Great friendly service
Alex was very thorough, personable, knowledgeable in his trade, and extremely helpful explaining the problems with our system in a way I could understand.
I oversee two locations and every time that I have needed these guys they have come in quickly, and in an organized manner, in, out job completed no strings attached. I get the run around with many companies and this one is definitely not one of those!
Response from Fire Pros, LLC:
Thank you for leaving a review, we greatly appreciate your feedback! Alex is an awesome asset and we want to create value for you and your organization, Thanks again and have a fire safe day! Also if you have time, please visit Google and leave us a review there as well, we would greatly appreciate it!
Arrived On-Site FACP states all Systems Normal. Checked Panel History, Panel has been free and clear of ground faults since my last visit on Monday. History states open circuit troubles on RTU’s 1 thru 7, checked units on roof and found Duct smoke heads very dirty, cleaned all 7 smoke heads and Reset system. Also checked loop that ground was on, to verify no pinched wiring connections. ***All Systems Normal and Reset at this Time***
Arrived on-Site FACP stated ground fault after further trouble shooting isolated ground to NAC Circuit 1 North Side Of Restaurant which covers the Employee Restrooms the entire kitchen and ends in the Bar area above the booths ( NAC CIRCUIT RUNS are on print in FACP). Took Down H/S outside of Employee Restroom and ground cleared off system, put Horn/strobe back up. And ground at this time is clear from system. ***All Systems Normal and Reset at this time***
Sprinkler Inspection Annual Sprinkler System Inspection (2 Wet, 1 Dry)
Alarm Systems Inspection