Sprinkler Service Call
Annual Fire Alarm Inspection (137 devices) (Est Quickstart)
Wet: Remove and replace the painted sprinkler sidewall heads outside of rooms 14 & 32. Painting of sprinklers can retard the thermal response of the heat-responsive element, can interfere with the free movement of parts, and render the sprinkler inoperable. Wet: Dry sidewall heads dated 2009 in the balconies have been in service for more than 10 years and will need to have (4) sent to UL for testing. Approval of replacement will consist of two steps, the first being that we will obtain the measurements of the sprinkler heads. Once the measurements are obtained, the next step would be to send a quote with actual cost for the replacements. NFPA 25 (188.8.131.52.1.6) Dry sprinklers that have been in service for 10 years shall be replaced or representative samples shall be tested then re-tested at 10-year intervals.
Alarm Systems Inspection