Mike did an excellent job moving 2 horn strobes. Thank you!
Not real happy. When I ordered the inspection, I asked for 2 strobe lights to be moved. Jason wasn’t planning/prepared to do that. I was hoping to save money by having the inspection and strobes moved at the same time. Not Jason’s fault, but somebody dropped the ball.
Annual Fire Extinguisher Inspection (6 FE) Annual Exit & Emergency Lighting Inspection (6 units) Portable Extinguishers and Emergency / Exit Lights Inspection
Deficiency for Pyro Chem PCL-300 3 gallon Main Hood: Number of Systems failed : 1 NO Audio/Visual notification Electric to convection oven does NOT shut down when system is activated. Lori said she will have electrician fix. 2H nozzle needs to be dropped a total of 36” and have swivel nozzle added -36” pipe -36” chrome sleeve -swivel nozzle Need to remove and plug (2) appliance drops no longer needed Need to lower Class K and add Class K signage Semi-Annual Kitchen Hood Fire Suppression System Inspection (PCL-460?) Kitchen Suppression Inspection
Annual Fire Extinguisher Inspection (8 FE) Annual Kitchen Suppression System Inspection (PCL 3 gal AB) Portable Extinguishers and Kitchen Suppression Inspection
Annual Fire Extinguisher Inspection (13 FE) Portable Extinguishers Inspection
Annual Fire Alarm Inspection (114 Devices) (Firelite MS5-UD)