TD 2.5.20 Eddie approved and will be on site @ 5a Semi-Annual Kitchen Suppression System Inspection Kitchen Suppression Inspection Deficiency: System tank out of hydro date.
Alarm Systems Service Call, tie in Southwest Duct Detector into Fire Alarm System
Completed annual Emergency light inspection for 2019
Arrived On-Site FACP showing 0267 Sprinkler Tamper Valves Short Circuit. After Trouble shooting found Short on pair of wires going to elevator sprinkler Tamper valve. Re-Wired Elevator Tamper valve and Reset System. After Resetting of Valve FACP stated Trouble on 0148 2nd floor North wing Smoke Detector. Located Smoke Detector and cleaned device and Reset System. After another attempt of resetting system, FACP PNL Batteries we’re showing in trouble. Load tested Batteries ( batteries failed load test and require replacement) ***Replaced FACP PNL Batteries and Reset System***. ***All Systems Normal and Reset ***
While performing annual fire sprinkler inspection the pump motor coupler came apart. Inspection will be rescheduled after repair has been made