Mike did a great job on the Exit Lights.
Helpful and answered all my questions
Alex was great, very fast and efficient.
MONITORED BY PROTECTED ACCESS SECURITY SYSTEMS, 2486826800 ACCT#5149, FACP IN BACK KITCHEN BY RISER. Confirmed with Brandon for 6:00 AM on Friday ask for Dave. SM Portable Extinguishers and Kitchen Suppression Inspection Annual Fire Extinguisher Inspection (8) Semi-Annual Kitchen Suppression System Inspection Deficiency: Number of Systems failed : 1 Deficiency: 12 Gallon Ansul system out of hydro date. Deficiency: Electric fuel source on steam oven does not shut down during system actuation. Electric non fuel source 110v outlets under hood do not de energize upon fire system actuation. Inoperable Deficiency: Exhaust fan over char broiler not working prior to test. Deficiency: Protection over 2B-Range/Grill combo blocked by shelf. Deficiency: Improper nozzle protection over first two deep fryers. Nozzles are 290’s and to high above cooking surface.