Good to work with
Mike did a great job on the Exit Lights.
Helpful and answered all my questions
Alex was great, very fast and efficient.
11/1/23 Confirmed for 11/3/23 DH Sprinkler Inspection Deficiency: Hydraulic nameplate is not legible, and must be made to be legible by customer Annual Fire Sprinkler Inspection (1 Wet System) 5-Year Internal Due: FDC Hydro Due:
Sprinkler Repair COMMERCIAL FIRE PAPERWORK ATTACHED: The tech will remove and replace the outdated water gauges. NFPA 25 (220.127.116.11) Gauges shall be replaced every 5 years
Kitchen Suppression and Portable Extinguishers Inspection Semi-Annual Kitchen Hood Fire Suppression System Inspection (PCL-460) Annual Fire Extinguisher Inspection (3 FE?) Deficiency for Pyro Chem KK-II PCL-460 Left of Hood: Electric 110v outlet under hood near grill does not de energize upon fire system actuation. Deficiency for Pyro Chem KK-II PCL-460 Left of Hood: Exhaust fan on left hood not working prior to test. Deficiency: Number of Systems failed : 1