Chris called in- the dialer panel is beeping - CMS is getting unidentified zones 36 & 32- please check beeping and identify zones and add to CMS zone list - or they will dispatch FD on them. those 2 points are in test until 3PM Friday. CMS acct# FLLV40342
Chris called having trouble with same smoke detector as on 9/23 Smoke at C Hall by room 4 616-450-2004
FACP BY BOILER ROOM: SD in C hall by room 4. 129 is saying MAINT required, cleaning the detector did not fix the issue. Recommend replacing detector. Notifier FSP- 851 - repair This quote is for fire pros to provide and install 1 notifier smoke detector head.
Chris called in said the system is beeping- this is monitored b y CMS and I don't see anything in the history. he does want service today if possible. 269-525-8305 CMS acct# FLLV40342
Hydrostatic Testing Repair
Portable Extinguishers and Kitchen Suppression Inspection
Chris called (269-587-2141) said he is showing ground fault again. we were out earlier in the summer and it was cleared by the time we got there- he is thinking maybe a sensor close to the outside of the bldg. call to set up a time.
Secured smoke head to base after customer cleaned smokes over night.
Fixed Fire Alarm ground fault- Fire Alarm Panel is beeping