Completed fire extinguisher inspection and emergency light inspection. Rehung 1 fire extinguisher in garage that was coming out of the wall.
Annual Fire Extinguisher Inspection Annual Emergency/Exit Light Inspection
Completed annual Fire Alarm inspection for 2019
Completed annual Fire Extinguisher and emergency light inspections for 2019
Replaced Sprinkler Room Tamper PTS Plug Switch with New. Wired and tested ***All Systems Normal and Reset ***
Serviced System (Zone 3 ) Waterflow/Tamper in trouble upon arrival found sprinkler tamper plug very loose in its socket. Highly Recommended for Replacement. Bent prongs on plug to better fit securely in Socket. Tested and Reset System. ***All Systems Normal and Reset ***
Corrected Deficiencies from inspection ***All Systems Normal and Reset ***