” plugs x2 20’ extension ladder Suggested for Wet Sprinkler: Recalled heads in front seating area. (10) 1/2” 155 SE chrome pendants with escutcheons Deficiency: There is no evidence of 5 year FDC check valve inspection. Deficiency: There is evidence of 5 year FDC hydrostatic test. Deficiency: There is no evidence of 5 year internal pipe obstruction investigation. Deficiency: Missing control valve sign. Deficiency: Missing main drain sign. Deficiency: Mezzanine needs two additional heads added to cover area under it. Deficiency: Inspectors test needs sign. Deficiency: Missing escutcheons in seating area in gym by office area. Will have to lower heads to add escutcheons. (2) 1 x 1/2 RCs (2) 1/2” 155 SR chrome pendants with escutcheons 6’ 1” pipe Defici
Sprinkler Repair Add the missing supervision on the control valve. This will prevent tampering with. Remove and replace the 1" threaded flow switch due to the current one is leaking. Remove and replace the outdated water gauge.