Mike did a great job on the Exit Lights.
Helpful and answered all my questions
Alex was great, very fast and efficient.
Annual Extinguisher Inspection ( 2 ABCs )
Annual Alarm Inspection
TBD: Furnish necessary parts and labor to complete required testing on (1) Class K extinguisher Emergency/Exit Light: Furnish necessary parts and labor to replace (1) combo light that failed
Semi-annual Kitchen Suppression System Inspection Semi-annual Fire Extinguisher Inspection Semi-annual Exit & Emergency Lighting Inspection (2 units)
Portable Extinguishers, Emergency / Exit Lights, and Kitchen Suppression Inspection
Trouble shot System. System has Inoperable Deficiencies that Require attention. System will function partially (Fire Door/Furnace Shut-down will not function until system is Replaced)
Furnish necessary parts and labor to complete the following: -Replace (11) special order batteries _Install (6) new LED emergency lights
Replaced bedroom hallway Horn/Strobe and are glass Rod for bedroom hallway pull station ***All systems Normal and Reset ***
Completed FACP REPLACEMENT and Completed full Systems Inspection /Completed Annual Fire Alarm/Fire Extinguisher/Emergency Light inspections for 2019 ***All systems Normal and Reset ***
Connected Fire Panel for Monitoring and tested system ***All systems normal and reset ***
Completed Annual Fire Extinguisher inspection for 2018
2-20 Ashley confirmed ATTN: Ashley Alman PH: (248) 624-7948 EMAIL: firstname.lastname@example.org . RE: FIRE PROTECTION DEFICIENCIES NOTED FROM INSPECTION . Ashley, Thank you for choosing FIRE PROS, INC. as a service provider for your organization. We appreciate the opportunity to keep your facility fire safe and code compliant. During our recent inspection services, we found some items that require additional attention in order to be brought back up to code compliance. Please see the description below and the total cost for the service. . Emergency / Exit Lights Repair Exit / Emergency Lighting: During our recent Inspection Service, we found (44) fixtures that failed inspection due to to Bad Back-Up Batteries -which require replacement. We also found that (3) Emergency Light fixtures failed (2 due to bad Charging Boards and 1 is missing from its Mount) and (1) Exit Sign failed Inspection due to a Bad Charging Board requiring replacement. Below is a quick summary - repair > (44) Replace